CREATE TABLE `skontroly_jn` (
  `id` int NOT NULL AUTO_INCREMENT,
  `odkaz_sjednotka` int NOT NULL DEFAULT '0',
  `Aktual_KO_p` date DEFAULT NULL,
  `Aktual_KO_p_cas` varchar(10) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `Popis_p` text CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci,
  `Poznamka_p` text CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci,
  `Info_p` text CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci,
  `Zarizeni1_p` varchar(50) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `Zarizeni2_p` varchar(50) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `Zarizeni3_p` varchar(50) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `Zarizeni4_p` varchar(50) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `C_zarizeni1_p` varchar(30) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `C_zarizeni2_p` varchar(30) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `C_zarizeni3_p` varchar(30) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `C_zarizeni4_p` varchar(30) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `Aktual_KO_k` date DEFAULT NULL,
  `Aktual_KO_k_cas` varchar(10) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `Popis_k` text CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci,
  `Poznamka_k` text CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci,
  `Info_k` text CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci,
  `Zarizeni1_k` varchar(50) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `Zarizeni2_k` varchar(50) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `C_zarizeni1_k` varchar(20) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `C_zarizeni2_k` varchar(20) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `Aktual_KO_e` date DEFAULT NULL,
  `Aktual_KO_e_cas` varchar(10) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `Popis_e` text CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci,
  `Poznamka_e` text CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci,
  `Info_e` text CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci,
  `Zarizeni1_e` varchar(50) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `Zarizeni2_e` varchar(50) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `C_zarizeni1_e` varchar(20) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `C_zarizeni2_e` varchar(20) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `Aktual_KO_z` date DEFAULT NULL,
  `Aktual_KO_z_cas` varchar(10) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `Popis_z` text CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci,
  `Poznamka_z` text CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci,
  `Info_z` text CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci,
  `Zarizeni1_z` varchar(50) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `Zarizeni2_z` varchar(50) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `C_zarizeni1_z` varchar(20) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `C_zarizeni2_z` varchar(20) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `Aktual_KO_s` date DEFAULT NULL,
  `Aktual_KO_s_cas` varchar(10) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `Popis_s` text CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci,
  `Poznamka_s` text CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci,
  `Info_s` text CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci,
  `Zarizeni1_s` varchar(50) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `C_zarizeni1_s` varchar(20) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  UNIQUE KEY `id` (`id`)
) ENGINE=InnoDB AUTO_INCREMENT=476 DEFAULT CHARSET=utf8mb4 COLLATE=utf8mb4_czech_ci;

#
# Data for table "skontroly_jn"
#

INSERT INTO `skontroly_jn` VALUES (255,255,NULL,'','','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','','',NULL,'KomĂ­ny v provozovnĂˇch',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(256,256,NULL,'','','',NULL,'THERMONA Duo 50T','rozvod plynu','','','1039/09/04','','','',NULL,'','IndividuĂˇlnĂ­ samostatnĂˇ spalinovĂˇ  cesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 80mm. KouĹ™ovod s funkcĂ­ komĂ­na veden pĹ™es stĹ™echu do venkovnĂ­ho prostoru rourou AL. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn Pet Thermona-24kW - typu C. Napojen kouĹ™ovodem o svÄ›tlosti 80mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen napĹ™Ă­mo. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,5m-neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe 1n.p ĂşklidovĂˇ mĂ­stnost.','','                                                                                                ','IndividuĂˇlnĂ­ spal cesta P1','AL kouĹ™ovod-koaxiĂˇlnĂ­ 80','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(257,257,NULL,'','','',NULL,'BAXI NUVOLA 3 Comfort 240Fi','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','C13446600','','','','1999-11-30','','IndividuĂˇlnĂ­  samostatnĂˇ spalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100/60mm. KouĹ™ovod s funkcĂ­ komĂ­na veden pĹ™es stĹ™echu do venkovnĂ­ho prostoru rourou AL. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PetBaxi-24Kw  typu C. Napojen kouĹ™ovodem o svÄ›tlosti 100/60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 2x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  2n.p fa.TruhlĂˇrna.\r\n','','KominĂˇk pan AbrahĂˇm uvĂˇdĂ­ jinĂ˝ kotel neĹľ je u plynaĹ™e pana SkĂˇly                                                                                         ','IndividuĂˇlnĂ­ spal cesta P1','AL kouĹ™ovod-koaxiĂˇlnĂ­ 100/60','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'',''),(258,258,NULL,'','','',NULL,'BAXI Ecofour 24 F','rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','120447090','','','','1999-11-30','','IndividuĂˇlnĂ­  samostatnĂˇ spalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100/60mm. KouĹ™ovod s funkcĂ­ komĂ­na veden pĹ™es stĹ™echu do venkovnĂ­ho prostoru. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PetBaxi-24Kw  typu C. Napojen koaxiĂˇlnĂ­m kouĹ™ovodem o svÄ›tlosti 100/60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  2n.p fa. Nespo','','                                                ','IndividuĂˇlnĂ­ spal cesta P1','AL kouĹ™ovod-koaxiĂˇlnĂ­ 100/60','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(259,259,NULL,'','','',NULL,'BAXI LUNA 1,2 Fi','rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','B04141236','','','','1999-11-30','','IndividuĂˇlnĂ­  samostatnĂˇ spalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100/60mm. KouĹ™ovod s funkcĂ­ komĂ­na veden pĹ™es stĹ™echu do venkovnĂ­ho prostoru. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PetBaxi-24Kw  typu C. Napojen koaxiĂˇlnĂ­m kouĹ™ovodem o svÄ›tlosti 100/60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  2n.p fa. Nespo.\r\nKotel slouĹľĂ­ pro prodejnu Barev LakĹŻ','',' MyslĂ­m si, Ĺľe nesedĂ­ kotel                                                               ','IndividuĂˇlnĂ­ spal cesta P1','AL kouĹ™ovod-koaxiĂˇlnĂ­ 100/60','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(261,261,NULL,'','','NenĂ­ provedena revize domovnĂ­ho rozvodu',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','','','                                ','KomĂ­ny v provozovnĂˇch',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(262,262,NULL,'','BAXI Â Eco 240i - poĹˇkozen demontovĂˇn\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ\r\n25.08.2021 vĂ˝mÄ›na kotle za BAXI ECOFOUR 24','',NULL,'BAXI prime 24 - kondenzaÄŤnĂ­ kotel','rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','231611158','','','','1999-11-30','','IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - oprdinace 1n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AL ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 1 x 90 stupĹĹŻ z pevnĂ©ho hlinĂ­ku o prĹŻmÄ›ru 120 mm a dĂ©lce 0,8 m. ĂšÄŤinnĂˇ dĂ©lka 11 m-neĂşÄŤinnĂˇ 0,3 m. ','','                                                                ','IndividuĂˇlnĂ­ spalinovĂˇ cesta N1','Kom zdÄ›nĂ˝ vĂ˝cevr. vyvloĹľ. AL oheb 120 mm','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'',''),(263,263,NULL,'','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ\r\n\r\n21.12. 2022 VĂ˝mÄ›na kotle za kondenzaÄŤnĂ­ Baxi Luna classic 24','NenĂ­ provedena nebo zaloĹľena ĹľĂˇdnĂˇ revize ani kontrola',NULL,'Baxi Luna classic 24 - kondenzaÄŤnĂ­ kotel','rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','221839030','','','','1999-11-30','','IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - technickĂˇ mĂ­stnost 1n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AL ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 1 x 90 stupĹĹŻ z pevnĂ©ho hlinĂ­ku o prĹŻmÄ›ru 120 mm a dĂ©lce 0,6 m. ĂšÄŤinnĂˇ dĂ©lka 11 m-neĂşÄŤinnĂˇ 0,3 m. ','','                                                                                ','IndividuĂˇlnĂ­ spalinovĂˇ cesta N1','Kom zdÄ›nĂ˝ vĂ˝cevr. vyvloĹľ. AL oheb 120 mm','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(264,264,NULL,'','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ\r\nplynovĂ˝ sporĂˇk\r\n\r\n21.12. 2022 VĂ˝mÄ›na kotle za kondenzaÄŤnĂ­ Luna classic 24','',NULL,'Baxi Luna classic 24 - kondenzaÄŤnĂ­ kotel','rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','plynovĂ˝ sporĂˇk','','221839034','','','','1999-11-30','','IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - chodba 2n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AL ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 2 x 90stupĹĹŻ z pevnĂ©ho hlinĂ­ku o prĹŻmÄ›ru 120 mm a dĂ©lce 1,2 m. ĂšÄŤinnĂˇ dĂ©lka 8 m-neĂşÄŤinnĂˇ 0,3 m. ','','                                                ','IndividuĂˇlnĂ­ spalinovĂˇ cesta N1','Kom zdÄ›nĂ˝ vĂ˝cevr. vyvloĹľ. AL oheb 120 mm','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'',''),(265,265,NULL,'','BAXI ECOFOUR 240F\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','',NULL,'BAXI ECOFOUR 240F','rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','','','','','1999-11-30','','IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - chodba 2n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AC ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 1 x 90stupĹĹŻ z pevnĂ©ho nerezu o prĹŻmÄ›ru 120 mm a dĂ©lce 1,2 m. ĂšÄŤinnĂˇ dĂ©lka 8 m-neĂşÄŤinnĂˇ 0,3 m. ','','                                                ','IndividuĂˇlnĂ­ spalinovĂˇ cesta N1','Kom zdÄ›nĂ˝ vĂ˝cevr. vyvloĹľ. AL oheb 120 mm','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(266,266,'2022-05-02','13-14','kondenzaÄŤnĂ­ kotel - Baxi Luna classic 24\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','',NULL,'Baxi Luna classic 24 - kondenzaÄŤnĂ­ kotel','rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','231641229','','','','1999-11-30','','IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - kuchyĹ 2n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AL ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 1 x 90 a 1x45 stupĹĹŻ z pevnĂ©ho nerezu o prĹŻmÄ›ru 120 mm a dĂ©lce 0,6 m. ĂšÄŤinnĂˇ dĂ©lka 8 m-neĂşÄŤinnĂˇ 0,3 m. ','','                                                ','IndividuĂˇlnĂ­ spalinovĂˇ cesta N1','Kom zdÄ›nĂ˝ vĂ˝cevr. vyvloĹľ. AL oheb 120 mm','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'',''),(268,268,NULL,'','','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','','KomĂ­n ÄŤ.1 nevyhovuje a je udÄ›len MarĹˇĂ­kovi pĂ­semnĂ˝ zĂˇkaz pouĹľĂ­vat viz. zprĂˇva\r\nKomĂ­n ÄŤ.2 nenĂ­ pouĹľĂ­vanĂ˝','                ','KomĂ­ny v provozovnĂˇch','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(269,269,NULL,'','','',NULL,'BAXI ECOFOUR 24','rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','','','','',NULL,'','IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem-120 mm. KouĹ™ovod osazen 1x kolenem 90 stupĹĹŻ o dĂ©lce 0,7 m. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PETBaxi-24kW Typu B. KomĂ­n zdÄ›nĂ˝ osazen AL H400 o prĹŻmÄ›ru 120mm. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 5,5 m - neĂşÄŤinnĂˇ 0,2 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe 1n.p-Hala ÄŤĂ­slo 3 - KrÄŤka.','ChybĂ­ kontrola komĂ­nu pro plynovĂ© spotĹ™ebiÄŤe 2017 ','                ','IndividuĂˇlnĂ­ sam spalinovĂˇ cesta N1','AL kouĹ™ovod 120mm','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(270,270,NULL,'','','',NULL,'','','','','','','','',NULL,'','','','                ','',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(271,271,NULL,'','','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','budova,  , ','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(272,272,'2022-05-16','','BAXI ECOFOUR 240F - turbo kotel\r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe                                                                                              ','                                                                                              ',NULL,'BAXI ECOFOUR 240F - turbo kotel','rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','122415652','','','','1999-11-30','','SamostatnĂˇ  spalinovĂˇ  cesta P1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ kouĹ™ovod  AL pevnĂˇ roura o svÄ›tlosti  80mm. SpotĹ™ebiÄŤ PET â€“ Baxi  - 24 kW  v provedenĂ­  C - napojen  kouĹ™ovodem AL  80mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝+ kontrolnĂ­ otvor  . KomĂ­novĂˇ  konstrukce zdÄ›nĂˇ osazena nerez ohebnou hadicĂ­ v provedenĂ­ pĹ™etlak 2x0,12mm .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 12m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  prĂˇdelna 1n.p.                                                                                                   ','                                                                                                ',NULL,'SamostatnĂˇ Â spalinovĂˇ Â cesta P1','KouĹ™ovod Â AL pevnĂˇ roura o svÄ›tlosti Â 80mm','','',NULL,'','','                                                                                                ',NULL,'','','','',NULL,'','                                                                                                ','                                                                                                ',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(273,273,NULL,'','                                                              ','byt majitele                                                                ',NULL,'','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','','','',NULL,'',' ,                                                                 ','                                                                ',NULL,'',' ','','',NULL,'','','                                                                ',NULL,'','','','',NULL,'','                                                                ','                                                                ',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(275,275,NULL,'','','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','budova,  , ','','                ','budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(276,276,NULL,'','VIADRUS G25 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ\r\nplynovĂ˝ sporĂˇk                           ','                                ',NULL,'VIADRUS G25 - atmosfĂ©rickĂ˝ kotel, plyn kamna','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','plynovĂˇ kamna','',' ','','','','1999-11-30','','SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AL  H400  vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Viadrus   28 kW  v provedenĂ­ B- napojen kouĹ™ovodem AL -130mm. DĂ©lka kouĹ™ovodu 1,5m â€“osazen  1x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v suterĂ©nu .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  16m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  techn. mĂ­stnost - suterĂ©n .                                 ','                                ','                                ','SamostatnĂˇ Â spalinovĂˇ Â cesta N1','VĂ­cevrstvĂ­ zdÄ›nĂ˝ komĂ­n','','',NULL,'','','                                ',NULL,'','','','',NULL,'','                                ','                                ',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(278,278,NULL,'','','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','budova,  , ','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(279,279,NULL,'','THERM 12 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ','',NULL,'THERM 12 - atmosfĂ©rickĂ˝ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','','','','','','','1999-11-30','','SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AL  H400 vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Therm na zemnĂ­ plyn    24 kW  v provedenĂ­- B- napojen kouĹ™ovodem AL -130mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  2x kolenem  90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝. KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p .ĂšÄŤinnĂˇ   vĂ˝Ĺˇka spalinovĂ© cesty  14m- neĂşÄŤinnĂˇ - 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  techn. mĂ­stnost 1n.p .','','                ','SamostatnĂˇ Â spalinovĂˇ Â cesta N1','VĂ­cevrstvĂ­ zdÄ›nĂ˝ komĂ­n','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(281,281,'2022-05-16','nenĂ­','Prime 24 - kondenzaÄŤnĂ­ kotel\r\nRozvody plynu od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ.           ','3x Plyn Topidlo BETA 4 - gamaty,plynovĂ˝ sporĂˇk ,rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe.\r\n31. 3. 2021 Byla provedena vĂ˝mÄ›na plynovĂ˝ch spotĹ™ebiÄŤĹŻ - plyn. kotel + radiĂˇtory                                  ',NULL,'BAXI prime 24 - kondenzaÄŤnĂ­ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','203937010','','','','1999-11-30','','NovĂ˝ kondenzaÄŤnĂ­ kotel-vĂ˝mÄ›na mĂ­sto gamat                              ','                                ',NULL,'KomĂ­n systĂ©movĂ˝kondenzaÄŤnĂ­ kotel-mĂ­sto gamat  ',' ','','','1999-11-30','','','                                ',NULL,'','','','',NULL,'','                                ','                                ',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(283,283,NULL,'','','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','budova,  , ','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(284,284,NULL,'','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','',NULL,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel','rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','120259419','','','','1999-11-30','','SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400 vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu1,2mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  7m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba  1n.p.','',NULL,'SamostatnĂˇ Â spalinovĂˇ Â cesta N1','VĂ­cevrstvĂ­ zdÄ›nĂ˝ komĂ­n','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(285,285,NULL,'','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ','',NULL,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','120959571','','','','1999-11-30','','SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu1,2mosazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  5m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 2n.p.  ','','                ','SamostatnĂˇ Â spalinovĂˇ Â cesta N1','VĂ­cevrstvĂ­ zdÄ›nĂ˝ komĂ­n','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(286,286,NULL,'','BAXI Ecofour 24F - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ                                                                                               ','                                                                                                ',NULL,'BAXI Ecofour 24F - turbo kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','C13750985','','','','1999-11-30','','IndividuĂˇlnĂ­  samostatnĂˇspalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100x60mm. KouĹ™ovod s funkcĂ­ komĂ­na â€“ rourouAL.SpotĹ™ebiÄŤ -plyn.PetBaxi-24Kw  typu C.Napojen  kouĹ™ovodem o svÄ›tlosti 100x60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 1x kolenem 90 stupĹĹŻ s kontrolnĂ­m otvorem.ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  3n.p chodba.Kontrolu spalinovĂ© cesty lze provĂ©st z ĂşstĂ­ komĂ­na+ kontrolnĂ­m otvorem na kouĹ™ovodu.                                                                                                ','                                                                                                ',NULL,'SamostatnĂˇ Â spalinovĂˇ Â cesta P1','KouĹ™ovod Â AL pevnĂˇ roura o svÄ›tlosti Â 100x60mm','','',NULL,'','','                                                                ',NULL,'','','','',NULL,'','                                                                                        ','                                                                                                ',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(288,288,NULL,'','','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','budova,  , ','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(289,289,NULL,'','','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','',NULL,NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(290,290,NULL,'','BAXI Ecofour 24 \r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','',NULL,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','124859741','','','','1999-11-30','','SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 1,8m osazen 1x kolenem 90 stupĹĹŻ a 1x 60 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 13,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba1n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','',NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1','zdÄ›nĂ˝ komĂ­n osazen AK oh. vloĹľ. 120mm','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(291,291,NULL,'','BAXI Prime 24 - kondenzaÄŤnĂ­ kotel\r\nplynovĂ˝ sporĂˇk\r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','',NULL,'BAXI Prime 24 - kondenzaÄŤnĂ­ kotel','plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','171937617','','','','1999-11-30','','SamostatnĂˇ  spalinovĂˇcesta P1, kterĂˇ je tvoĹ™ena PP  kouĹ™ovodem 80mm - napojen na zdÄ›nĂ˝  komĂ­n, osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm  - koaxiĂˇlnÄ› osazena PP ohebnou vloĹľkou dn 75mm . SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­  C -napojen kouĹ™ovodem PP. DĂ©lka kouĹ™ovodu 1,8m osazen 1x kolenem 90 stupĹĹŻ a 1x 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 13,5m- neĂşÄŤinnĂˇ  0,0m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba2n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 2n.p.','','                                                                                                ','KomĂ­n systĂ©movĂ˝-kondenzaÄŤnĂ­ kotel',' KondenzaÄŤnĂ­ kotel','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(292,292,NULL,'','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ','31.01.2023 VĂ˝mÄ›na kotle na typ: BAXI ECOFOUR 24, kterĂ˝ byl dĹ™Ă­ve u panĂ­ Ĺ imanovĂ© v areĂˇlu MĂ­rova DubĂ­, vĂ˝mÄ›nu provedl pan KuiĹˇ. Stav kotle 25.08.2021 novĂ˝.',NULL,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','C13760619','','','','1999-11-30','','SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,8m osazen 2x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 11,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba2n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 2n.p.','','                ','SamostatnĂˇ spalinovĂˇ cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(293,293,NULL,'','THERM 12S - atmosfĂ©rickĂ˝ kotel\r\nplynovĂ˝ sporĂˇk\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','nevhodnĂˇ hadice u sporĂˇku -  vymÄ›nit za vhodnĂ˝ typ\r\n\r\ndoplnit hlĂˇsiÄŤ CO\r\n\r\n14.05.2024 VymÄ›nit kotel za novĂ˝ typ',NULL,'THERM 12S - atmosfĂ©rickĂ˝ kotel - nutnĂˇ vĂ˝mÄ›na','plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','86/2','','','','1999-11-30','','SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 130mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AL ohebnou vloĹľkou o prĹŻmÄ›ru 125mm. SpotĹ™ebiÄŤ plyn. PETThermona- 24kW v provedenĂ­  Bnapojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 2m osazen 1x kolenem 90 stupĹĹŻ a 1x 45 stupĹĹŻ .ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 8,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  koupelna  3n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','',NULL,'SamostatnĂˇ spalinovĂˇ cesta P1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(294,294,NULL,'','BAXI Main 24i - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','',NULL,'BAXI Main 24i - turbo kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','B74765266','','','','1999-11-30','','SamostatnĂˇ  spalinovĂˇcesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 2m osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 8,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“koupelna3n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','',NULL,'SamostatnĂˇ spalinovĂˇ cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(295,295,NULL,'','BAXI Main 24i - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','',NULL,'BAXI Main 24i - turbo kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','','','','1999-11-30','','SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n, osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 20kW v provedenĂ­  B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 1,2m -  osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 5,3m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  koupelna4n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 4n.p.','','                ','SamostatnĂˇ spalinovĂˇ cesta P1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(296,296,NULL,'','BAXI Mainfour 24 F - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','V ÄŤervnu 2017 probÄ›hla instalace novĂ©hoho kotle BAXI Ecofour 24F (atmosferickĂ© turbo).\r\n',NULL,'BAXI Mainfour 24 F - turbo kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','','','',NULL,'','SamostatnĂˇ  spalinovĂˇcesta P1, kterĂˇ je tvoĹ™enaAL  kouĹ™ovodem 80mm - napojen na zdÄ›nĂ˝  komĂ­n, osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm  - koaxiĂˇlnÄ› osazena AK  ohebnou vloĹľkou dn 80mm â€“ provedenĂ­ pĹ™etlak. SpotĹ™ebiÄŤplyn. PET Baxi- 24kW v provedenĂ­  C -napojen kouĹ™ovodem AL .DĂ©lkakouĹ™ovodu 1,8m osazen 2x kolenem 90 stupĹĹŻ a 1x 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 4,5m- neĂşÄŤinnĂˇ  0,0m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 4n.p.KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 4n.p.','','                ','SamostatnĂˇ Â spalinovĂˇ cesta P1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(297,297,NULL,'','','',NULL,'BAXI Ecofour 24','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','','','',NULL,'','','',NULL,'',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(298,298,NULL,'','BAXI Main 24i - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','14.05.2024 vymÄ›nit kotel',NULL,'BAXI Main 24i - turbo kotel - nutnĂˇ vĂ˝mÄ›na','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','B44493376','','','','1999-11-30','','SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 20kW v provedenĂ­ B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 0,8m osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 4,3m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“5n.p.KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 5n.p.KomĂ­nv ĂşstĂ­ osazen  3m nĂˇstavcem. ','','                                ','SamostatnĂˇ spalinovĂˇ cesta P1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(301,301,NULL,'','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','',NULL,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','124955396','','','','2022-02-17','15:00','SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­ B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 15,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba 1n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','',NULL,'SamostatnĂˇ spalinovĂˇ cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(302,302,NULL,'','BAXI Ecofour 24 atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe\r\n','NemĂˇ hlĂˇsiÄŤe - CO + poĹľĂˇrnĂ­.\r\nOstatnĂ­ vĹˇe ok.\r\n',NULL,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','142455306','','','','2022-02-17','15:00','SamostatnĂˇ  spalinovĂˇcesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­  B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 15,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“chodba1n.p . KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','',NULL,'SamostatnĂˇ spalinovĂˇ cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(303,303,'2022-05-30','11.00','2x PT Gamaty 461\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','2017-Instalace CO hlĂˇsiÄŤe a detektoru kouĹ™e',NULL,'3x PT Gamaty 461','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','','','','2022-02-17','15:00','SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena ALkouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen  ALohebnou vloĹľkou o prĹŻmÄ›ru 125mm. SpotĹ™ebiÄŤ plyn. POV Mora 371+topidlo- 20kW v provedenĂ­- B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 1,7m -  osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 12,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“koupelna2n.p','',NULL,'Gamaty - prozkoumat komĂ­n se nepouĹľĂ­vĂˇ',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(304,304,'2022-05-30','12.00','1x PT Gamat 461\r\n1x PT MORATHERM','2017-Instalace CO hlĂˇsiÄŤe, Detektoru kouĹ™e',NULL,'1x PT Gamat 461','','','','','','','','2022-02-17','15:00','SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena ALkouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen  AL ohebnou vloĹľkou o prĹŻmÄ›ru 125mm. SpotĹ™ebiÄŤ plyn. POV Mora35 - 35kW v provedenĂ­ â€“ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,3m -  osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 12,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“koupelna2n.p','',NULL,'Gamaty - prozkoumat',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(305,305,NULL,'','BAXI Ecofour 24 atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe',' ',NULL,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','144859117','','','','2022-02-17','15:00','SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­  B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba3n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','',NULL,'SamostatnĂˇ spalinovĂˇ cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(306,306,NULL,'','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','',NULL,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','152518241','','','','2022-02-17','15:00','SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝ komĂ­n osa AKohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­ B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba3n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','',NULL,'SamostatnĂˇ spalinovĂˇ cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(307,307,NULL,'','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','',NULL,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','144859117','','','','2022-02-17','15:00','SamostatnĂˇ  spalinovĂˇcesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­  B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba3n.p.  KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','',NULL,'SamostatnĂˇ spalinovĂˇ cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(308,308,NULL,'','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','',NULL,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','152518242','','','','2022-02-17','15:00','SamostatnĂˇ  spalinovĂˇcesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝ komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­ B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 2x kolenem 90 stupĹĹŻ a 1x30 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 4m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“4n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 4n.p.','',NULL,'SamostatnĂˇ spalinovĂˇ cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(309,309,NULL,'','BAXI Ecofour 24 F - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','',NULL,'BAXI Ecofour 24 F - turbo kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','','','','2022-02-17','15:00','SamostatnĂˇ  spalinovĂˇcesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem  80mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm â€“ koaxiĂˇlnÄ› osazena AK nerez pĹ™etlak dn 80mm . SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­ C -napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 2m - osazen 2x kolenem 90 stupĹĹŻ a 1x30 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 4m- neĂşÄŤinnĂˇ  0,0m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“4n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 4n.p.','','                ','SamostatnĂˇ Â spalinovĂˇcesta P1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(310,310,NULL,'','','Byt nenĂ­ v provozu',NULL,'NenĂ­ instalovĂˇno','','','','','','','',NULL,'','','','                ','NenĂ­ instalovĂˇno',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(312,312,NULL,'','','2018-chybĂ­ zprava o rozvodech v domÄ›',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(313,313,NULL,'','','19.02.2021 \r\nRevizi udÄ›lĂˇ Petr MatkoviÄŤ od Koudyho 606 338 216 \r\nzjistil jsem, Ĺľe je asi dobrĂ˝ znĂˇmĂ˝ pana SkĂˇly.',NULL,'PK BAXI Nuvola 240Fi - turbo kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','','','','2022-02-16','15:00','SamostatnĂˇ  spalinovĂˇ  cesta P1, kterĂˇ je tvoĹ™ena AL koaxiĂˇlnĂ­m kouĹ™ovodem  kouĹ™ovodem  â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti 100/60mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­  B- napojen koaxiĂˇlnĂ­m  kouĹ™ovodem AL +AL -100/60mm. DĂ©lka kouĹ™ovodu 2,5m â€“ osazen  2x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝.  ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 3m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  restaurace 1 n.p .   ','',NULL,'SamostatnĂˇ Â spalinovĂˇ Â cesta P1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(314,314,NULL,'','PK BAXI Nuvola 240Fi - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','kontrola typu kotle',NULL,'PK BAXI Nuvola 240Fi - turbo kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','B41634261','','','','1999-11-30','','SamostatnĂˇ spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti  80mm. SpotĹ™ebiÄŤ PETâ€“Baxi  - 24kW v provedenĂ­  C -napojen kouĹ™ovodem AL 80mm. DĂ©lka kouĹ™ovodu10mâ€“osazen2x kolenem 90stupĹĹŻ- kouĹ™ovodrozebĂ­ratelnĂ˝ .ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ salon  2n.p.','',NULL,'SamostatnĂˇ Â spalinovĂˇ Â cesta P1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(315,315,NULL,'','Baxi Main 24Fi - turbo kotel\r\nplynovĂ˝ sporĂˇk\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','',NULL,'Baxi Main 24Fi - turbo kotel','plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','B54285468','','','','1999-11-30','','SamostatnĂˇ spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena ALkoaxiĂˇlnĂ­m kouĹ™ovodem â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti 100/60mm. SpotĹ™ebiÄŤ PETâ€“Baxi  - 24kW v provedenĂ­- B-napojenkoaxiĂˇlnĂ­m  kouĹ™ovodem AL+AL -100/60mm. DĂ©lka kouĹ™ovodu2mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovodrozebĂ­ratelnĂ˝ .ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty 2m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ koupelna  3n.p.','',NULL,'SamostatnĂˇ spalinovĂˇ cesta P1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(316,316,NULL,'','BAXI Main 24i - turbo kotel\r\nplynovĂ˝ sporĂˇk\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','',NULL,'BAXI Main 24i - turbo kotel','plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','B54285474','','','','1999-11-30','','SamostatnĂˇ spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena ALkoaxiĂˇlnĂ­m kouĹ™ovodem â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti 100/60mm. SpotĹ™ebiÄŤ PETBaxi  - 24kW v provedenĂ­ B-napojenkoaxiĂˇlnĂ­m  kouĹ™ovodem AL+AL -100/60mm. DĂ©lka kouĹ™ovodu2mosazenna pĹ™Ă­mo - kouĹ™ovod rozebĂ­ratelnĂ˝ .ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty 2m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ koupelna  3n.p.','',NULL,'SamostatnĂˇ spalinovĂˇ cesta P1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(318,318,NULL,'','','2018-chybĂ­ revize rozvodĹŻ plynu v domÄ›',NULL,'','','','','','','','',NULL,'','','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(319,319,NULL,'','BAXI ECO 3 Compact 240i - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','',NULL,'BAXI ECO 3 Compact 240i - turbo kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','','','','1999-11-30','','SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90 stupĹĹŻ â€“ kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  9m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ kuchyĹ 2n.p.','',NULL,'SamostatnĂˇ Â spalinovĂˇ Â cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(320,320,NULL,'','BAXI ECO 3 Compact 240i - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','23.2.2021 - praskliny v rozĂ­ch kolem stropu na stranÄ› smÄ›rem do ulice (obĂ˝vĂˇk\r\n            a loĹľnice)    \r\n          - sporĂˇk je elektrickĂ˝ se 4 plotĂ˝nkami',NULL,'BAXI ECO 3 Compact 240i - turbo kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','B92160715','','','','1999-11-30','','SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.UÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  6m-neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ kuchyĹ 2n.p.','',NULL,'SamostatnĂˇ Â spalinovĂˇ Â cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(322,322,NULL,'','','2018-chybĂ­ zprava o rozvodech v domÄ›',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(323,323,NULL,'','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','',NULL,'BAXI prime 24 - kondenzaÄŤnĂ­ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','212137001','','','','1999-11-30','','SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400 vloĹľkou   DN 120mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­ B- napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupĹĹŻ - kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  12m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba   1n.p.  ','',NULL,'SamostatnĂˇ Â spalinovĂˇ Â cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(324,324,NULL,'','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','',NULL,'BAXI prime 24 - kondenzaÄŤnĂ­ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','231611155','','','','1999-11-30','','SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  12m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 1n.p.DigestoĹ™ provedena vnitĹ™nĂ­m reĹľimu filtrace.','',NULL,'SamostatnĂˇ Â spalinovĂˇ Â cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(325,325,NULL,'','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','11/03/2024 BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel C01961164- za \r\nBaxi Luna classic 24 - kondenzaÄŤnĂ­ kotel ',NULL,'Baxi Luna classic 24 - kondenzaÄŤnĂ­ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','234411331','','','','1999-11-30','','SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena ALkouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝ - zdÄ›nĂ˝komĂ­n -osazen AC H400dnvloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.UÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  9mâ€“ neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ kuchyĹ 2n.p. DigestoĹ™ provedena ve vnitĹ™nĂ­m reĹľimu filtrace.','',NULL,'SamostatnĂˇ Â spalinovĂˇ Â cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(326,326,NULL,'','BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','10/2023 BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel - za \r\nBaxi Luna classic 24 - kondenzaÄŤnĂ­ kotel 233941344',NULL,'Baxi Luna classic 24 - kondenzaÄŤnĂ­ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','233941344','','','','1999-11-30','','SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena ALkouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝ - zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤPETâ€“Baxi24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.UÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  9m-neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 2n.p.','',NULL,'SamostatnĂˇ Â  spalinovĂˇ Â cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(327,327,NULL,'','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','',NULL,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','C01365233','','','','1999-11-30','','SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90 stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 3n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  6m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 3n.p.','',NULL,'SamostatnĂˇ Â spalinovĂˇ Â cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(328,328,NULL,'','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe\r\n\r\n8/2023 vĂ˝mÄ›na kotle ','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe\r\n\r\n8/2023 VĂ˝mÄ›na kotle za kondenzaÄŤnĂ­ Baxi Luna classic 24 ',NULL,'Baxi Luna classic 24 - kondenzaÄŤnĂ­ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','231611124','','','','1999-11-30','','SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena ALkouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝ - zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­ B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 3n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  9m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ kuchyĹ 3n.p. DigestoĹ™ provedena ve vnitĹ™nĂ­m reĹľimu filtrace.','',NULL,'SamostatnĂˇ Â spalinovĂˇ Â  cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(331,331,NULL,'','THERM 23LXI - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ','14.05.2024 ',NULL,'THERM 23LXI - atmosfĂ©rickĂ˝ kotel  - nutnĂˇ vĂ˝mÄ›na','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','820/8/97','','','','1999-11-30','','SamostatnĂˇ   spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena  AL  kouĹ™ovodem 130mm - napojen na zdÄ›nĂ˝  komĂ­n - osazen AL  ohebnou  vloĹľkou o prĹŻmÄ›ru 130mm. SpotĹ™ebiÄŤ plyn. PET  Therm  o vĂ˝konu 24kW  v provedenĂ­ B - napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,3m - osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 15,5m- neĂşÄŤinnĂˇ  0,3m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  kancelĂˇĹ™  1n.p KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','',NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(332,332,NULL,'','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','',NULL,'BAXI prime 24 - kondenzaÄŤnĂ­ kotel','rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','211339267','','','','1999-11-30','','SamostatnĂˇ  spalinovĂˇcesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 130mm - napojen na zdÄ›nĂ˝  komĂ­n - osazen AL  ohebnou vloĹľkou o prĹŻmÄ›ru 130mm. SpotĹ™ebiÄŤ plyn. PET  na zemnĂ­ plyn o vĂ˝konu 24kW  v provedenĂ­ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,5m - osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 9m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  koupelna2n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 2n.p.','','                ','SamostatnĂˇ Â spalinovĂˇ Â cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(333,333,NULL,'','','',NULL,'BAXI PRIME 28 se zĂˇsobnĂ­kem TUV','rozvod plynu','','','174539463','','','',NULL,'','IndividuĂˇlnĂ­  samostatnĂˇ spalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100/60mm. KouĹ™ovod s funkcĂ­ komĂ­na veden pĹ™es obvodovou zeÄŹ do venkovnĂ­ho prostoru rourou PP. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PetBaxi-24Kw  typu C. Napojen kouĹ™ovodem o svÄ›tlosti 100/60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,5m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe 1n.p technickĂˇ mĂ­stnost-prodejna.\r\n','','                                                                                                ','IndividuĂˇlnĂ­ spal cesta P1','PP kouĹ™ovod-koaxiĂˇlnĂ­ 100/60','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(337,337,NULL,'','','',NULL,'','','','','','','','',NULL,'','','','                                                ','',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(338,338,NULL,'','','',NULL,'','','','','','','','',NULL,'','','','                                                ','',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(339,339,NULL,'','','',NULL,'','','','','','','','',NULL,'','','','                                                ','',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(341,341,NULL,'','','',NULL,'','','','','','','','',NULL,'','','','                                                                ','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(342,342,NULL,'','','',NULL,'','','','','','','','',NULL,'','','','                                                                ','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(343,343,NULL,'','','',NULL,'BAXI Ecofour 24','rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','','','','',NULL,'','IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem-120 mm. KouĹ™ovod osazen 1x kolenem 90 stupĹĹŻ o dĂ©lce 0,7 m. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PETBaxi-24kW Typu B. KomĂ­n zdÄ›nĂ˝ osazen AL H400 o prĹŻmÄ›ru 120mm. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 5,5 m - neĂşÄŤinnĂˇ 0,2 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe 1n.p-Hala ÄŤĂ­slo 1 - MarĹˇĂ­k.','','                ','IndividuĂˇlnĂ­ sam spalinovĂˇ cesta N1','AL kouĹ™ovod 120mm','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(344,344,NULL,'','','',NULL,'','','','','','','','',NULL,'','','','                                                ','',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(345,345,NULL,'','','',NULL,'','','','','','','','',NULL,'','','','                                                ','',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(346,346,NULL,'','','',NULL,'','','','','','','','',NULL,'','','','                                                ','',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(347,347,NULL,'','','',NULL,'','','','','','','','',NULL,'','','','                                                ','',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(348,348,NULL,'','','',NULL,'','','','','','','','',NULL,'','','','                                                ','',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(349,349,NULL,'','','',NULL,'','','','','','','','',NULL,'',' , ','','                                                ','',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(350,350,NULL,'','','',NULL,'','','','','','','','',NULL,'','',' ','                ','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(351,351,NULL,'','','',NULL,'','','','','','','','',NULL,'','','',NULL,'',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(353,353,NULL,'','','',NULL,'','','','','','','','',NULL,'','','','                                                ','',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(354,354,NULL,'','','',NULL,'','','','','','','','',NULL,'',' , ','','                                                ','',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(356,356,NULL,'','','',NULL,'','','','','','','','',NULL,'',' , ','','                                                ','',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(357,357,NULL,'','','',NULL,'','','','','','','','',NULL,'','','',NULL,'',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(359,359,NULL,'','PlynomÄ›r, rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','',NULL,'PlynomÄ›r','rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','',NULL,'','','','','KomĂ­ny v provozovnĂˇch',' ','','',NULL,'','','','','','','','',NULL,'','','','','','','','',NULL,'','','',NULL,'',''),(360,360,NULL,'','','NenĂ­ provedena revize domovnĂ­ho rozvodu',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','','','                                ','KomĂ­ny v provozovnĂˇch',' ','','',NULL,'','','','','','','','',NULL,'','HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','','','HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','','','',NULL,'','','',NULL,'',''),(361,361,NULL,'','','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','','KomĂ­n ÄŤ.1 nevyhovuje a je udÄ›len MarĹˇĂ­kovi pĂ­semnĂ˝ zĂˇkaz pouĹľĂ­vat viz. zprĂˇva\r\nKomĂ­n ÄŤ.2 nenĂ­ pouĹľĂ­vanĂ˝','                ','KomĂ­ny v provozovnĂˇch','','','',NULL,'',NULL,'','','','','','',NULL,'',NULL,'','','','','','',NULL,'',NULL,NULL,NULL,'',''),(362,362,NULL,'','rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','','','','','','','',NULL,'','budova,  , ','','','budova',' ','','',NULL,'','','','','','','','',NULL,'','','','','','','','',NULL,'','','',NULL,'',''),(363,363,NULL,'','rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','','','','','','','',NULL,'','budova,  , ','','                ','budova',' ','','',NULL,'','','','','','','','',NULL,'','','','','','','','',NULL,'','','',NULL,'',''),(364,364,NULL,'','rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','','','','','','','',NULL,'','budova,  , ','','','budova',' ','','',NULL,'','','','','','','','',NULL,'','HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','','','HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','','','',NULL,'','','',NULL,'',''),(365,365,NULL,'','rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','','','','','','','',NULL,'','budova,  , ','','','budova',' ','','',NULL,'','','','','','','','',NULL,'','','','','','','','',NULL,'','','',NULL,'',''),(366,366,NULL,'','rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','','','','','','','',NULL,'','budova,  , ','','','budova',' ','','',NULL,'','','','','','','','',NULL,'','HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST - 5 ks vÄŤetnÄ› 5 ks skĹ™Ă­nÄ›k','','','SkĹ™Ă­Ĺ + HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST ','','','',NULL,'','','',NULL,'',''),(367,367,NULL,'','rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','','','','','','','',NULL,'','','','','budova',' ','','',NULL,'','','','','','','','',NULL,'','HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','','','SkĹ™Ă­Ĺ + HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST ','','','',NULL,'','','',NULL,'',''),(368,368,NULL,'','rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','','','','','','','',NULL,'','','','','budova',' ','','',NULL,'','','','','','','','',NULL,'','HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','','','HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','','','',NULL,'','','',NULL,'',''),(369,369,NULL,'','rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','2018-chybĂ­ revize rozvodĹŻ plynu v domÄ›',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','','','','','','','',NULL,'','','','','budova',' ','','',NULL,'','','','','','','','',NULL,'','HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','','','HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','','','',NULL,'','','',NULL,'',''),(370,370,NULL,'','rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','','','','','','','',NULL,'','','','','budova',' ','','',NULL,'','','','','','','','',NULL,'','HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','','','HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','','','',NULL,'','','',NULL,'',''),(371,371,NULL,'','TepelnĂ© ÄŤerpadlo                                                              ','                                                                                                                                                                                                ',NULL,'TepelnĂ© ÄŤerpadlo','pĹ™Ă­pojka plynu od hodin aĹľ ke spotĹ™ebiÄŤi','','','','','','',NULL,'','                                                                                                                                                                                               ','                                                                                                                                                                                                ','                                                ','NemĂˇ komĂ­n',' ','','',NULL,'','','                                                                                                                                                                                                ','','','','','',NULL,'','                                                                                                                                                                                                ','                                                                                                                                                                                                ','','','','','',NULL,'','                                                                                                                                                                                                ','     yyy                                                                                                                                                                                           ',NULL,'',''),(372,372,NULL,'','','',NULL,'','','','','','','','',NULL,'','','','                                                ','',' ','','',NULL,'',NULL,'','','','','','',NULL,'',NULL,'','','','','','',NULL,'',NULL,NULL,NULL,'',''),(373,373,NULL,'','','',NULL,'','','','','','','','',NULL,'',' , ','','                                                ','',' ','','',NULL,'',NULL,'','','','','','',NULL,'',NULL,'','','','','','',NULL,'',NULL,NULL,NULL,'',''),(375,375,NULL,'','Protherm Panther Condens 30KKO 30kW\r\nKondezaÄŤnĂ­ kotel','',NULL,'Protherm Panther Condens 30KKO 30 kW','','','','30KKO-A(H-CZ)R1','','','',NULL,'','SystĂ©movĂ˝ vnitĹ™nĂ­ dodateÄŤnÄ› vloĹľkovanĂ˝ samostatnĂ˝ odvod spalin v provedenĂ­ C33, od Ricom Gas (souosĂ˝) 80Pp pevnĂˇ vloĹľka, pro odvod spalin od tzv. kondenzaÄŤnĂ­ho kotle na plynnĂˇ paliva. VypouzdĹ™en do Ĺˇachty o svÄ›tlosti 125 mm.','','                                                ','SamostatnĂˇ spalinovĂˇ cesta pro kondenzaÄŤnĂ­ kotel',' ','','',NULL,'','','','','','','','',NULL,'','','','','','','','',NULL,'','','',NULL,'',''),(376,376,NULL,'','','',NULL,'','','','','','','','','2022-02-16','14:00','','','','',' ','','',NULL,'',NULL,'','','','','','',NULL,'',NULL,'','','','','','',NULL,'',NULL,NULL,NULL,'',''),(378,378,NULL,'','Prime 24 - kondenzaÄŤnĂ­ kotel\r\nRozvody plynu od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ.','KondenzaÄŤnĂ­ kotel Baxi Prime 24 nainstalovanĂ˝ do novÄ› zĹ™Ă­zenĂ©ho odbÄ›rnĂ©ho mĂ­sta. NovĂ© rozvody topenĂ­, plynu a elektriky.',NULL,'BAXI prime 24 - kondenzaÄŤnĂ­ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','C13750985','','','','1999-11-30','','KomĂ­n systĂ©movĂ˝-Ricom gas Cvikov osazen Ocel/PP rourou o svÄ›tlosti DN 100/60 mm. CelkovĂˇ dĂ©lka 1,8 m. Novostavba bytovĂ© jednotky 1n.p.-nepodsklepenĂ˝, stĹ™echa valbovĂˇ. VyĂşstÄ›nĂ­ spalinovĂ© cesty - 1n.p. chodba.','',NULL,'KomĂ­n systĂ©movĂ˝-kondenzaÄŤnĂ­ kotel','KouĹ™ovod Â AL pevnĂˇ roura o svÄ›tlosti Â 100x60mm','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(380,380,NULL,'','Baxi Prime 24 - kondenzaÄŤnĂ­ kotel\r\nrozvod od uzĂˇvÄ›ru plynomÄ›ru aĹľ po plynovĂˇ zaĹ™izenĂ­','VĂ˝mÄ›na starĂ˝ kotel za novĂ˝ kotel nainstalovanĂ˝ do stĂˇvajĂ­cĂ­ho \r\nodbÄ›rnĂ©ho mĂ­sta.',NULL,'Baxi Prime 24 - kondenzaÄŤnĂ­ kotel','rozvod od plynomÄ›ru po plyn. zaĹ™Ă­zenĂ­','','','201137818','','','','2022-02-18','14:00','','','                ','KomĂ­n systĂ©movĂ˝-kondenzaÄŤnĂ­ kotel',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(382,382,NULL,'','                                                              ','byt majitele                                                                ',NULL,'','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','','','',NULL,'',' ,                                                                 ','                                                                ',NULL,'',' ','','',NULL,'','','                                                                ',NULL,'','','','',NULL,'','                                                                ','                                                                ',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(383,383,NULL,'','','2018-chybĂ­ zprava o rozvodech v domÄ›',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(384,384,NULL,'','','2018-chybĂ­ zprava o rozvodech v domÄ›',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(385,385,NULL,'','','2018-chybĂ­ zprava o rozvodech v domÄ›',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(386,386,NULL,'','','2018-chybĂ­ zprava o rozvodech v domÄ›',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(387,387,NULL,'','','2018-chybĂ­ zprava o rozvodech v domÄ›',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(390,390,NULL,'','','',NULL,'','','','','','','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(393,393,NULL,'',NULL,'',NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(400,400,NULL,'',NULL,'',NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(401,401,NULL,'',NULL,'',NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(402,402,NULL,'',NULL,'',NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(403,403,NULL,'',NULL,'',NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(404,404,NULL,'',NULL,'',NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(405,405,NULL,'',NULL,'',NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(407,407,NULL,'',NULL,'',NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(408,408,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(409,409,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(410,410,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(411,411,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(412,412,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(413,413,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(414,414,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(415,415,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(416,416,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(417,417,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(418,418,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(419,419,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(421,421,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(422,422,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(423,423,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(424,424,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(425,425,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(426,426,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(427,427,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(428,428,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(429,429,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(430,430,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(431,431,NULL,'','','2018-chybĂ­ zprava o rozvodech v domÄ›',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(432,432,NULL,'','','2018-chybĂ­ zprava o rozvodech v domÄ›',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(433,433,NULL,'','','2018-chybĂ­ zprava o rozvodech v domÄ›',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(434,434,NULL,'','','2018-chybĂ­ zprava o rozvodech v domÄ›',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(435,435,NULL,'','','2018-chybĂ­ zprava o rozvodech v domÄ›',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(436,436,NULL,'','','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','budova,  , ','','                ','budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(437,437,NULL,'','rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','','','','','','','',NULL,'','budova,  , ','','                ','budova',' ','','',NULL,'','','','','','','','',NULL,'','','','','','','','',NULL,'','','',NULL,'',''),(438,438,NULL,'','VIADRUS G25 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ\r\nplynovĂ˝ sporĂˇk                           ','                                ',NULL,'VIADRUS G25 - atmosfĂ©rickĂ˝ kotel, plyn kamna','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','plynovĂˇ kamna','',' ','','','','1999-11-30','','SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AL  H400  vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Viadrus   28 kW  v provedenĂ­ B- napojen kouĹ™ovodem AL -130mm. DĂ©lka kouĹ™ovodu 1,5m â€“osazen  1x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v suterĂ©nu .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  16m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  techn. mĂ­stnost - suterĂ©n .                                 ','                                ','                                ','SamostatnĂˇ Â spalinovĂˇ Â cesta N1','VĂ­cevrstvĂ­ zdÄ›nĂ˝ komĂ­n','','',NULL,'','','                                ',NULL,'','','','',NULL,'','                                ','                                ',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(439,439,'2022-05-16','','BAXI ECOFOUR 240F - turbo kotel\r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe                                                                                              ','                                                                                              ',NULL,'BAXI ECOFOUR 240F - turbo kotel','rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','122415652','','','','1999-11-30','','SamostatnĂˇ  spalinovĂˇ  cesta P1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ kouĹ™ovod  AL pevnĂˇ roura o svÄ›tlosti  80mm. SpotĹ™ebiÄŤ PET â€“ Baxi  - 24 kW  v provedenĂ­  C - napojen  kouĹ™ovodem AL  80mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝+ kontrolnĂ­ otvor  . KomĂ­novĂˇ  konstrukce zdÄ›nĂˇ osazena nerez ohebnou hadicĂ­ v provedenĂ­ pĹ™etlak 2x0,12mm .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 12m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  prĂˇdelna 1n.p.                                                                                                   ','                                                                                                ',NULL,'SamostatnĂˇ Â spalinovĂˇ Â cesta P1','KouĹ™ovod Â AL pevnĂˇ roura o svÄ›tlosti Â 80mm','','',NULL,'','','                                                                                                ',NULL,'','','','',NULL,'','                                                                                                ','                                                                                                ',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(440,440,NULL,'','Baxi Prime 24 - kondenzaÄŤnĂ­ kotel\r\nrozvod od uzĂˇvÄ›ru plynomÄ›ru aĹľ po plynovĂˇ zaĹ™izenĂ­','VĂ˝mÄ›na starĂ˝ kotel za novĂ˝ kotel nainstalovanĂ˝ do stĂˇvajĂ­cĂ­ho \r\nodbÄ›rnĂ©ho mĂ­sta.',NULL,'Baxi Prime 24 - kondenzaÄŤnĂ­ kotel','rozvod od plynomÄ›ru po plyn. zaĹ™Ă­zenĂ­','','','201137818','','','','2022-02-18','14:00','','','                ','KomĂ­n systĂ©movĂ˝-kondenzaÄŤnĂ­ kotel',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(441,441,NULL,'',NULL,'',NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(442,442,NULL,'','                                                              ','byt majitele                                                                ',NULL,'','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','','','',NULL,'',' ,                                                                 ','                                                                ',NULL,'',' ','','',NULL,'','','                                                                ',NULL,'','','','',NULL,'','                                                                ','                                                                ',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(443,443,NULL,'','                                                              ','byt majitele                                                                ',NULL,'','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','','','',NULL,'',' ,                                                                 ','                                                                ',NULL,'',' ','','',NULL,'','','                                                                ',NULL,'','','','',NULL,'','                                                                ','                                                                ',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(444,444,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(445,445,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(446,446,NULL,'','rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','','','','','','','',NULL,'','budova,  , ','','','budova',' ','','',NULL,'','','','','','','','',NULL,'','','','','','','','',NULL,'','','',NULL,'',''),(447,447,NULL,'','','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','budova,  , ','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(449,449,NULL,'','','',NULL,'','','','','','','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(450,450,NULL,'','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','',NULL,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel','rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','120259419','','','','1999-11-30','','SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400 vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu1,2mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  7m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba  1n.p.','',NULL,'SamostatnĂˇ Â spalinovĂˇ Â cesta N1','VĂ­cevrstvĂ­ zdÄ›nĂ˝ komĂ­n','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(451,451,NULL,'','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ','',NULL,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','120959571','','','','1999-11-30','','SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu1,2mosazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  5m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 2n.p.  ','','                ','SamostatnĂˇ Â spalinovĂˇ Â cesta N1','VĂ­cevrstvĂ­ zdÄ›nĂ˝ komĂ­n','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(452,452,NULL,'','BAXI Ecofour 24F - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ                                                                                               ','                                                                                                ',NULL,'BAXI Ecofour 24F - turbo kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','C13750985','','','','1999-11-30','','IndividuĂˇlnĂ­  samostatnĂˇspalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100x60mm. KouĹ™ovod s funkcĂ­ komĂ­na â€“ rourouAL.SpotĹ™ebiÄŤ -plyn.PetBaxi-24Kw  typu C.Napojen  kouĹ™ovodem o svÄ›tlosti 100x60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 1x kolenem 90 stupĹĹŻ s kontrolnĂ­m otvorem.ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  3n.p chodba.Kontrolu spalinovĂ© cesty lze provĂ©st z ĂşstĂ­ komĂ­na+ kontrolnĂ­m otvorem na kouĹ™ovodu.                                                                                                ','                                                                                                ',NULL,'SamostatnĂˇ Â spalinovĂˇ Â cesta P1','KouĹ™ovod Â AL pevnĂˇ roura o svÄ›tlosti Â 100x60mm','','',NULL,'','','                                                                ',NULL,'','','','',NULL,'','                                                                                        ','                                                                                                ',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(453,453,NULL,'','Prime 24 - kondenzaÄŤnĂ­ kotel\r\nRozvody plynu od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ.','KondenzaÄŤnĂ­ kotel Baxi Prime 24 nainstalovanĂ˝ do novÄ› zĹ™Ă­zenĂ©ho odbÄ›rnĂ©ho mĂ­sta. NovĂ© rozvody topenĂ­, plynu a elektriky.',NULL,'BAXI prime 24 - kondenzaÄŤnĂ­ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','C13750985','','','','1999-11-30','','KomĂ­n systĂ©movĂ˝-Ricom gas Cvikov osazen Ocel/PP rourou o svÄ›tlosti DN 100/60 mm. CelkovĂˇ dĂ©lka 1,8 m. Novostavba bytovĂ© jednotky 1n.p.-nepodsklepenĂ˝, stĹ™echa valbovĂˇ. VyĂşstÄ›nĂ­ spalinovĂ© cesty - 1n.p. chodba.','',NULL,'KomĂ­n systĂ©movĂ˝-kondenzaÄŤnĂ­ kotel','KouĹ™ovod Â AL pevnĂˇ roura o svÄ›tlosti Â 100x60mm','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(454,454,NULL,'','','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','','','','','',NULL,'','budova,  , ','',NULL,'budova',' ','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(455,455,NULL,'','rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','',NULL,'rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','','','','','','','',NULL,'','budova,  , ','','','budova',' ','','',NULL,'','','','','','','','',NULL,'','HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','','','HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','','','',NULL,'','','',NULL,'',''),(456,456,NULL,'','THERM 12 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ','',NULL,'THERM 12 - atmosfĂ©rickĂ˝ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','','','','','','','1999-11-30','','SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AL  H400 vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Therm na zemnĂ­ plyn    24 kW  v provedenĂ­- B- napojen kouĹ™ovodem AL -130mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  2x kolenem  90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝. KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p .ĂšÄŤinnĂˇ   vĂ˝Ĺˇka spalinovĂ© cesty  14m- neĂşÄŤinnĂˇ - 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  techn. mĂ­stnost 1n.p .','','                ','SamostatnĂˇ Â spalinovĂˇ Â cesta N1','VĂ­cevrstvĂ­ zdÄ›nĂ˝ komĂ­n','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(457,457,NULL,'','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','',NULL,'BAXI prime 24 - kondenzaÄŤnĂ­ kotel','rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','211339267','','','','1999-11-30','','SamostatnĂˇ  spalinovĂˇcesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 130mm - napojen na zdÄ›nĂ˝  komĂ­n - osazen AL  ohebnou vloĹľkou o prĹŻmÄ›ru 130mm. SpotĹ™ebiÄŤ plyn. PET  na zemnĂ­ plyn o vĂ˝konu 24kW  v provedenĂ­ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,5m - osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 9m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  koupelna2n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 2n.p.','','                ','SamostatnĂˇ Â spalinovĂˇ Â cesta N1',' ','','',NULL,'','','',NULL,'','','','',NULL,'','','',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(458,458,'2022-05-16','nenĂ­','Prime 24 - kondenzaÄŤnĂ­ kotel\r\nRozvody plynu od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ.           ','3x Plyn Topidlo BETA 4 - gamaty,plynovĂ˝ sporĂˇk ,rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe.\r\n31. 3. 2021 Byla provedena vĂ˝mÄ›na plynovĂ˝ch spotĹ™ebiÄŤĹŻ - plyn. kotel + radiĂˇtory                                  ',NULL,'BAXI prime 24 - kondenzaÄŤnĂ­ kotel','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','203937010','','','','1999-11-30','','NovĂ˝ kondenzaÄŤnĂ­ kotel-vĂ˝mÄ›na mĂ­sto gamat                              ','                                ',NULL,'KomĂ­n systĂ©movĂ˝kondenzaÄŤnĂ­ kotel-mĂ­sto gamat Â ',' ','','','1999-11-30','','','                                ',NULL,'','','','',NULL,'','                                ','                                ',NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(463,463,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(464,464,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(466,466,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(467,467,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(468,468,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(469,469,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(470,470,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'',''),(472,472,NULL,'',NULL,NULL,NULL,'','','','','','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','','','',NULL,'',NULL,NULL,NULL,'','');

#
# Structure for table "skontroly_typ"
#

CREATE TABLE `skontroly_typ` (
  `id` int NOT NULL AUTO_INCREMENT,
  `odkaz_skontroly_uk` int DEFAULT '0',
  `textA` varchar(30) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci DEFAULT '',
  `textB` varchar(30) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci DEFAULT '',
  `obor` tinyint DEFAULT '0',
  `ukon_akce` enum('A','K','O','V','N') CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci DEFAULT NULL,
  `poradi` tinyint(1) DEFAULT NULL,
  PRIMARY KEY (`id`),
  UNIQUE KEY `id` (`id`)
) ENGINE=MyISAM AUTO_INCREMENT=23 DEFAULT CHARSET=utf8mb4 COLLATE=utf8mb4_czech_ci ROW_FORMAT=DYNAMIC;

#
# Data for table "skontroly_typ"
#

INSERT INTO `skontroly_typ` VALUES (1,0,'Kontrola 1 plyn. zaĹ™Ă­zenĂ­','KONTROLA-1',0,'K',1),(2,0,'Kontrola 2 plyn. zaĹ™Ă­zenĂ­','KONTROLA-2',0,'K',2),(3,0,'9','REVIZE+KONTR',0,'K',3),(4,0,'VĂ˝chozĂ­ Revize plyn. zaĹ™Ă­zenĂ­','VĂťCH.REVIZE',0,'V',NULL),(5,0,'Oprava plyn. zaĹ™Ă­zenĂ­','OPRAVA',0,'O',NULL),(7,0,'VĂ˝chozĂ­ kontrola komĂ­nu','VĂťCH.REVIZE',1,'V',NULL),(8,0,'Oprava komĂ­nĹŻ','OPRAVA',1,'O',NULL),(9,0,'Kontrola elektrickĂ©ho zĹ™Ă­zenĂ­','KONTROLA',2,'K',1),(10,0,'VĂ˝chozĂ­ kontrola el. zaĹ™Ă­zenĂ­','VĂťCH.REVIZE',2,'V',NULL),(11,0,'Orava elektrickĂ©ho zaĹ™izenĂ­','OPRAVA',2,'O',NULL),(12,0,'Kontrola poĹľĂˇrnĂ­ho zaĹ™Ă­zenĂ­','KONTROLA',3,'K',1),(13,0,'Oprava poĹľĂˇrnĂ­ho zaĹ™Ă­zenĂ­','OPRAVA',3,'O',NULL),(14,0,'VĂ˝chozĂ­ kontrola poĹľ. zaĹ™izenĂ­','VĂťCH.REVIZE',3,'V',NULL),(15,0,'VypracovĂˇnĂ­ en. prĹŻkazu','ENERG.PRUKAZ',4,'K',1),(16,0,'Kontrola neprovedena','NEPROVEDENA',0,'N',NULL),(17,0,'Kontrola neprovedena','NEPROVEDENA',1,'N',NULL),(18,0,'Kontrola neprovedena','NEPROVEDENA',2,'N',NULL),(19,0,'Kontrola neprovedena','NEPROVEDENA',4,'N',1),(20,0,'Kontrola komĂ­nĹŻ','KONTROLA',1,'K',1);

#
# Structure for table "skontroly_uk"
#

CREATE TABLE `skontroly_uk` (
  `id` int NOT NULL AUTO_INCREMENT,
  `odkaz_skontroly_jn` int DEFAULT '0',
  `odkaz_skontroly_typ` tinyint DEFAULT '0',
  `odkaz_sadresar` int DEFAULT '0',
  `ukon_dat` date DEFAULT NULL,
  `obor` tinyint DEFAULT '0',
  `Ukon_zarizeni1` varchar(50) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci DEFAULT '',
  `Ukon_Typ_dalsi` tinyint DEFAULT '0',
  `Ukon_zarizeni2` varchar(50) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci DEFAULT '',
  `Ukon_zarizeni3` varchar(50) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci DEFAULT '',
  `Ukon_zarizeni4` varchar(50) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci DEFAULT '',
  `Ukon_Popis` text CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci,
  `Ukon_Poznamka` text CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci,
  `Ukon_Provedl` varchar(20) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci DEFAULT '',
  `Platba_Naj` varchar(20) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci DEFAULT '',
  `Platba_Maj` varchar(20) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci DEFAULT '',
  `Platba` enum('ANO','NE') CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT 'NE',
  `Platba_Dat` date DEFAULT NULL,
  `Platba_popis` varchar(50) CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT '',
  `Ukon_End` enum('ANO','NE') CHARACTER SET utf8mb4 COLLATE utf8mb4_czech_ci NOT NULL DEFAULT 'NE',
  UNIQUE KEY `id` (`id`)
) ENGINE=InnoDB AUTO_INCREMENT=1742 DEFAULT CHARSET=utf8mb4 COLLATE=utf8mb4_czech_ci ROW_FORMAT=DYNAMIC;

#
# Data for table "skontroly_uk"
#

INSERT INTO `skontroly_uk` VALUES (65,279,3,0,'2017-05-03',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','NutnĂˇ vĂ˝mÄ›na pĹ™eruĹˇovaÄŤe tahu + vĂ˝mÄ›na pĹ™Ă­vodnĂ­ hadice plynu.','pan SkĂˇla','','1000','ANO',NULL,'','ANO'),(67,276,1,0,'2017-05-03',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','plynovĂˇ kamna','','','VĹˇe v poĹ™Ăˇdku jen natĹ™Ă­t plynovod.','pan SkĂˇla','1000','','ANO',NULL,'','ANO'),(68,281,1,0,'2017-05-03',0,'',2,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','VyÄŤiĹˇtÄ›nĂ˝ vĹˇechny topidla. VĹˇe v poĹ™Ăˇdku.','pan SkĂˇla','400','600','ANO',NULL,'','ANO'),(69,332,1,0,'2017-05-03',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VyÄŤiĹˇtÄ›no. VĹˇe v poĹ™Ăˇdku.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(70,273,1,0,'2017-05-05',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VymÄ›nit hadici\r\nUzĂˇvÄ›r pĹ™ed hadici\r\nĹˇpatnĂ˝  prĹŻtokovĂ˝ snĂ­maÄŤ - vymÄ›nit\r\n\r\nKotel je poĹˇkozen nelze opravit \r\n\r\n\r\n','pan SkĂˇla','','','ANO',NULL,'','ANO'),(71,363,3,0,'2017-05-06',0,'',1,'','','','','VĹˇe v poĹ™Ăˇdku.','pan SkĂˇla','','400','ANO',NULL,'','ANO'),(72,364,3,0,'2017-05-06',0,'',1,'','','','','VĹˇe v poĹ™Ăˇdku. VyÄŤiĹˇtÄ›no.','pan SkĂˇla','','400','ANO',NULL,'','ANO'),(73,362,3,0,'2017-05-06',0,'',1,'','','','','VĹˇe v poĹ™Ăˇdku. VyÄŤistÄ›no','pan SkĂˇla','','400','ANO',NULL,'','ANO'),(74,272,1,0,'2017-05-06',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VĹˇe v poĹ™Ăˇdku. VyÄŤiĹˇtÄ›no','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(75,286,2,0,'2017-05-09',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VyÄŤiĹˇtÄ›no. VĹˇe ok','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(76,285,2,0,'2017-05-09',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VĹˇe v poĹ™Ăˇdku. VyÄŤiĹˇtÄ›no ','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(77,284,2,0,'2017-05-09',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VĹˇe v poĹ™Ăˇdku. VyÄŤiĹˇtÄ›no','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(78,365,2,0,'2017-05-09',0,'',3,'','','','','Postavit budku na hlavnĂ­ uzĂˇvÄ›r + natĹ™Ă­t trubku.','pan SkĂˇla','','400','ANO',NULL,'','ANO'),(83,290,1,0,'2017-05-15',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','Kotel vyÄŤiĹˇtÄ›nĂ˝ a zkontrolovĂˇny. VĹˇe v poĹ™Ăˇdku. Odstranit tÄ›snÄ›nĂ­ ve dveĹ™Ă­ ','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(84,331,1,147,'2017-05-15',0,'THERM 23LXI - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VyÄŤiĹˇtÄ›no a zkontrolovĂˇno. VĹˇe v poĹ™Ăˇdku.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(85,291,1,0,'2017-05-15',0,'',2,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','RozbitĂ˝ trojcestny ventil. Cena pĹ™ibliĹľnÄ› 5000Kc. DoporuÄŤeno vymÄ›nit kotel. Nastaveno pouze na ohĹ™ev teplĂ© vody.','pan SkĂˇla','0','','ANO',NULL,'','ANO'),(86,366,1,0,'2017-05-15',0,'',2,'','','','','VĹˇe v poĹ™Ăˇdku jen oznaÄŤit dveĹ™e hlavnĂ­m uzĂˇvÄ›rem plynu','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(87,292,1,0,'2017-05-15',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','NutnĂˇ vĂ˝mÄ›na desky. Chyba E35. Cena pĹ™ibliĹľnÄ› kolem 5000Kc. VĂ˝mÄ›na hadice. Jinak vĹˇe vyÄŤiĹˇtÄ›no a nastavena jiskra v kotli. VĹˇe ok\r\n\r\nVĹˇe bylo opraveno','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(88,298,1,0,'2017-05-17',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VyÄŤiĹˇtÄ›no a zkontrolovĂˇno. DoporuÄŤeno do koupelny co hlĂˇsiÄŤ. A vĂ˝mÄ›na plyn.hadice 60cm.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(89,304,1,0,'2017-05-17',0,'',2,'','','','','VyÄŤiĹˇtÄ›nĂ­ vĹˇe ok ale byl by dobrĂ˝ hlĂˇsiÄŤ co2 do koupelny.','pan SkĂˇla','400','','ANO',NULL,'','ANO'),(90,301,1,0,'2017-05-17',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VyÄŤiĹˇtÄ›no, vĹˇe v poĹ™Ăˇdku. ','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(92,294,1,0,'2017-05-19',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','ZkontrolovĂˇno a vyÄŤiĹˇtÄ›no. Koupit novou hadici 40cm\r\nmusĂ­ bĂ˝t revize','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(93,303,1,0,'2017-05-19',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','ZkontrolovĂˇno.','pan SkĂˇla','400','','ANO',NULL,'','ANO'),(94,293,1,0,'2017-05-19',0,'',2,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','VyÄŤiĹˇtÄ›no a zkontrolovĂˇno. VĹˇe ok','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(95,295,1,0,'2017-05-22',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','ZkontrolovĂˇno, vĹˇe ok. VymÄ›nit hadici + co hlĂˇsiÄŤ.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(96,327,2,0,'2017-06-06',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','Byl problĂ©m, Ĺľe kotel vypĂ­nal ohĹ™ev teplĂ© vody.\r\nByl zanesen vĂ˝mÄ›nĂ­k tahu\r\nBylo vĹˇe vyÄŤiĹˇtÄ›no vĹˇe ok ','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(101,296,4,0,'2017-06-09',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','ZapojenĂ­ a zprovoznÄ›nĂ­ kotle do provotu 9.6.2017.\r\nVĹˇe v poĹ™Ăˇdku.','pan SkĂˇla','','800','ANO',NULL,'','ANO'),(104,297,1,0,'2017-06-22',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VĹˇe v poĹ™Ăˇdku. ','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(105,305,2,0,'2017-06-22',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VĹˇe v poĹ™Ăˇdku ','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(106,306,2,0,'2017-06-22',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VĹˇe v poĹ™Ăˇdku.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(107,307,1,0,'2017-06-22',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VĹˇe v poĹ™Ăˇdku ','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(108,308,2,0,'2017-06-22',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VĹˇe v poĹ™Ăˇdku. ','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(109,316,3,0,'2017-06-23',0,'',1,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','VĹˇe v poĹ™Ăˇdku, jen vymÄ›nit plynovou hadici.','pan SkĂˇla','','1000','ANO',NULL,'','ANO'),(110,314,3,0,'2017-06-23',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VĹˇe ok, jen vymÄ›nit plyn. hadici','pan SkĂˇla','1000','','ANO',NULL,'','ANO'),(111,315,2,0,'2017-06-23',0,'',3,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','VĹˇe ok, jen vymÄ›nit hadici.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(112,327,5,0,'2017-07-03',0,'',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','Vse ok. Vymena hadice 50cm','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(113,320,3,0,'2017-07-03',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','Vycisteno ok','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(114,328,2,0,'2017-07-03',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','Vse ok vycisteno.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(115,323,2,0,'2017-07-03',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VĹˇe vyÄŤiĹˇtÄ›no. VĂ˝mÄ›na hadice 60cm + pojiĹˇĹĄovacĂ­ ventil','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(116,324,2,0,'2017-07-03',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','Vse ok. Vymenit hadici 60cm','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(117,309,4,0,'2017-08-22',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','cena se musĂ­ dohodnout','pan SkĂˇla','','800','ANO',NULL,'','ANO'),(118,256,2,0,'2017-09-25',0,'',3,'rozvod plynu','','','','VĹˇe v poĹ™Ăˇdku ','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(119,257,2,0,'2017-09-25',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VĹˇe v poĹ™Ăˇdku. DoporuÄŤenĂ­ montĂˇĹľe odvodu spalin na odtah nad kotlem vĹŻÄŤi vodÄ› ','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(120,257,5,0,'2017-09-25',0,'',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','Kotel vyÄŤiĹˇtÄ›nĂ˝. Problem v odtahu. Zkontrolovat odtah','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(121,264,3,0,'2017-09-25',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VyÄŤiĹˇtÄ›no. Nutno vymenit pĹ™eruĹˇovaÄŤ tahu. + vymenit hadici','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(122,259,2,0,'2017-09-25',0,'',3,'rozvod od podruĹľ. plynomÄ›ru po spotĹ™ebiÄŤ','','','','VĹˇe v poĹ™Ăˇdku. VyÄŤiĹˇtÄ›no','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(123,258,2,0,'2017-09-25',0,'',3,'rozvod od podruĹľ. plynomÄ›ru po spotĹ™ebiÄŤ','','','','VyÄŤiĹˇtÄ›no. VĹˇe ok.','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(124,262,3,0,'2017-09-26',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','Kontrola  a revize 26.9.2017','pan SkĂˇla','400','600','ANO',NULL,'','ANO'),(126,302,1,0,'2017-09-26',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VyÄŤiĹˇtÄ›no. VĹˇe v poĹ™Ăˇdku.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(136,291,7,0,'2017-11-02',1,'oddÄ›lenĂ© odkouĹ™enĂ­ plast komĂ­n a kuchyĹ',6,NULL,NULL,NULL,'KomĂ­n zdÄ›nĂ˝ ,vĂ­cevrstvĂ˝vyvloĹľkovĂˇn AC- ohebnou hadicĂ­ o prĹŻmÄ›ru 120mm â€“ osazena koaxiĂˇlnÄ› PP ohebnou dn 80mm. CelkovĂˇ vĂ˝Ĺˇka 8,5m. ÄŚinĹľovnĂ­ dĹŻm- 5n.p podsklepenĂ˝, stĹ™echa sedlovĂˇ. VyĂşstÄ›nĂ­ 90 stupĹĹŻ v koupelnÄ›2n.p. SpotĹ™ebiÄŤ plyn. kotel-Baxinapojen PP kouĹ™ovodem.','zaĹ™Ă­zenĂ­ 1: oddÄ›lenĂ© odkouĹ™enĂ­ plastovĂˇ roura do komĂ­na a nasĂˇvĂˇnĂ­ vzduchu dĂ­ra ven z kuchynÄ›. viz. obrĂˇzek','pan AbrahĂˇm','','1100','ANO',NULL,'','ANO'),(138,319,2,0,'2017-07-03',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(139,256,6,0,'2017-09-13',1,'AL kouĹ™. koax. 80 mm, ind. spal. cesta P1',6,'','','','AL kouĹ™. koax. 80 mm, ind. spal. cesta P1,  , ','VĹˇe v poĹ™Ăˇdku','pan AbrahĂˇm','','240','ANO',NULL,'','ANO'),(140,257,6,0,'2017-09-13',1,'AL kouĹ™. koax. 100x60 m, ind. spal cesta P1',6,'','','','AL kouĹ™. koax. 100x60 m, ind. spal cesta P1,  , ','vĹˇe v poĹ™Ăˇdku','pan AbrahĂˇm','','240','ANO',NULL,'','ANO'),(141,258,6,0,'2017-09-13',1,'AL kouĹ™. koax. 100x60 m, ind. spal cesta P1',6,'','','','AL kouĹ™. koax. 100x60 m, ind. spal cesta P1,  , ','vĹˇe ok ','pan AbrahĂˇm','','240','ANO',NULL,'','ANO'),(142,259,6,0,'2017-09-13',1,'AL kouĹ™. koax. 100x60 m, ind. spal cesta P1',6,'','','','AL kouĹ™. koax. 100x60 m, ind. spal cesta P1,  , ','VĹˇe ok','pan AbrahĂˇm','','240','ANO',NULL,'','ANO'),(143,262,6,0,'2017-09-13',1,'AL jednovrstvĂ˝ kouĹ™ovod N1 samostatnĂ˝',6,'','','','AL jednovrstvĂ˝ kouĹ™ovod N1 samostatnĂ˝,  , ','vĹˇe ok','pan AbrahĂˇm','','350','ANO',NULL,'','ANO'),(144,263,6,0,'2017-09-13',1,'AL jednovrstvĂ˝ kouĹ™ovod N1 samostatnĂ˝',6,'','','','AL jednovrstvĂ˝ kouĹ™ovod N1 samostatnĂ˝,  , ','vĹˇe ok','pan AbrahĂˇm','','350','ANO',NULL,'','ANO'),(145,291,4,0,'2017-10-30',0,'',1,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','ZkontrolovĂˇno vĹˇe ok, MontĂˇĹľ novĂ©ho kondenzaÄŤnĂ­ho kotle\r\n','pan SkĂˇla','','1200','ANO',NULL,'','ANO'),(146,266,6,0,'2017-09-13',1,'AL jednovrstvĂ˝ kouĹ™ovod N1 samostatnĂ˝',6,'','','','AL jednovrstvĂ˝ kouĹ™ovod N1 samostatnĂ˝,  , ','vĹˇe ok','pan AbrahĂˇm','','350','ANO',NULL,'','ANO'),(147,265,6,0,'2017-09-13',1,'AL jednovrstvĂ˝ kouĹ™ovod N1 samostatnĂ˝',6,'','','','AL jednovrstvĂ˝ kouĹ™ovod N1 samostatnĂ˝,  , ','vĹˇe ok','pan AbrahĂˇm','','350','ANO',NULL,'','ANO'),(148,264,6,0,'2017-10-30',1,'AL jednovrstvĂ˝ kouĹ™ovod N1 samostatnĂ˝',6,'','','','AL jednovrstvĂ˝ kouĹ™ovod N1 samostatnĂ˝,  , ','vĹˇe ok','pan AbrahĂˇm','','350','ANO',NULL,'','ANO'),(149,296,7,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ˝ vyvloĹľkovĂˇn AC- ohebnou hadicĂ­ o prĹŻmÄ›ru 120mm â€“ osazena koaxiĂˇlnÄ› AK ohebnou provedenĂ­ pĹ™etlak dn 80mm. CelkovĂˇ vĂ˝Ĺˇka 4m. ÄŚinĹľovnĂ­ dĹŻm- 5n.p podsklepenĂ˝, stĹ™echa sedlovĂˇ. VyĂşstÄ›nĂ­ 90 stupĹĹŻ v koupelnÄ›4n.p. SpotĹ™ebiÄŤ plyn. kotel-Baxinapojen AL kouĹ™ovodem.','VĹˇe v poĹ™Ăˇdku ','pan AbrahĂˇm','','600','ANO',NULL,'','ANO'),(150,332,6,0,'2017-11-02',1,'',6,'','','','SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 130 mm-napojen na zdÄ›nĂ˝ komĂ­n AL ohebnou vloĹľkou o prĹŻmÄ›ru 130 mm. DĂ©lka kouĹ™ovodu 0,5 m- osazen 1 x kolenem 90 stupĹĹŻ.','VĹˇe zkontrolovĂˇno ok','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(151,272,6,0,'2017-11-02',1,'SamostatnĂˇ Â spalinovĂˇ Â cesta P1',6,'','','','SamostatnĂˇ  spalinovĂˇ  cesta P1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ kouĹ™ovod  AL pevnĂˇ roura o svÄ›tlosti  80mm. SpotĹ™ebiÄŤ PET â€“ Baxi  - 24 kW  v provedenĂ­  C - napojen  kouĹ™ovodem AL  80mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝+ kontrolnĂ­ otvor  . KomĂ­novĂˇ  konstrukce zdÄ›nĂˇ osazena nerez ohebnou hadicĂ­ v provedenĂ­ pĹ™etlak 2x0,12mm .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 12m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  prĂˇdelna 1n.p.   ','VĹˇe zkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(152,284,6,0,'2017-11-02',1,'SamostatnĂˇ  spalinovĂˇ  cesta N1',6,'','','','SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400 vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu1,2mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  7m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba  1n.p.','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(153,285,6,0,'2017-11-02',1,'SamostatnĂˇ  spalinovĂˇ  cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu1,2mosazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  5m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 2n.p.  ','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(154,286,6,0,'2017-11-02',1,'SamostatnĂˇ  spalinovĂˇ  cesta P1',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­  samostatnĂˇspalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100x60mm. KouĹ™ovod s funkcĂ­ komĂ­na â€“ rourouAL.SpotĹ™ebiÄŤ -plyn.PetBaxi-24Kw  typu C.Napojen  kouĹ™ovodem o svÄ›tlosti 100x60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 1x kolenem 90 stupĹĹŻ s kontrolnĂ­m otvorem.ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  3n.p chodba.Kontrolu spalinovĂ© cesty lze provĂ©st z ĂşstĂ­ komĂ­na+ kontrolnĂ­m otvorem na kouĹ™ovodu.','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(155,290,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 1,8m osazen 1x kolenem 90 stupĹĹŻ a 1x 60 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 13,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba1n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(156,292,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,8m osazen 2x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 11,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba2n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 2n.p.','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(157,293,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 130mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AL ohebnou vloĹľkou o prĹŻmÄ›ru 125mm. SpotĹ™ebiÄŤ plyn. PETThermona- 24kW v provedenĂ­  Bnapojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 2m osazen 1x kolenem 90 stupĹĹŻ a 1x 45 stupĹĹŻ .ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 8,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  koupelna  3n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(158,294,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 2m osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 8,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  koupelna 3n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(159,298,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 20kW v provedenĂ­ B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 0,8m osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 4,3m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“5n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 5n.p.KomĂ­n v ĂşstĂ­ osazen  3m nĂˇstavcem. ','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(160,301,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­ B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 15,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba 1n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(161,303,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,' , ','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(162,304,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,' , ','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(163,305,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­  B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba3n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(164,306,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nnĂ˝ komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­ B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba 3n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(165,308,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­ B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 2x kolenem 90 stupĹĹŻ a 1x30 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 4m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“4n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 4n.p.','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(166,323,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400 vloĹľkou   DN 120mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­ B- napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupĹĹŻ - kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  12m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba   1n.p.  ','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(167,319,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400 vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­  B- napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90 stupĹĹŻ â€“ kouĹ™ovod  rozebĂ­ratelnĂ˝. KontrolnĂ­  dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  9m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  kuchyĹ  2n.p.','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(168,320,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400 vloĹľkou   DN 120mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­  B- napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.UÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  6m- neuÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  kuchyĹ  2n.p. ','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(169,324,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400 vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­  B - napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupnĹŻ- kouĹ™ovod  rozebĂ­ratelnĂ˝ .KontrolnĂ­  dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  12m â€“ neĂşÄŤinnĂˇ - 0,3 m. ','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(170,325,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400 vloĹľkou   DN 120mm. SpotĹ™ebiÄŤ  PET â€“Baxi  - 24 kW  v provedenĂ­  B - napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“ osazen  1x kolenem  90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p .UÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  9m - neuÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba   2n.p.','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(171,326,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ   spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400 vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­  B- napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.UÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  9m â€“ neĂşÄŤinnĂˇ - 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  kuchyĹ   2n.p. ','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(172,327,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400 vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ  PET â€“Baxi  - 24 kW  v provedenĂ­ B - napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90 stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 3n.p .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  6m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba   3n.p.','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(173,328,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ   cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400  vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­  B- napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupĹĹŻ - kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 3n.p .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  9m- neĂşÄŤinnĂˇ - 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  kuchyĹ   3n.p. ','ZkontrolovĂˇno','pan AbrahĂˇm','','550','ANO',NULL,'','ANO'),(177,258,5,0,'2017-11-23',0,'',0,'rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','','Oprava plynu, vĂ˝mÄ›na cĂ­vky na uzavĂ­rĂˇnĂ­ plynu\r\nVĂ˝mÄ›na plynovĂ˝ch hodin viz. Dokumentace','pan SkĂˇla','','700','ANO',NULL,'','ANO'),(178,295,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 20kW v provedenĂ­- B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 1,2m -  osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 5,3m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  koupelna4n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 4n.p.','vĹˇe ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(179,297,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,' , ','vĹˇe ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(180,315,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena ALkoaxiĂˇlnĂ­m kouĹ™ovodem â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti 100/60mm. SpotĹ™ebiÄŤ PETâ€“Baxi  - 24kW v provedenĂ­- B-napojenkoaxiĂˇlnĂ­m  kouĹ™ovodem AL+AL -100/60mm. DĂ©lka kouĹ™ovodu2mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovodrozebĂ­ratelnĂ˝ .ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty 2m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ koupelna  3n.p.','vĹˇe ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(181,316,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena ALkoaxiĂˇlnĂ­m kouĹ™ovodem â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti 100/60mm. SpotĹ™ebiÄŤ PETBaxi  - 24kW v provedenĂ­ B-napojen koaxiĂˇlnĂ­m  kouĹ™ovodem AL+AL -100/60mm. DĂ©lka kouĹ™ovodu2mosazenna pĹ™Ă­mo - kouĹ™ovod rozebĂ­ratelnĂ˝ .ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty 2m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ koupelna  3n.p.','vĹˇe ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(182,302,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­  B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 15,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba1n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','vĹˇe ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(183,307,6,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­  B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba 3n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','vĹˇe ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(186,333,4,0,'2017-12-08',0,'',1,'rozvod plynu','','','','provedena vĂ˝chozĂ­ revize na kondenzaÄŤnĂ­m kotly\r\nvĹˇe ok','pan SkĂˇla','','','ANO',NULL,'','ANO'),(191,276,6,0,'2017-11-09',1,'SamostatnĂˇ  spalinovĂˇ  cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AL  H400  vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Viadrus   28 kW  v provedenĂ­ B- napojen kouĹ™ovodem AL -130mm. DĂ©lka kouĹ™ovodu 1,5m â€“osazen  1x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v suterĂ©nu .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  16m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  techn. mĂ­stnost - suterĂ©n . ','vĹˇe ok','pan AbrahĂˇm','450','','ANO',NULL,'','ANO'),(192,279,6,0,'2017-11-09',1,'SamostatnĂˇ  spalinovĂˇ  cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AL  H400 vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Therm na zemnĂ­ plyn    24 kW  v provedenĂ­- B- napojen kouĹ™ovodem AL -130mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  2x kolenem  90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝. KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p .ĂšÄŤinnĂˇ   vĂ˝Ĺˇka spalinovĂ© cesty  14m- neĂşÄŤinnĂˇ - 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  techn. mĂ­stnost 1n.p .','VĹˇe ok.','pan AbrahĂˇm','450','','ANO',NULL,'','ANO'),(193,313,6,0,'2017-12-22',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta P1, kterĂˇ je tvoĹ™ena AL koaxiĂˇlnĂ­m kouĹ™ovodem  kouĹ™ovodem  â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti 100/60mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­  B- napojen koaxiĂˇlnĂ­m  kouĹ™ovodem AL +AL -100/60mm. DĂ©lka kouĹ™ovodu 2,5m â€“ osazen  2x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝.  ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 3m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  restaurace 1 n.p .   ','vĹˇe ok','pan AbrahĂˇm','450','','ANO',NULL,'','ANO'),(194,314,6,0,'2017-11-09',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta P1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti  80mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­  C - napojen  kouĹ™ovodem AL  80mm. DĂ©lka kouĹ™ovodu 10m â€“osazen  2x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝  .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  salon  2 n.p .  ','VĹˇe ok','pan AbrahĂˇm','','450','ANO',NULL,'','ANO'),(195,331,6,0,'2017-11-22',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ   spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena  AL  kouĹ™ovodem 130mm - napojen na zdÄ›nĂ˝  komĂ­n - osazen AL  ohebnou  vloĹľkou o prĹŻmÄ›ru 130mm. SpotĹ™ebiÄŤ plyn. PET  Therm  o vĂ˝konu 24kW  v provedenĂ­ B - napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,3m - osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 15,5m- neĂşÄŤinnĂˇ  0,3m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  kancelĂˇĹ™  1n.p KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','VĹˇe ok','pan AbrahĂˇm','','450','ANO',NULL,'','ANO'),(196,343,6,0,'2017-09-13',1,'PL KomĂ­n sp. cesta N1 AL kouĹ™ovod 120 mm',6,'','','','PL KomĂ­n sp. cesta N1 AL kouĹ™ovod 120 mm, TP KomĂ­n kouĹ™ovod 120mm - zĂˇkaz, ','PlynovĂ˝ komĂ­n ok\r\nKomĂ­n na tuhĂˇ paliva je neschopnĂ˝ provozu a je zakĂˇzĂˇn pouĹľĂ­vat','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(197,269,6,0,'2017-09-13',1,'PL KomĂ­n sp. cesta N1 AL kouĹ™ovod 120 mm',6,'','','','PL KomĂ­n sp. cesta N1 AL kouĹ™ovod 120 mm, TP KomĂ­n FE kouĹ™ovod 120mm tuhĂˇ paliva, ','KomĂ­n na tuhĂˇ paliva je v provozu schopnĂ˝\r\n','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(198,279,5,0,'2018-02-08',0,'',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','','','','Provedena vĂ˝mÄ›na ÄŤerpadla u kotle ','pan SkĂˇla','','3500','ANO',NULL,'','ANO'),(199,292,5,0,'2018-02-08',0,'',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','','','','vĂ˝mÄ›na elektroniky na kotly (E35)','pan SkĂˇla','','5000','ANO',NULL,'','ANO'),(202,290,3,0,'2018-07-09',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, VĹˇe-ok, Odstranit tÄ›snÄ›nĂ­ ve dveĹ™Ă­ ','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(203,292,3,0,'2018-07-09',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','','','','Provedena vĂ˝mÄ›na hadice, SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, , OstatnĂ­ vĹˇe-ok','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(204,293,3,0,'2018-07-09',0,'',1,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','Kotel Therm, SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ-ok, NevhodnĂˇ hadice ke sporĂˇku, Doplnit hlĂˇsiÄŤe CO, doplnit vodu','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(205,294,3,0,'2018-07-09',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, vymÄ›nit plynovou hadici','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(206,291,1,0,'2018-07-09',0,'',2,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, VĹˇe-ok','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(207,331,3,147,'2018-07-09',0,'THERM 23LXI - atmosfĂ©rickĂ˝ kotel',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, VymÄ›nit hadici, OstatnĂ­ vĹˇe ok.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(208,295,3,0,'2018-07-09',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, VĹˇe-ok, VymÄ›nit plynovou hadici, CO hlasiÄŤ','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(209,298,3,0,'2018-07-09',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, VymÄ›nit plynovou hadici, Do koupelny CO hlĂˇsiÄŤ,\r\nVĹˇe ostatnĂ­-ok','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(211,366,3,0,'2018-07-09',0,'',1,'','','','','DomovnĂ­ rozvod od HUP po uzĂˇvÄ›ry spotĹ™ebnĂ­ch rozvodĹŻ-ok, OznaÄŤit dveĹ™e u sklepa, Ĺľe je tam hlavnĂ­ uzĂˇvÄ›r plynu.','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(212,367,3,0,'2018-07-09',0,'',1,'','','','','DomovnĂ­ rozvod od HUP po uzĂˇvÄ›ry spotĹ™ebnĂ­ch rozvodĹŻ-ok, OznaÄŤit dveĹ™e do sklepa, Ĺľe je tam uzĂˇvÄ›r plynu.','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(213,301,3,0,'2018-07-10',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, VĹˇe-ok\r\n','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(214,309,3,0,'2018-07-10',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, OstatnĂ­-ok','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(215,302,3,0,'2018-07-10',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','ZprĂˇva o rozvodu nelze otevĹ™Ă­t, OstatnĂ­-ok','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(216,303,3,0,'2018-07-10',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, VĹˇe-ok','pan SkĂˇla','400','','ANO',NULL,'','ANO'),(217,308,3,0,'2018-07-10',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, OstatnĂ­-ok','pan SkĂˇla','600+400','','ANO',NULL,'','ANO'),(218,304,3,0,'2018-07-10',0,'',1,'plynovod','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, OstatnĂ­-ok','pan SkĂˇla','400','','ANO',NULL,'','ANO'),(219,305,3,0,'2018-07-10',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, OstatnĂ­-ok','pan SkĂˇla','600+400','','ANO',NULL,'','ANO'),(220,306,3,0,'2018-07-10',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, OstatnĂ­-ok','pan SkĂˇla','600+400','','ANO',NULL,'','ANO'),(222,276,3,0,'2018-07-11',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','plynovĂˇ kamna','','','NatĹ™Ă­t plynovod - je to uvedeno jako zĂˇvada pĹ™i reviznĂ­ kontrole ze dne 03.05.2017\r\nSpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe\r\n- ok\r\nChybĂ­ uzĂˇvÄ›r u plynovĂ©ho sporĂˇku\r\nNevyhovujĂ­cĂ­ hadice u sporĂˇku','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(223,273,3,0,'2018-07-11',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','Likvidace kotle bude instalovĂˇn novĂ˝ kotel','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(224,363,3,0,'2018-07-11',0,'',1,'','','','','DomovnĂ­ rozvod od HUP po uzĂˇvÄ›ry spotĹ™ebnĂ­ch rozvodĹŻ\r\nvĹˇe ok','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(225,362,3,0,'2018-07-11',0,'',1,'','','','','DomovnĂ­ rozvod od HUP po uzĂˇvÄ›ry spotĹ™ebnĂ­ch rozvodĹŻ-ok','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(226,272,3,0,'2018-07-11',0,'',1,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, VĹˇe-ok','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(227,279,3,0,'2018-07-11',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, VymÄ›nit hadici + ventily','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(228,281,3,0,'2018-07-11',0,'',1,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, VĹˇe ok','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(229,332,3,0,'2018-07-11',0,'',1,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, VĹˇe ok','pan SkĂˇla','600+400','','ANO',NULL,'','ANO'),(230,364,3,0,'2018-07-11',0,'',1,'','','','','DomovnĂ­ rozvod od HUP po uzĂˇvÄ›ry spotĹ™ebnĂ­ch rozvodĹŻ-ok','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(231,365,3,0,'2018-07-13',0,'',1,'','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, ChybĂ­ vyzdĂ­t kiosek HUP','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(232,284,3,0,'2018-07-13',0,'',1,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, VĹˇe-ok','pan SkĂˇla','600+400','','ANO',NULL,'','ANO'),(233,316,3,0,'2018-07-13',0,'',1,'','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, OstatnĂ­-ok, VymÄ›nit hadici u kotle!','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(234,285,3,0,'2018-07-13',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, vĹˇe-ok','pan SkĂˇla','600+400','','ANO',NULL,'','ANO'),(235,323,3,0,'2018-07-13',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, OstatnĂ­-ok, VymÄ›nit hadici','pan SkĂˇla','600+400','','ANO',NULL,'','ANO'),(236,324,3,0,'2018-07-13',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','Ĺ patnĂˇ hadice u plynovĂ©ho kotle\r\nĹ patnĂˇ digestoĹ™\r\nNevyhovujĂ­cĂ­ revize','pan SkĂˇla','600+400','','ANO',NULL,'','ANO'),(237,325,3,0,'2018-07-13',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, OstatnĂ­-ok','pan SkĂˇla','600+400','','ANO',NULL,'','ANO'),(238,326,3,0,'2018-07-13',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','Ĺ patnĂ˝ pojistnĂ˝ ventil\r\nĹ patnĂˇ digestoĹ™\r\nNevyhovujĂ­cĂ­ revize','pan SkĂˇla','','600+400','ANO',NULL,'','ANO'),(239,327,3,0,'2018-07-13',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','Ĺ patnĂˇ hadice u plynovĂ©ho kotle\r\nĹ patnĂˇ digestoĹ™\r\nNevyhovujĂ­cĂ­ revize','pan SkĂˇla','600+400','','ANO',NULL,'','ANO'),(240,328,3,0,'2018-07-13',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, OstatnĂ­-ok','pan SkĂˇla','600+400','','ANO',NULL,'','ANO'),(241,319,3,0,'2018-07-13',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, OstatnĂ­-ok','pan SkĂˇla','600+400','','ANO',NULL,'','ANO'),(242,262,3,0,'2018-07-16',0,'',1,'rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok,Kotel ok, VymÄ›nit hadici','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(243,266,3,0,'2018-07-16',0,'',1,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, Kotel ok,NevhodnĂˇ hadice i jejĂ­ pouĹľitĂ­- nahradit vhodnou a instalovat tak aby nehrozilo nebezpeÄŤĂ­ spĂˇlenĂ­ hadice','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(244,265,3,0,'2018-07-16',0,'',1,'rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ, spotĹ™ebiÄŤe-ok, Kotel ok, VymÄ›nit hadici u plynovĂ©ho sporĂˇku','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(245,264,3,0,'2018-07-16',0,'',1,'rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','plynovĂ˝ sporĂˇk','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ-ok, Kotel ok,\r\nvymÄ›nit hadici u plynovĂ©ho kotle, vymÄ›nit pĹ™eruĹˇovaÄŤ tahu, vymÄ›nit hoĹ™Ăˇk, vymÄ›nit ucpĂˇvku trojcest ventilu.\r\n\r\npĹ™edpoklĂˇdanĂˇ cena za hoĹ™Ăˇk, pĹ™eruĹˇovaÄŤ tahu a ucpĂˇvku cca 5-6 tisĂ­c KÄŤ','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(246,361,3,0,'2018-07-16',0,'',1,'','','','','dvĂ­Ĺ™ka kiosku jsou zniÄŤenĂˇ\r\noznaÄŤit kiosek samolepou HUP','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(247,269,3,0,'2018-07-16',0,'',1,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','','NĂ­zkotlakĂ˝ rozvod do 0,5 Mpa-ok,Kotel-ok\r\nvymÄ›nit hadice u plynovĂ˝ch kotlĹŻ\r\nvymÄ›nit dvĂ­Ĺ™ka u kiosku s HUP\r\noznaÄŤit kiosek samolepkou HUP','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(248,343,3,0,'2018-07-16',0,'',1,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','','vymÄ›nit hadice u plynovĂ˝ch kotlĹŻ\r\nvymÄ›nit dvĂ­Ĺ™ka u kiosku s HUP\r\noznaÄŤit kiosek samolepkou HUP','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(249,258,3,0,'2018-07-16',0,'',1,'rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ-chybĂ­, Kotel ok','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(250,259,3,0,'2018-07-16',0,'',1,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ-chybĂ­, Kotel ok','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(251,256,3,0,'2018-07-16',0,'',1,'rozvod plynu','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ-chybĂ­, Kotel-ok','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(252,257,3,0,'2018-07-16',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ-chybĂ­, Kotel ok','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(253,333,3,0,'2018-07-16',0,'',1,'rozvod plynu','','','','SpotĹ™ebnĂ­ rozvod, pĹ™ipojenĂ­ spotĹ™ebiÄŤĹŻ-chybĂ­, Kotel ok','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(254,269,5,0,'2018-10-08',0,'',0,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','','Provedena oprava vĂ˝mÄ›na zĂˇkladnĂ­ desky + prĂˇce\r\n5251,0 KÄŤ','pan SkĂˇla','','5251','ANO',NULL,'','ANO'),(255,286,6,0,'2018-12-27',1,'Samostatnďż˝  spalinovďż˝  cesta P1',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­  samostatnĂˇspalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100x60mm. KouĹ™ovod s funkcĂ­ komĂ­na â€“ rourouAL.SpotĹ™ebiÄŤ -plyn.PetBaxi-24Kw  typu C.Napojen  kouĹ™ovodem o svÄ›tlosti 100x60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 1x kolenem 90 stupĹĹŻ s kontrolnĂ­m otvorem.ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  3n.p chodba.Kontrolu spalinovĂ© cesty lze provĂ©st z ĂşstĂ­ komĂ­na+ kontrolnĂ­m otvorem na kouĹ™ovodu.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(256,324,6,0,'2018-12-27',1,'',6,NULL,NULL,NULL,' , ','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(257,323,6,0,'2018-12-27',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400 vloĹľkou   DN 120mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­ B- napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupĹĹŻ - kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  12m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba   1n.p.  ','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(258,320,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400 vloĹľkou   DN 120mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­  B- napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.UÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  6m- neuÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  kuchyĹ  2n.p. ','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(259,319,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400 vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­  B- napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90 stupĹĹŻ â€“ kouĹ™ovod  rozebĂ­ratelnĂ˝. KontrolnĂ­  dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  9m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  kuchyĹ  2n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(260,328,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ   cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400  vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­  B- napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupĹĹŻ - kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 3n.p .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  9m- neĂşÄŤinnĂˇ - 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  kuchyĹ   3n.p. ','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(261,325,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400 vloĹľkou   DN 120mm. SpotĹ™ebiÄŤ  PET â€“Baxi  - 24 kW  v provedenĂ­  B - napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“ osazen  1x kolenem  90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p .UÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  9m - neuÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba   2n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(262,327,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400 vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ  PET â€“Baxi  - 24 kW  v provedenĂ­ B - napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90 stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 3n.p .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  6m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba   3n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(263,326,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ   spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400 vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­  B- napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.UÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  9m â€“ neĂşÄŤinnĂˇ - 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  kuchyĹ   2n.p. ','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(264,316,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena ALkoaxiĂˇlnĂ­m kouĹ™ovodem â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti 100/60mm. SpotĹ™ebiÄŤ PETBaxi  - 24kW v provedenĂ­ B-napojen koaxiĂˇlnĂ­m  kouĹ™ovodem AL+AL -100/60mm. DĂ©lka kouĹ™ovodu2mosazenna pĹ™Ă­mo - kouĹ™ovod rozebĂ­ratelnĂ˝ .ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty 2m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ koupelna  3n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(265,315,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena ALkoaxiĂˇlnĂ­m kouĹ™ovodem â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti 100/60mm. SpotĹ™ebiÄŤ PETâ€“Baxi  - 24kW v provedenĂ­- B-napojenkoaxiĂˇlnĂ­m  kouĹ™ovodem AL+AL -100/60mm. DĂ©lka kouĹ™ovodu2mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovodrozebĂ­ratelnĂ˝ .ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty 2m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ koupelna  3n.p.','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(266,285,6,0,'2018-11-30',1,'Samostatnďż˝  spalinovďż˝  cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu1,2mosazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  5m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 2n.p. ','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(267,284,6,0,'2018-11-30',1,'SamostatnĂˇ  spalinovĂˇ  cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400 vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu1,2mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  7m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba  1n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(268,309,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,' , ','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(269,308,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­ B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 2x kolenem 90 stupĹĹŻ a 1x30 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 4m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“4n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 4n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(270,307,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­  B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba 3n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(271,306,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nnĂ˝ komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­ B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba 3n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(272,305,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­  B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba3n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(273,304,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,' , ','byt mĂˇ osazeny 2 x gamaty','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(274,303,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,' , ','mĂˇ gamaty','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(275,302,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­  B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 15,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba1n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(276,301,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­ B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 15,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba 1n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(277,290,6,0,'2018-11-30',1,'AK kouĹ™ovod 120 mm',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 1,8m osazen 1x kolenem 90 stupĹĹŻ a 1x 60 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 13,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba1n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(278,292,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,8m osazen 2x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 11,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba2n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 2n.p.','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(279,293,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 130mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AL ohebnou vloĹľkou o prĹŻmÄ›ru 125mm. SpotĹ™ebiÄŤ plyn. PETThermona- 24kW v provedenĂ­  Bnapojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 2m osazen 1x kolenem 90 stupĹĹŻ a 1x 45 stupĹĹŻ .ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 8,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  koupelna  3n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(280,294,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 2m osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 8,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  koupelna 3n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(281,295,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 20kW v provedenĂ­- B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 1,2m -  osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 5,3m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  koupelna4n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 4n.p.','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(282,296,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ˝ vyvloĹľkovĂˇn AC- ohebnou hadicĂ­ o prĹŻmÄ›ru 120mm â€“ osazena koaxiĂˇlnÄ› AK ohebnou provedenĂ­ pĹ™etlak dn 80mm. CelkovĂˇ vĂ˝Ĺˇka 4m. ÄŚinĹľovnĂ­ dĹŻm- 5n.p podsklepenĂ˝, stĹ™echa sedlovĂˇ. VyĂşstÄ›nĂ­ 90 stupĹĹŻ v koupelnÄ›4n.p. SpotĹ™ebiÄŤ plyn. kotel-Baxinapojen AL kouĹ™ovodem.','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(283,298,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 20kW v provedenĂ­ B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 0,8m osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 4,3m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“5n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 5n.p.KomĂ­n v ĂşstĂ­ osazen  3m nĂˇstavcem. ','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(284,291,6,0,'2018-11-30',1,'oddÄ›lenĂ© odkouĹ™enĂ­ plast komĂ­n a kuchyĹ',6,NULL,NULL,NULL,'KomĂ­n zdÄ›nĂ˝ ,vĂ­cevrstvĂ˝vyvloĹľkovĂˇn AC- ohebnou hadicĂ­ o prĹŻmÄ›ru 120mm â€“ osazena koaxiĂˇlnÄ› PP ohebnou dn 80mm. CelkovĂˇ vĂ˝Ĺˇka 8,5m. ÄŚinĹľovnĂ­ dĹŻm- 5n.p podsklepenĂ˝, stĹ™echa sedlovĂˇ. VyĂşstÄ›nĂ­ 90 stupĹĹŻ v koupelnÄ›2n.p. SpotĹ™ebiÄŤ plyn. kotel-Baxinapojen PP kouĹ™ovodem.','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(285,332,6,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 130 mm-napojen na zdÄ›nĂ˝ komĂ­n AL ohebnou vloĹľkou o prĹŻmÄ›ru 130 mm. DĂ©lka kouĹ™ovodu 0,5 m- osazen 1 x kolenem 90 stupĹĹŻ.','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(288,279,5,0,'2019-02-08',0,'',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','','','','Provedena vĂ˝mÄ›na plynovĂ© hadice + ventilĹŻ','pan SkĂˇla','','','ANO',NULL,'','ANO'),(289,294,5,0,'2019-02-08',0,'',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','Provedena vĂ˝mÄ›na plynovĂ© hadice, VĹˇe-ok','Markovi','','','ANO',NULL,'','ANO'),(290,295,5,0,'2019-02-08',0,'',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','Provedena vĂ˝mÄ›na plynovĂ© hadice.','Markovi','','','ANO',NULL,'','ANO'),(293,262,6,0,'2018-11-30',1,'Sam.spal. cesta N1, AL jednovr. kouĹ™ovod',6,NULL,NULL,NULL,'Sam.spal. cesta N1, AL jednovr. kouĹ™ovod, Kom zdÄ›nĂ˝ vĂ˝cevr. vyvloĹľ. AL oheb 120 mm, ','Kontrola ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(294,263,6,0,'2018-11-30',1,'Sam.spal. cesta N1, AL jednovr. kouĹ™ovod',6,NULL,NULL,NULL,'Sam.spal. cesta N1, AL jednovr. kouĹ™ovod, Kom zdÄ›nĂ˝ vĂ˝cevr. vyvloĹľ. AL oheb 120 mm, ','Kontrola ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(295,266,6,0,'2018-11-30',1,'Sam.spal. cesta N1, AL jednovr. kouĹ™ovod',6,NULL,NULL,NULL,'Sam.spal. cesta N1, AL jednovr. kouĹ™ovod, Kom zdÄ›nĂ˝ vĂ˝cevr. vyvloĹľ. AL oheb 120 mm, ','Kontrola ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(296,265,6,0,'2018-11-30',1,'Sam.spal. cesta N1, AL jednovr. kouĹ™ovod',6,NULL,NULL,NULL,'Sam.spal. cesta N1, AL jednovr. kouĹ™ovod, Kom zdÄ›nĂ˝ vĂ˝cevr. vyvloĹľ. AL oheb 120 mm, ','Kontrola ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(297,264,6,0,'2018-11-30',1,'Sam.spal. cesta N1, AL jednovr. kouĹ™ovod',6,NULL,NULL,NULL,'Sam.spal. cesta N1, AL jednovr. kouĹ™ovod, Kom zdÄ›nĂ˝ vĂ˝cevr. vyvloĹľ. AL oheb 120 mm, ','Kontrola ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(298,256,6,0,'2018-11-30',1,'IndividuĂˇlnĂ­ spal cesta P1',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spal cesta P1, PP kouĹ™ovod-koaxiĂˇlnĂ­ 100/60 , ','KomĂ­n ok, ĹˇpatnÄ› napsanĂ˝ plynovĂ˝ kotel. MĂˇ bĂ˝t Thermona Duo 50T','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(299,333,6,0,'2018-11-30',1,'IndividuĂˇlnĂ­ spal cesta P1',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spal cesta P1, PP kouĹ™ovod-koaxiĂˇlnĂ­ 100/60, ','KomĂ­n ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(300,257,6,0,'2018-11-30',1,'IndividuĂˇlnĂ­ spal cesta P1',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spal cesta P1, AL kouĹ™ovod-koaxiĂˇlnĂ­ 100/60, ','KomĂ­n ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(301,258,6,0,'2018-11-30',1,'IndividuĂˇlnĂ­ spal cesta P1',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spal cesta P1, AL kouĹ™ovod-koaxiĂˇlnĂ­ 100/60, ','KomĂ­n ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(303,343,6,0,'2018-11-30',1,'IndividuĂˇlnĂ­ sam spalinovĂˇ cesta N1',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ sam spalinovĂˇ cesta N1, AL kouĹ™ovod 120mm, IndividuĂˇlnĂ­ sam spalinovĂˇ cesta N1, FE kouĹ™ovod 120 mm','KomĂ­n na plyn je ok,KomĂ­n na tuhĂˇ paliva je nezpĹŻsobilĂ˝ a nesmĂ­ se pouĹľĂ­vat','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(304,269,6,0,'2018-11-30',1,'IndividuĂˇlnĂ­ sam spalinovĂˇ cesta N1',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ sam spalinovĂˇ cesta N1, AL kouĹ™ovod 120mm, IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, FE kouĹ™ovod 110 mm','KomĂ­n na plyn ok, KomĂ­n na tuhĂˇ paliva ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(309,255,1,0,'2019-05-10',0,'',2,'','','','','vĹˇe ok','pan JiĹ™Ă­ Vrba','','','ANO',NULL,'','ANO'),(310,256,1,0,'2019-05-10',0,'',2,'rozvod plynu','','','','vĹˇe ok','pan JiĹ™Ă­ Vrba','','','ANO',NULL,'','ANO'),(312,257,1,0,'2019-05-10',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','vĹˇe ok','pan JiĹ™Ă­ Vrba','','','ANO',NULL,'','ANO'),(313,258,1,0,'2019-05-10',0,'',2,'rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','','vĹˇe ok','pan JiĹ™Ă­ Vrba','','','ANO',NULL,'','ANO'),(314,259,1,0,'2019-05-10',0,'',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','','vĹˇe ok','pan JiĹ™Ă­ Vrba','','','ANO',NULL,'','ANO'),(316,291,2,0,'2019-10-14',0,'',3,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','Kotel v poĹ™Ăˇdku, ĹˇpatnÄ› tÄ›snĂ­ ventil na trubce.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(317,293,1,0,'2019-10-14',0,'',2,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','Kotel v poĹ™Ăˇdku, pan si ucpĂˇvĂˇ prĹŻduch ve dveĹ™Ă­.\r\nInstalovat do Koupelny HlĂˇsiÄŤ Ăşniku CO!!!!','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(318,290,1,0,'2019-10-14',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','VĹˇe v poĹ™Ăˇdku.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(319,292,1,0,'2019-10-14',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','','','','VĹˇe v poĹ™Ăˇdku.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(320,366,1,0,'2019-10-14',0,'',2,'','','','','VĹˇe v poĹ™Ăˇdku','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(322,294,1,0,'2019-10-14',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','Instalovat HlĂˇsiÄŤ Ăşniku CO!!!','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(323,295,1,0,'2019-10-14',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','Instalovat hlĂˇsiÄŤ Ăşniku CO!!!','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(324,298,1,0,'2019-10-14',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','VĹˇe ok, vymÄ›nit hadici','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(325,331,1,147,'2019-10-14',0,'THERM 23LXI - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VĹˇe v poĹ™Ăˇdku.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(326,301,1,0,'2019-10-15',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','VĹˇe v poĹ™Ăˇdku. OdpojenĂ˝ hlĂˇsiÄŤ.\r\nZprovoznit hlĂˇsiÄŤ Ăşniku CO!!!','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(327,302,1,0,'2019-10-15',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','VĹˇe v poĹ™Ăˇdku. Byla nutnĂˇ vĂ˝mÄ›na cĂ­vka plynovĂ©ho ventilu','pan SkĂˇla','1090','','ANO',NULL,'','ANO'),(328,303,1,0,'2019-10-15',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','VĹˇe v poĹ™Ăˇdku','pan SkĂˇla','400','','ANO',NULL,'','ANO'),(329,304,1,0,'2019-10-15',0,'',2,'','','','1x PT Gamat 461\r\n1x PT MORATHERM','VĹˇe v poĹ™Ăˇdku.','pan SkĂˇla','400','','ANO',NULL,'','ANO'),(330,305,1,0,'2019-10-15',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','VĹˇe v poĹ™Ăˇdku.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(331,306,1,0,'2019-10-15',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','VĹˇe v poĹ™Ăˇdku','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(333,308,1,0,'2019-10-15',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','VĹˇe v poĹ™Ăˇdku.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(334,367,1,0,'2019-10-15',0,'',2,'','','','','VĹˇe v poĹ™Ăˇdku','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(335,309,1,0,'2019-10-15',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','VĹˇe v poĹ™Ăˇdku.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(336,276,1,0,'2019-10-16',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','plynovĂˇ kamna','','','VĹˇe v poĹ™Ăˇdku, jen malĂ˝ kousek plynovĂ© trubky do natĹ™Ă­t','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(337,332,1,0,'2019-10-16',0,'',2,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','','ChybĂ­ CO2 hlĂˇsiÄŤ, jelikoĹľ je kotel v koupelnÄ›. jinak vĹˇe ok','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(338,364,1,0,'2019-10-16',0,'',2,'','','','','VĹˇe v poĹ™Ăˇdku','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(339,279,1,0,'2019-10-16',0,'THERM 12',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','','','','VĹˇe v poĹ™Ăˇdku, jen odpojit ventilĂˇtor u kotle.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(340,281,1,0,'2019-10-16',0,'',2,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','Upevnit topidlo v zadnĂ­m pokoji.','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(341,362,1,0,'2019-10-16',0,'',2,'','','','','VĹˇe ok','pan SkĂˇla','','','ANO',NULL,'','ANO'),(342,272,1,0,'2019-10-16',0,'',2,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','BAXI ECOFOUR 240F - turbo kotel\r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe ','VĹˇe v poĹ™Ăˇdku ok','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(343,363,1,0,'2019-10-16',0,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry',3,'','','','','VĹˇe ok','pan SkĂˇla','','600','ANO','2019-10-16','','ANO'),(345,285,1,0,'2019-10-17',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','VĹˇe v poĹ™Ăˇdku','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(346,284,1,0,'2019-10-17',0,'',2,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','','VĹˇe v poĹ™Ăˇdku','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(347,365,1,0,'2019-10-17',0,'',2,'','','','','StĂˇle chybĂ­ budka na plyn','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(348,316,1,0,'2019-10-17',0,'',2,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','VĹˇe v poĹ™Ăˇdku','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(353,262,1,0,'2019-10-21',0,'',2,'rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','','Vymenit hadici u PK','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(354,266,1,0,'2019-10-21',0,'',2,'rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','','Vymenit hadici u plynoveho sporaku.\r\nVymenena icpavka TMV.','','950','','ANO',NULL,'','ANO'),(355,264,1,0,'2019-10-21',0,'',2,'rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','plynovĂ˝ sporĂˇk','','','Vymenit prerusovac,vymenik a ucpaku tmv. Zvazit vymenu kotle.Predbezna cena 10 000kÄŤ. Domluveno na 4.11.2019. Skala\r\nVymenit hadici. Markovi','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(358,265,1,0,'2019-10-21',0,'',2,'rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','','Vse ok.','','600','','ANO',NULL,'','ANO'),(359,323,1,0,'2019-10-22',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','Kontrola PK ok. \r\nVymenit hadici u PK!','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(360,324,1,0,'2019-10-22',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','Kotel ok. Vymenit hadici u kotle.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(361,325,1,0,'2019-10-22',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','Vse ok','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(363,319,1,0,'2019-10-22',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','Vse ok.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(364,327,1,0,'2019-10-22',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','Kotel ok. Vymenit hadici u kotle','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(365,328,1,0,'2019-10-22',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','Vse ok.','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(369,313,16,0,'2018-07-13',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','pan SĂ­gl nezastiĹľen','pan SkĂˇla','','','ANO',NULL,'','ANO'),(370,313,16,0,'2019-10-17',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','pan SĂ­gl nezastiĹľen','pan SkĂˇla','','','ANO',NULL,'','ANO'),(371,326,16,0,'2019-10-22',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','pani VyhnalovĂˇ nezastiĹľena','pan SkĂˇla','','','ANO',NULL,'','ANO'),(372,286,16,0,'2018-07-13',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','Daniel Marek - nezastiĹľen','pan SkĂˇla','','','ANO',NULL,'','ANO'),(373,307,16,0,'2018-07-10',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','pan Pergler nezastiĹľen','pan SkĂˇla','','','ANO',NULL,'','ANO'),(374,368,16,0,'2018-07-13',0,'',3,'','','','','Neprovedeno','pan SkĂˇla','','','ANO',NULL,'','ANO'),(375,314,16,0,'2018-07-13',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','pani HrabĂˇkovĂˇ nezastiĹľen','pan SkĂˇla','','','ANO',NULL,'','ANO'),(377,315,16,0,'2018-07-13',0,'',3,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','pan KuiĹˇ nezastiĹľen','pan SkĂˇla','','','ANO',NULL,'','ANO'),(378,370,16,0,'2018-07-13',0,'',3,'','','','','Neprovedena','pan SkĂˇla','','','ANO',NULL,'','ANO'),(379,369,16,0,'2018-07-13',0,'',3,'','','','','Neprovedena','pan SkĂˇla','','','ANO',NULL,'','ANO'),(381,296,16,0,'2018-07-09',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','pan Synek-nezastiĹľen','pan SkĂˇla','','','ANO',NULL,'','ANO'),(382,269,16,0,'2019-10-21',0,'',3,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','','pan KrÄŤka nezastizen','','','','ANO',NULL,'','ANO'),(383,343,16,0,'2019-10-21',0,'',3,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','','pan MarĹˇĂ­k nezastizen','pan SkĂˇla','','','ANO',NULL,'','ANO'),(386,263,16,0,'2018-07-16',0,'',3,'rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','','Mudr PokornĂ˝ nezastiĹľen','pan SkĂˇla','','','ANO',NULL,'','ANO'),(387,363,16,0,'2018-07-16',0,'',3,'','','','','Neprovedena','pan SkĂˇla','','','ANO',NULL,'','ANO'),(388,359,16,0,'2018-07-16',0,'',3,'','','','','Neprovedena','pan SkĂˇla','','','ANO',NULL,'','ANO'),(391,370,16,0,'2017-07-03',0,'',3,'','','','','neprovedena','pan SkĂˇla','','','ANO',NULL,'','ANO'),(393,325,16,0,'2017-07-03',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','neprovedena','pan SkĂˇla','','','ANO',NULL,'','ANO'),(394,326,16,0,'2017-07-03',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','neprovedena','pan SkĂˇla','','','ANO',NULL,'','ANO'),(395,369,16,0,'2017-07-03',0,'',3,'','','','','neprovedena','pan SkĂˇla','','','ANO',NULL,'','ANO'),(397,367,16,0,'2017-06-22',0,'',3,'','','','','neprovedena','pan SkĂˇla','','','ANO',NULL,'','ANO'),(398,368,16,0,'2017-06-23',0,'',3,'','','','','neprovedena','pan SkĂˇla','','','ANO',NULL,'','ANO'),(399,313,16,0,'2017-06-23',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','pan SĂ­gl nepzastiĹľen','pan SkĂˇla','','','ANO',NULL,'','ANO'),(400,361,16,0,'2017-09-25',0,'',3,'','','','','neprovedena','pan SkĂˇla','','','ANO',NULL,'','ANO'),(401,269,16,0,'2017-09-25',0,'',3,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','','pan KrÄŤka nezastiĹľen','pan SkĂˇla','','','ANO',NULL,'','ANO'),(402,343,16,0,'2017-09-25',0,'',3,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','','pan MarĹˇĂ­k nezastiĹľen','pan SkĂˇla','','','ANO',NULL,'','ANO'),(404,263,16,0,'2017-09-25',0,'',3,'rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','','Mudr pokornĂ˝ nezastiĹľen','pan SkĂˇla','','','ANO',NULL,'','ANO'),(405,266,16,0,'2017-09-25',0,'',3,'rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','','pan Topinka nezastiĹľen','pan SkĂˇla','','','ANO',NULL,'','ANO'),(406,265,16,0,'2017-09-25',0,'',3,'rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','','pan Ĺ rĂˇmek nezastiĹľen','pan SkĂˇla','','','ANO',NULL,'','ANO'),(407,359,16,0,'2017-09-25',0,'',3,'','','','','neprovedena','pan SkĂˇla','','','ANO',NULL,'','ANO'),(418,368,2,0,'2019-10-17',0,'',3,'','','','','VĹˇe v poĹ™Ăˇdku','pan SkĂˇla','','','ANO',NULL,'','ANO'),(423,276,17,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AL  H400  vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Viadrus   28 kW  v provedenĂ­ B- napojen kouĹ™ovodem AL -130mm. DĂ©lka kouĹ™ovodu 1,5m â€“osazen  1x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v suterĂ©nu .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  16m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  techn. mĂ­stnost - suterĂ©n . ','Neprovedena','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(424,279,17,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AL  H400 vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Therm na zemnĂ­ plyn    24 kW  v provedenĂ­- B- napojen kouĹ™ovodem AL -130mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  2x kolenem  90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝. KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p .ĂšÄŤinnĂˇ   vĂ˝Ĺˇka spalinovĂ© cesty  14m- neĂşÄŤinnĂˇ - 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  techn. mĂ­stnost 1n.p .','Neprovedena','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(425,272,17,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta P1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ kouĹ™ovod  AL pevnĂˇ roura o svÄ›tlosti  80mm. SpotĹ™ebiÄŤ PET â€“ Baxi  - 24 kW  v provedenĂ­  C - napojen  kouĹ™ovodem AL  80mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝+ kontrolnĂ­ otvor  . KomĂ­novĂˇ  konstrukce zdÄ›nĂˇ osazena nerez ohebnou hadicĂ­ v provedenĂ­ pĹ™etlak 2x0,12mm .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 12m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  prĂˇdelna 1n.p.   ','Neprovedena','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(426,331,17,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ   spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena  AL  kouĹ™ovodem 130mm - napojen na zdÄ›nĂ˝  komĂ­n - osazen AL  ohebnou  vloĹľkou o prĹŻmÄ›ru 130mm. SpotĹ™ebiÄŤ plyn. PET  Therm  o vĂ˝konu 24kW  v provedenĂ­ B - napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,3m - osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 15,5m- neĂşÄŤinnĂˇ  0,3m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  kancelĂˇĹ™  1n.p KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','Neprovedena','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(427,309,17,0,'2017-11-02',1,'',6,NULL,NULL,NULL,'','Neprovedena','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(429,313,17,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta P1, kterĂˇ je tvoĹ™ena AL koaxiĂˇlnĂ­m kouĹ™ovodem  kouĹ™ovodem  â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti 100/60mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­  B- napojen koaxiĂˇlnĂ­m  kouĹ™ovodem AL +AL -100/60mm. DĂ©lka kouĹ™ovodu 2,5m â€“ osazen  2x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝.  ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 3m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  restaurace 1 n.p .   ','Neprovedena','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(430,314,17,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta P1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti  80mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­  C - napojen  kouĹ™ovodem AL  80mm. DĂ©lka kouĹ™ovodu 10m â€“osazen  2x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝  .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  salon  2 n.p .  ','Neprovedena','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(431,357,17,0,'2018-11-30',1,'',6,NULL,NULL,NULL,'Neprovedena','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(432,263,2,0,'2019-10-21',0,'',3,'rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','','Vymenit hadici u PK','','600','','ANO',NULL,'','ANO'),(433,333,1,0,'2019-05-10',0,'',2,'rozvod plynu','','','','vĹˇe ok JiĹ™Ă­ Vrba','pan JiĹ™Ă­ Vrba','','','ANO',NULL,'','ANO'),(448,258,5,0,'2019-11-21',0,'',0,'rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','',NULL,'VĂ˝mÄ›na zĂˇkladnĂ­ desky','pan SkĂˇla','','','ANO',NULL,'','ANO'),(450,276,5,122,'2019-11-10',0,'',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','plynovĂˇ kamna','','','NeĹˇel kotel - byl vyhozenĂ˝ jistiÄŤ (jistiÄŤ je souÄŤĂˇstĂ­ kotle)\r\n\r\nVymÄ›nÄ›n odruĹˇovacĂ­ kondezĂˇtor ze starĂ©ho kotle + vymÄ›nÄ›na pojistka 2A.\r\nSkĂˇla','pan SkĂˇla','?','','ANO',NULL,'','ANO'),(451,378,4,0,'2020-03-03',0,'',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','KOndenzaÄŤnĂ­ kotel Baxi Prima 24. Rozvody plynu od plynomÄ›ru aĹľ po kotelspotĹ™ebiÄŤ  o','VĂ˝chozĂ­ revize rozvodĹŻ plynu od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ\r\nVĂ˝chozĂ­ revize a zprovoznÄ›nĂ­ KondenzaÄŤnĂ­ho kotle Baxi Prime 24\r\nvĹˇe ok','p.SkĂˇla, p.Vrba','ano','','ANO','2020-03-03','nĂˇjemce ','ANO'),(452,378,7,0,'2019-11-29',1,'',6,NULL,NULL,NULL,'KomĂ­n systĂ©movĂ˝-Ricom gas Cvikov osazen Ocel/PP rourou o svÄ›tlosti DN 100/60 mm. CelkovĂˇ dĂ©lka 1,8 m. Novostavba bytovĂ© jednotky 1n.p.-nepodsklepenĂ˝, stĹ™echa valbovĂˇ. VyĂşstÄ›nĂ­ spalinovĂ© cesty - 1n.p. chodba.','vĹˇe ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(453,314,5,0,'2019-12-04',0,'',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','VĂ˝mÄ›na hadice','Markovi','','','ANO',NULL,'','ANO'),(454,286,5,0,'2019-12-04',0,'',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','BAXI Ecofour 24F turbo kotel','Hadice zde ĹľĂˇdnĂˇ nenĂ­, zapojeno na pĹ™Ă­mo\r\n','Markovi','','','ANO',NULL,'','ANO'),(455,316,5,0,'2019-12-06',0,'',0,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','BAXI Main 24i turbo kotel','VĂ˝mÄ›na hadice ','Markovi','','','ANO',NULL,'','ANO'),(456,314,1,0,'2019-10-17',0,'',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','',NULL,'ok','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(457,314,5,0,'2019-12-04',0,'',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','VĂ˝mÄ›na NTS sondy zĂˇsobnĂ­ku TUV.\r\nOprava zatĂ­m neuhrazena - zkuĹˇebnĂ­ provoz','pan SkĂˇla','950','','ANO',NULL,'','ANO'),(459,320,16,0,'2019-10-22',0,'',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','nezastiĹľen','pan SkĂˇla','','','ANO',NULL,'','ANO'),(460,264,5,0,'2019-12-12',0,'',0,'rozvood od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','plynovĂ˝ sporĂˇk','','','Oprava plyn kotle.\r\nVymena vymeniku, prerusovace tahu, ucpavky trojcest ventilu, izolace spalovaci komory.','pan SkĂˇla','','12000','ANO',NULL,'','ANO'),(461,327,5,0,'2019-12-13',0,'',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','VĂ˝mÄ›na hadice','Markovi','','','ANO',NULL,'','ANO'),(462,276,5,0,'2019-12-13',0,'',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','plynovĂˇ kamna','','','Trubka je jiĹľ natĹ™enĂˇ ','Markovi','','','ANO',NULL,'','ANO'),(463,323,5,0,'2019-12-17',0,'',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','VĂ˝mÄ›na plynovĂ© hadice','Markovi','','','ANO',NULL,'','ANO'),(464,324,5,0,'2019-12-18',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','vĂ˝mÄ›na plynovĂˇ hadice ','Markovi','','','ANO',NULL,'','ANO'),(465,294,5,0,'2020-01-09',0,'',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','Honeywell XC70-CS','NainstalovanĂ˝ CO hlĂˇsiÄŤ - je tĹ™eba doplnit dodatek ke smlouvÄ›','Markovi','','','ANO',NULL,'','ANO'),(466,295,5,0,'2020-01-09',0,'',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','Honeywell XC70-CS','NainstalovanĂ˝ co hlĂˇsiÄŤ - je tĹ™eba doplnit dodatek ke smlouvÄ›','Markovi','','','ANO',NULL,'','ANO'),(468,371,3,0,'2019-11-29',0,'TepelnĂ© ÄŤerpadlo',1,'','','','TepelnĂ© ÄŤerpadlo','Revize tepelnĂ©ho ÄŤerpadla ok','','','','ANO',NULL,'','ANO'),(469,258,6,0,'2019-12-20',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­  samostatnĂˇ spalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100/60mm. KouĹ™ovod s funkcĂ­ komĂ­na veden pĹ™es stĹ™echu do venkovnĂ­ho prostoru. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PetBaxi-24Kw  typu C. Napojen koaxiĂˇlnĂ­m kouĹ™ovodem o svÄ›tlosti 100/60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  2n.p fa. Nespo','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(470,259,6,0,'2019-12-20',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­  samostatnĂˇ spalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100/60mm. KouĹ™ovod s funkcĂ­ komĂ­na veden pĹ™es stĹ™echu do venkovnĂ­ho prostoru. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PetBaxi-24Kw  typu C. Napojen koaxiĂˇlnĂ­m kouĹ™ovodem o svÄ›tlosti 100/60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  2n.p fa. Nespo.\r\nKotel slouĹľĂ­ pro prodejnu Barev LakĹŻ','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(471,257,6,0,'2019-12-20',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­  samostatnĂˇ spalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100/60mm. KouĹ™ovod s funkcĂ­ komĂ­na veden pĹ™es stĹ™echu do venkovnĂ­ho prostoru rourou AL. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PetBaxi-24Kw  typu C. Napojen kouĹ™ovodem o svÄ›tlosti 100/60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 2x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  2n.p fa.TruhlĂˇrna.\r\n','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(472,333,6,0,'2019-12-20',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­  samostatnĂˇ spalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100/60mm. KouĹ™ovod s funkcĂ­ komĂ­na veden pĹ™es obvodovou zeÄŹ do venkovnĂ­ho prostoru rourou PP. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PetBaxi-24Kw  typu C. Napojen kouĹ™ovodem o svÄ›tlosti 100/60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,5m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe 1n.p technickĂˇ mĂ­stnost-prodejna.\r\n','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(473,256,6,0,'2019-12-20',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ samostatnĂˇ spalinovĂˇ  cesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 80mm. KouĹ™ovod s funkcĂ­ komĂ­na veden pĹ™es stĹ™echu do venkovnĂ­ho prostoru rourou AL. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn Pet Thermona-24kW - typu C. Napojen kouĹ™ovodem o svÄ›tlosti 80mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen napĹ™Ă­mo. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,5m-neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe 1n.p ĂşklidovĂˇ mĂ­stnost.','','','','','ANO',NULL,'','ANO'),(474,379,6,0,'2019-12-20',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena FE kouĹ™ovodem-110 mm. KouĹ™ovod osazen 2x kolenem 90 stupĹĹŻ o dĂ©lce 1,3 m. SpotĹ™ebiÄŤ-lokĂˇlnĂ­ na tuhĂˇ paliva 6 kW typ B.\r\nKomĂ­n zdÄ›nĂ˝ jednovrstvĂ­ o svÄ›tlosti 150mm. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 5,5 m - neĂşÄŤinnĂˇ 1,2 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe 1n.p-Hala ÄŤĂ­slo 2 - MarĹˇĂ­k.','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(475,343,6,0,'2019-12-20',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem-120 mm. KouĹ™ovod osazen 1x kolenem 90 stupĹĹŻ o dĂ©lce 0,7 m. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PETBaxi-24kW Typu B. KomĂ­n zdÄ›nĂ˝ osazen AL H400 o prĹŻmÄ›ru 120mm. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 5,5 m - neĂşÄŤinnĂˇ 0,2 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe 1n.p-Hala ÄŤĂ­slo 1 - MarĹˇĂ­k.','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(476,269,6,0,'2019-12-20',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem-120 mm. KouĹ™ovod osazen 1x kolenem 90 stupĹĹŻ o dĂ©lce 0,7 m. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PETBaxi-24kW Typu B. KomĂ­n zdÄ›nĂ˝ osazen AL H400 o prĹŻmÄ›ru 120mm. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 5,5 m - neĂşÄŤinnĂˇ 0,2 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe 1n.p-Hala ÄŤĂ­slo 3 - KrÄŤka.','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(477,264,6,0,'2019-12-20',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - chodba 2n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AL ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 2 x 90stupĹĹŻ z pevnĂ©ho hlinĂ­ku o prĹŻmÄ›ru 120 mm a dĂ©lce 1,2 m. ĂšÄŤinnĂˇ dĂ©lka 8 m-neĂşÄŤinnĂˇ 0,3 m. ','','','','','ANO',NULL,'','ANO'),(478,265,6,0,'2019-12-20',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - chodba 2n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AC ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 1 x 90stupĹĹŻ z pevnĂ©ho nerezu o prĹŻmÄ›ru 120 mm a dĂ©lce 1,2 m. ĂšÄŤinnĂˇ dĂ©lka 8 m-neĂşÄŤinnĂˇ 0,3 m. ','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(479,266,6,0,'2019-12-20',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - kuchyĹ 2n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AL ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 1 x 90 a 1x45 stupĹĹŻ z pevnĂ©ho nerezu o prĹŻmÄ›ru 120 mm a dĂ©lce 0,6 m. ĂšÄŤinnĂˇ dĂ©lka 8 m-neĂşÄŤinnĂˇ 0,3 m. ','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(480,263,6,0,'2019-12-20',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - technickĂˇ mĂ­stnost 1n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AL ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 1 x 90 stupĹĹŻ z pevnĂ©ho hlinĂ­ku o prĹŻmÄ›ru 120 mm a dĂ©lce 0,6 m. ĂšÄŤinnĂˇ dĂ©lka 11 m-neĂşÄŤinnĂˇ 0,3 m. ','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(481,262,6,0,'2019-12-20',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - oprdinace 1n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AL ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 1 x 90 stupĹĹŻ z pevnĂ©ho hlinĂ­ku o prĹŻmÄ›ru 120 mm a dĂ©lce 0,8 m. ĂšÄŤinnĂˇ dĂ©lka 11 m-neĂşÄŤinnĂˇ 0,3 m. ','','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(482,276,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AL  H400  vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Viadrus   28 kW  v provedenĂ­ B- napojen kouĹ™ovodem AL -130mm. DĂ©lka kouĹ™ovodu 1,5m â€“osazen  1x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v suterĂ©nu .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  16m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  techn. mĂ­stnost - suterĂ©n . ','Ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(483,272,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta P1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ kouĹ™ovod  AL pevnĂˇ roura o svÄ›tlosti  80mm. SpotĹ™ebiÄŤ PET â€“ Baxi  - 24 kW  v provedenĂ­  C - napojen  kouĹ™ovodem AL  80mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝+ kontrolnĂ­ otvor  . KomĂ­novĂˇ  konstrukce zdÄ›nĂˇ osazena nerez ohebnou hadicĂ­ v provedenĂ­ pĹ™etlak 2x0,12mm .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 12m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  prĂˇdelna 1n.p.   ','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(484,279,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AL  H400 vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Therm na zemnĂ­ plyn    24 kW  v provedenĂ­- B- napojen kouĹ™ovodem AL -130mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  2x kolenem  90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝. KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p .ĂšÄŤinnĂˇ   vĂ˝Ĺˇka spalinovĂ© cesty  14m- neĂşÄŤinnĂˇ - 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  techn. mĂ­stnost 1n.p .','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(485,332,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇcesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 130mm - napojen na zdÄ›nĂ˝  komĂ­n - osazen AL  ohebnou vloĹľkou o prĹŻmÄ›ru 130mm. SpotĹ™ebiÄŤ plyn. PET  na zemnĂ­ plyn o vĂ˝konu 24kW  v provedenĂ­ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,5m - osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 9m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  koupelna2n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 2n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(486,284,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝ - zdÄ›nĂ˝komĂ­n -osazen AC H400 vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu1,2mâ€“osazen1x kolenem90stupnĹŻ â€“kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  7m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba  1n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(487,285,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu1,2mosazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  5m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 2n.p.  ','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(488,286,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­  samostatnĂˇspalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100x60mm. KouĹ™ovod s funkcĂ­ komĂ­na â€“ rourouAL.SpotĹ™ebiÄŤ -plyn.PetBaxi-24Kw  typu C.Napojen  kouĹ™ovodem o svÄ›tlosti 100x60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 1x kolenem 90 stupĹĹŻ s kontrolnĂ­m otvorem.ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  3n.p chodba.Kontrolu spalinovĂ© cesty lze provĂ©st z ĂşstĂ­ komĂ­na+ kontrolnĂ­m otvorem na kouĹ™ovodu.                ','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(489,291,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena PP  kouĹ™ovodem 80mm - napojen na zdÄ›nĂ˝  komĂ­n, osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm  - koaxiĂˇlnÄ› osazena PP ohebnou vloĹľkou dn 75mm . SpotĹ™ebiÄŤ plyn. PET Baxi - 24kW v provedenĂ­  C -napojen kouĹ™ovodem PP. DĂ©lka kouĹ™ovodu 1,8m osazen 1x kolenem 90 stupĹĹŻ a 1x 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 13,5m- neĂşÄŤinnĂˇ  0,0m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba2n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 2n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(490,292,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇcesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,8m osazen 2x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 11,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“chodba2n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 2n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(491,293,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 130mm - napojen na zdÄ›nĂ˝ komĂ­n , osazen AL ohebnou vloĹľkou o prĹŻmÄ›ru 125mm. SpotĹ™ebiÄŤ plyn. PETThermona- 24kW v provedenĂ­  B - napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 2m osazen 1x kolenem 90 stupĹĹŻ a 1x 45 stupĹĹŻ .ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty 8,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  koupelna  3n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(492,294,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇcesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 2m osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 8,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“koupelna3n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(493,295,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n, osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 20kW v provedenĂ­  B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 1,2m -  osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 5,3m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  koupelna4n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 4n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(494,296,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇcesta P1, kterĂˇ je tvoĹ™enaAL  kouĹ™ovodem 80mm - napojen na zdÄ›nĂ˝  komĂ­n, osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm  - koaxiĂˇlnÄ› osazena AK  ohebnou vloĹľkou dn 80mm â€“ provedenĂ­ pĹ™etlak. SpotĹ™ebiÄŤplyn. PET Baxi- 24kW v provedenĂ­  C -napojen kouĹ™ovodem AL .DĂ©lkakouĹ™ovodu 1,8m osazen 2x kolenem 90 stupĹĹŻ a 1x 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 4,5m- neĂşÄŤinnĂˇ  0,0m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 4n.p.KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 4n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(495,298,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 20kW v provedenĂ­ B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 0,8m osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 4,3m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“5n.p.KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 5n.p.KomĂ­nv ĂşstĂ­ osazen  3m nĂˇstavcem. ','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(496,313,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta P1, kterĂˇ je tvoĹ™ena AL koaxiĂˇlnĂ­m kouĹ™ovodem  kouĹ™ovodem  â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti 100/60mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­  B- napojen koaxiĂˇlnĂ­m  kouĹ™ovodem AL +AL -100/60mm. DĂ©lka kouĹ™ovodu 2,5m â€“ osazen  2x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝.  ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 3m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  restaurace 1 n.p .   ','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(497,314,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti  80mm. SpotĹ™ebiÄŤ PETâ€“Baxi  - 24kW v provedenĂ­  C -napojen kouĹ™ovodem AL 80mm. DĂ©lka kouĹ™ovodu10mâ€“osazen2x kolenem 90stupĹĹŻ- kouĹ™ovodrozebĂ­ratelnĂ˝ .ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ salon  2n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(498,315,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena ALkoaxiĂˇlnĂ­m kouĹ™ovodem â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti 100/60mm. SpotĹ™ebiÄŤ PETâ€“Baxi  - 24kW v provedenĂ­- B-napojenkoaxiĂˇlnĂ­m  kouĹ™ovodem AL+AL -100/60mm. DĂ©lka kouĹ™ovodu2mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovodrozebĂ­ratelnĂ˝ .ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty 2m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ koupelna  3n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(499,316,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena ALkoaxiĂˇlnĂ­m kouĹ™ovodem â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti 100/60mm. SpotĹ™ebiÄŤ PETBaxi  - 24kW v provedenĂ­ B-napojenkoaxiĂˇlnĂ­m  kouĹ™ovodem AL+AL -100/60mm. DĂ©lka kouĹ™ovodu2mosazenna pĹ™Ă­mo - kouĹ™ovod rozebĂ­ratelnĂ˝ .ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty 2m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ koupelna  3n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(500,323,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90 stupĹĹŻ â€“ kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  9m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ kuchyĹ 2n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(501,324,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  12m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 1n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(502,325,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena ALkouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝ - zdÄ›nĂ˝komĂ­n -osazen AC H400dnvloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.UÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  9mâ€“ neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ kuchyĹ 2n.p. DigestoĹ™ provedena ve vnitĹ™nĂ­m reĹľimu filtrace.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(503,326,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena ALkouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝ - zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤPETâ€“Baxi24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.UÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  9m-neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 2n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(504,327,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90 stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 3n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  6m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 3n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(505,328,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena ALkouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝ - zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­ B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 3n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  9m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ kuchyĹ 3n.p. DigestoĹ™ provedena ve vnitĹ™nĂ­m reĹľimu filtrace.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(506,319,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90 stupĹĹŻ â€“ kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  9m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ kuchyĹ 2n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(507,320,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.UÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  6m-neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ kuchyĹ 2n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(508,290,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n - osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 1,8m osazen 1x kolenem 90 stupĹĹŻ a 1x 60 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 13,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba1n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(509,301,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­ B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 15,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba 1n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','OK','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(510,302,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇcesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­  B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 15,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“chodba1n.p . KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(511,303,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena ALkouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen  ALohebnou vloĹľkou o prĹŻmÄ›ru 125mm. SpotĹ™ebiÄŤ plyn. POV Mora 371+topidlo- 20kW v provedenĂ­- B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 1,7m -  osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 12,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“koupelna2n.p','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO');
INSERT INTO `skontroly_uk` VALUES (512,304,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena ALkouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen  AL ohebnou vloĹľkou o prĹŻmÄ›ru 125mm. SpotĹ™ebiÄŤ plyn. POV Mora35 - 35kW v provedenĂ­ â€“ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,3m -  osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 12,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“koupelna2n.p','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(513,305,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­  B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba3n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(514,306,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝ komĂ­n osa AKohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­ B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba3n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(515,307,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇcesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­  B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 1x kolenem 90 stupĹĹŻ a 1x30 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba3n.p.  KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(516,309,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇcesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem  80mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm â€“ koaxiĂˇlnÄ› osazena AK nerez pĹ™etlak dn 80mm . SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­ C -napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 2m - osazen 2x kolenem 90 stupĹĹŻ a 1x30 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 4m- neĂşÄŤinnĂˇ  0,0m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“4n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 4n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(517,308,6,0,'2019-12-06',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇcesta N1, kterĂˇ je tvoĹ™ena AC kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝ komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET  BAXI v provedenĂ­ B-napojen kouĹ™ovodem AC. DĂ©lka kouĹ™ovodu 2m - osazen 2x kolenem 90 stupĹĹŻ a 1x30 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 4m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“4n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 4n.p.','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(519,380,4,0,'2020-03-30',0,'',16,'KondenzaÄŤnĂ­ kotel Baxi Prime 24','','','Baxi Prime 24 - kondenzaÄŤnĂ­ kotel\r\nrozvod od uzĂˇvÄ›ru plynomÄ›ru aĹľ po plynovĂˇ zaĹ™izenĂ­\r\nVĂ˝chozĂ­ revize, zprovoznÄ›nĂ­ kondenzaÄŤnĂ­ho kotle Baxi Prime 24\r\n\r\nvĹˇe ok','VĂ˝chozĂ­ revize a instalace a zprovoznÄ›nĂ­ kondenzaÄŤnĂ­ho kotle Baxi Prime 24\r\nvĹˇe ok','pan SkĂˇla','','?','ANO',NULL,'','ANO'),(520,331,6,0,'2019-12-06',1,NULL,6,NULL,NULL,NULL,'SamostatnĂˇ   spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena  AL  kouĹ™ovodem 130mm - napojen na zdÄ›nĂ˝  komĂ­n - osazen AL  ohebnou  vloĹľkou o prĹŻmÄ›ru 130mm. SpotĹ™ebiÄŤ plyn. PET  Therm  o vĂ˝konu 24kW  v provedenĂ­ B - napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,3m - osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 15,5m- neĂşÄŤinnĂˇ  0,3m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  kancelĂˇĹ™  1n.p KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.                                                ','ok','pan AbrahĂˇm','','','ANO',NULL,'','ANO'),(521,365,5,0,'2020-08-17',0,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry',0,'','','','V chodbÄ› u plyn. hodin je cĂ­tit plyn je potĹ™eba to pĹ™etÄ›snit.','V chodbÄ› u plyn. pravĂ˝ch dolnĂ­ch hodin je cĂ­tit plyn je potĹ™eba to pĹ™etÄ›snit. Dne 18.08.2020 byla provedena oprava pĹ™etÄ›snÄ›nĂ­ potrubĂ­ a kontrola naĹˇĂ­m mÄ›Ĺ™Ă­cĂ­m zaĹ™Ă­zenĂ­m na Ăşnik plynu. ','Markovi','','','ANO',NULL,'','ANO'),(522,291,5,0,'2020-08-05',0,'BAXI Prime 24 kondenzaÄŤnĂ­ kotel',0,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','Byla provedena vĂ˝mÄ›na ĹˇroubenĂ­ pod kotlem, kontrola Ăşniku plynu a CO naĹˇĂ­m detekÄŤnĂ­m a mÄ›Ĺ™Ă­cĂ­m pĹ™Ă­strojem.\r\n\r\nvĹˇe ok','Markovi','','','ANO',NULL,'','ANO'),(525,290,5,0,'2020-10-01',0,'BAXI Ecofour 24',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','Provedena vĂ˝mÄ›na poĹˇkozenĂ© zĂˇkladnĂ­ Ĺ™Ă­dĂ­cĂ­ desky na kotly BAXI Ecofour 24','pan SkĂˇla','','4 842','ANO','2021-03-02','zaplaceno na ĂşÄŤet KB pana SkĂˇly (viz ĂşÄŤetnictvĂ­)','ANO'),(549,375,4,0,'2019-06-12',0,'Protherm Panther Condens 30KKO',1,'','','','Protherm Panther Condens 30KKO \r\nKondezaÄŤnĂ­ kotel ','UvedenĂ­ do provozu pan KameĹˇ ÄŚejkov Humpolec','','','','ANO',NULL,'','ANO'),(550,375,1,0,'2020-10-21',0,'Protherm Panther Condens 30KKO',2,'','','','Protherm Panther Condens 30KKO \r\nKondezaÄŤnĂ­ kotel','Byla provedena Kontrola ÄŤ. 1\r\nNemÄ›l jsem servisnĂ­ knĂ­Ĺľku, tak jsme se dohodli, Ĺľe pana KameĹˇe navĹˇtĂ­vĂ­m a on mÄ› \r\nprovedenĂ˝ servis zapĂ­Ĺˇe do knihy, \r\nPan KameĹˇ provedl zĂˇpis o provedenĂ©m servisu do knihy\r\nvĹˇe ok','','','','ANO',NULL,'','ANO'),(558,367,12,0,'2020-09-30',3,'Doklad o kontrole a ĂşdrĹľbÄ› hasĂ­cĂ­ch pĹ™Ă­strojĹŻ',12,NULL,NULL,NULL,'HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','Ok','','','','ANO',NULL,'','ANO'),(559,366,12,0,'2020-09-30',3,'Doklad o kontrole a ĂşdrĹľbÄ› hasĂ­cĂ­ch pĹ™Ă­strojĹŻ',12,NULL,NULL,NULL,'HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','Ok','','','','ANO',NULL,'','ANO'),(561,320,9,0,'2019-08-09',2,'ZprĂˇva o vĂ˝chozĂ­ revizi elektrickĂ©ho zaĹ™Ă­zenĂ­',9,NULL,NULL,NULL,'BytovĂˇ elektroinstalace','ok','','','','ANO',NULL,'','ANO'),(563,359,5,0,'2020-11-16',0,'PlynomÄ›r',0,'rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','','','PlynomÄ›r, rozvod od uzĂˇvÄ›ru plynu aĹľ po plynomÄ›ry','VĂ˝mÄ›na plynomÄ›ru','','','','ANO',NULL,'','ANO'),(565,307,2,0,'2019-10-15',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','VĹˇe v poĹ™Ăˇdku. NĂˇjemnĂ­ci si sundali poĹľĂˇrnĂ­ hlĂˇsiÄŤ. ','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(566,296,2,0,'2019-10-14',0,'BAXI Mainfour 24 F - turbo kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Mainfour 24 F - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','vĹˇe ok','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(567,315,2,0,'2019-10-17',0,'Baxi Main 24Fi - turbo kotel',3,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','Baxi Main 24Fi - turbo kotel\r\nplynovĂ˝ sporĂˇk\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','vĹˇe ok','pan SkĂˇla','600','','ANO',NULL,'','ANO'),(568,286,2,0,'2019-10-17',0,'BAXI Ecofour 24F - turbo kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','BAXI Ecofour 24F - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ                                                                                               ','ĹˇpatnĂˇ hadice jinak ok','pan SkĂˇla','','600','ANO',NULL,'','ANO'),(570,331,2,0,'2021-02-15',0,'THERM 23LXI - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','THERM 23LXI - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ','vĹˇe ok','pan SkĂˇla','700 ','','ANO',NULL,'','ANO'),(571,290,2,0,'2021-02-15',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 \r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','ChybĂ­ hlĂˇsiÄŤe - CO + kouĹ™ovĂ˝.\r\nVĹˇe ostatnĂ­ ok.','pan SkĂˇla','700','','ANO',NULL,'','NE'),(572,291,3,0,'2021-02-15',0,'BAXI Prime 24 - kondenzaÄŤnĂ­ kotel',1,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','BAXI Prime 24 - kondenzaÄŤnĂ­ kotel\r\nplynovĂ˝ sporĂˇk\r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','- vymÄ›nit hadici ke sporĂˇku\r\n- jinak ostatnĂ­ vĹˇe ok\r\n','pan SkĂˇla','700','400','ANO','2021-02-15','placeno hotovÄ› nĂˇjemnĂ­k i maji','NE'),(573,292,2,0,'2021-02-15',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ','vĹˇe ok','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(574,293,2,0,'2021-02-15',0,'THERM 12S - atmosfĂ©rickĂ˝ kotel',3,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','THERM 12S - atmosfĂ©rickĂ˝ kotel\r\nplynovĂ˝ sporĂˇk\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','ZĹ™ejmÄ› zde takĂ© (jako u pana Liperta) vymÄ›nit hadici u plynovĂ©ho sporĂˇku. U pana Liperta (byt ÄŤ.3) se dÄ›lala\r\ni revize, ale zde u pana Lycheva se dÄ›lala pouze kontrola 2 (servis 2), proto prohlĂ­dka sporĂˇku zde neprobÄ›hla,\r\nbude aĹľ pĹ™Ă­ĹˇtĂ­ rok pĹ™i revizi.  ','pan SkĂˇla','700','','ANO',NULL,'','NE'),(575,294,2,0,'2021-02-16',0,'BAXI Main 24i - turbo kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Main 24i - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','VĹˇe ok.','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(576,295,2,0,'2021-02-16',0,'BAXI Main 24i - turbo kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Main 24i - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','VĹˇe ok.','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(577,296,3,0,'2021-02-17',0,'BAXI Mainfour 24 F - turbo kotel',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Mainfour 24 F - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','HlĂˇsiÄŤe majĂ­ vlastnĂ­.\r\nVĹˇe ok.','pan SkĂˇla','700','400','ANO','2021-02-17','placeno-majitel i nĂˇjemnĂ­k','ANO'),(578,298,2,0,'2021-02-16',0,'BAXI Main 24i - turbo kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Main 24i - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','ChybĂ­ oba hlĂˇsiÄŤe - CO + kouĹ™ovĂ˝.\r\nProbÄ›hla vĂ˝mÄ›na hadice ke kotli.\r\nOstatnĂ­ vĹˇe ok.','pan SkĂˇla','700','','ANO',NULL,'','NE'),(579,301,2,0,'2021-02-16',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','VĹˇe ok.','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(580,302,2,0,'2021-02-17',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe\r\n','VĹˇe ok.','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(581,303,2,0,'2021-02-17',0,'3x PT Gamaty 461',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','2x PT Gamaty 461\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','vĹˇe ok','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(582,304,2,0,'2021-02-17',0,'1x PT Gamat 461',3,'','','','1x PT Gamat 461\r\n1x PT MORATHERM','vĹˇe ok','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(583,305,2,0,'2021-02-17',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','ChybĂ­ hlĂˇsiÄŤ CO hlĂˇsiÄŤ.\r\nJinak vĹˇe ok.','pan SkĂˇla','700','','ANO',NULL,'','NE'),(584,306,2,0,'2021-02-18',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','- chybĂ­ CO hlĂˇsiÄŤ\r\nJinak vĹˇe ok.','pan SkĂˇla','700','','ANO',NULL,'','NE'),(585,307,3,0,'2021-02-18',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','ChybĂ­ CO hlĂˇsiÄŤ.\r\nJinak vĹˇe ok.','pan SkĂˇla','1100','','ANO',NULL,'','NE'),(586,308,2,0,'2021-02-18',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','ChybĂ­ CO hlĂˇsiÄŤ.\r\nJinak vĹˇe ok.','pan SkĂˇla','700','','ANO',NULL,'','NE'),(587,309,2,0,'2021-02-18',0,'BAXI Ecofour 24 F - turbo kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 F - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','ChybĂ­ poĹľĂˇrnĂ­ (kouĹ™ovĂ˝) hlĂˇsiÄŤ.\r\nJinak vĹˇe ok.','pan SkĂˇla','700','','ANO',NULL,'','NE'),(588,313,16,0,'2021-02-19',0,'kotel - nutno upĹ™esnit',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','Servis ani revize nebyly provedeny, protoĹľe se hned pĹ™iĹˇlo na chybu nĂˇjemce: \r\n- kotel byl zcela vypnutĂ˝ (ani netemperoval), a tĂ­m mu v mrazech praskl vĂ˝mÄ›nĂ­k\r\n  (cena vĂ˝mÄ›nĂ­ku cca 4500 KÄŤ bez DPH) a to se nevĂ­, jestli nenĂ­ poĹˇkozenĂ­ i za vĂ˝mÄ›nĂ­kem.\r\n- servis a revize budou provedeny aĹľ se nĂˇjemce rozhodne na vlastnĂ­ nĂˇklady kotel opravit\r\n- dĂˇle bude potĹ™eba vymÄ›nit hadice u kotle i u sporĂˇku (jak dlouhĂ©?)\r\n','pan SkĂˇla','','','ANO',NULL,'','NE'),(589,314,2,0,'2021-02-19',0,'PK BAXI Nuvola 240Fi - turbo kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','PK BAXI Nuvola 240Fi - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','VĹˇe ok.','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(590,315,3,0,'2021-02-19',0,'Baxi Main 24Fi - turbo kotel',1,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','Baxi Main 24Fi - turbo kotel\r\nplynovĂ˝ sporĂˇk\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','ChybĂ­ kouĹ™ovĂ˝ hlĂˇsiÄŤ.\r\nJinak vĹˇe ok.','pan SkĂˇla','1 100','','ANO',NULL,'','NE'),(591,316,1,0,'2021-02-19',0,'BAXI Main 24i - turbo kotel',2,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','BAXI Main 24i - turbo kotel\r\nplynovĂ˝ sporĂˇk\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','ChybĂ­ kouĹ™ovĂ˝ hlĂˇsiÄŤ.\r\nJinak vĹˇe ok.','pan SkĂˇla','700','','ANO',NULL,'','NE'),(592,323,2,0,'2021-02-22',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','- ChybĂ­ CO hlĂˇsiÄŤ.\r\n\r\n\r\n- KouĹ™ovĂ˝ hlĂˇsiÄŤ nepouĹľĂ­vĂˇ, protoĹľe jĂ­ prĂ˝ stĂˇle houkĂˇ, jen co zaÄŤne vaĹ™it.\r\n- Byla zde provedena vĂ˝mÄ›na pojiĹˇĹĄovacĂ­ho ventilu (zaplatil nĂˇjemce).','pan SkĂˇla','700','','ANO',NULL,'','NE'),(593,324,2,0,'2021-02-22',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','ChybĂ­ CO hlĂˇsiÄŤ.\r\n\r\nOstatnĂ­ vĹˇe ok.\r\n\r\n','pan SkĂˇla','700','','ANO','2021-02-22','nĂˇjemce sleÄŤna Ĺ˝ĂˇrovĂˇ','NE'),(594,325,2,0,'2021-02-22',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','ChybĂ­ CO hlĂˇsiÄŤ.\r\nOstatnĂ­ vĹˇe ok.\r\n','pan SkĂˇla','','700','ANO','2021-02-22','poslĂˇno na ĂşÄŤet p. SkĂˇly','ANO'),(595,326,2,0,'2021-02-22',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','ChybĂ­ CO hlĂˇsiÄŤ.\r\n\r\nJinak vĹˇe ok.','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(596,327,2,0,'2021-02-23',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','ChybĂ­ CO hlĂˇsiÄŤ.\r\nPĹ™edÄ›lat digestoĹ™ na vnitĹ™nĂ­ okruh.\r\n\r\nOstatnĂ­ vĹˇe ok.\r\n\r\nKouĹ™ovĂ˝ hlĂˇsiÄŤ nepouĹľĂ­vajĂ­, protoĹľe houkĂˇ, pĹ™estoĹľe nic nevaĹ™Ă­ a je vypnutĂ˝ kotel.\r\n','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(597,328,2,0,'2021-02-23',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','ChybĂ­ CO hlĂˇsiÄŤ.\r\n\r\nOstatnĂ­ vĹˇe ok.','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(598,319,2,0,'2021-02-23',0,'BAXI ECO 3 Compact 240i - turbo kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI ECO 3 Compact 240i - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','- ChybĂ­ oba hlĂˇsiÄŤe.\r\n- PĹ™edÄ›lat digestoĹ™ na vnitĹ™nĂ­ okruh.\r\n\r\nOstatnĂ­ vĹˇe ok.','pan SkĂˇla','700','','ANO',NULL,'','NE'),(599,320,3,0,'2021-02-23',0,'BAXI ECO 3 Compact 240i - turbo kotel',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI ECO 3 Compact 240i - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','ChybĂ­ oba hlĂˇsiÄŤe.\r\nJinak vĹˇe ok.\r\n\r\nNefunguje digestoĹ™ - udÄ›lat digestoĹ™ na vnitĹ™nĂ­ okruh. \r\n','pan SkĂˇla','700','','ANO',NULL,'','NE'),(600,272,2,36,'2021-02-24',0,'BAXI ECOFOUR 240F - turbo kotel',3,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','BAXI ECOFOUR 240F - turbo kotel\r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe                                                                                              ','vĹˇe ok ok','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(601,276,2,0,'2021-02-24',0,'VIADRUS G25 - atmosfĂ©rickĂ˝ kotel, plyn kamna',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','plynovĂˇ kamna','','VIADRUS G25 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ\r\nplynovĂˇ kamna                              ','vĹˇe ok','pan SkĂˇla','700','','ANO','2021-02-24','','ANO'),(602,279,2,0,'2021-02-24',0,'THERM 12 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','','','THERM 12 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ','vĹˇe ok','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(603,332,2,0,'2021-02-24',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','vĹˇe ok','pan SkĂˇla','700','','ANO','2021-03-05','','ANO'),(604,284,2,0,'2021-02-25',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','VĹˇe ok.','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(605,285,2,0,'2021-03-25',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ','VĹˇe ok.','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(606,286,3,0,'2021-02-25',0,'BAXI Ecofour 24F - turbo kotel',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','BAXI Ecofour 24F - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ                                                                                               ','VĹˇe ok.','pan SkĂˇla','1100','','ANO',NULL,'','ANO'),(607,378,1,0,'2021-02-25',0,'BAXI prime 24 - kondenzaÄŤnĂ­ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','Prime 24 - kondenzaÄŤnĂ­ kotel\r\nRozvody plynu od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ.','VĹˇe ok.','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(608,262,2,0,'2021-02-26',0,'BAXI Â Eco 240i',3,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI Â Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','DobrĂ˝ den, posĂ­lĂˇm foto poĹˇkozenĂ©ho kotle, kterĂ˝ bude nutnĂ© v co nejbliĹľĹˇĂ­m \r\ntermĂ­nu vymÄ›nit. Na foto jsou vidÄ›t jiĹľ prohoĹ™elĂˇ mĂ­sta.\r\n\r\nDalĹˇĂ­ vĂ˝sledek kontroly musĂ­ doplnit pan SkĂˇla,','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(609,263,3,0,'2021-02-26',0,'BAXI  Eco 240i',1,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','Byla tĹ™eba udÄ›lat revize, jelikoĹľ jeĹˇtÄ› nabyla provedena\r\npan doktor vĹľdy Ĺ™Ă­kal, Ĺľe si kontrolu udÄ›lĂˇ sĂˇm, ale nikdy jsme nedostali potvrzenĂ­ o kontrole, proto\r\nvĹˇe jiĹľ budeme organizovat kontroly a revize sami. \r\n\r\nvymÄ›nit hadici u PK','pan SkĂˇla','1100','','ANO',NULL,'','NE'),(610,266,2,0,'2021-02-26',0,'BAXI  Ecofour 24',3,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Ecofour 24\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','vĹˇe ok','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(611,265,2,0,'2021-02-26',0,'BAXI ECOFOUR 240F',3,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI ECOFOUR 240F\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','vĹˇe ok','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(612,264,2,0,'2021-02-26',0,'BAXI  Eco 240i',3,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','plynovĂ˝ sporĂˇk','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ\r\nplynovĂ˝ sporĂˇk','vĹˇe ok','pan SkĂˇla','700','','ANO',NULL,'','ANO'),(613,314,5,0,'2019-10-30',0,'PK BAXI Nuvola 240Fi - turbo kotel',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','PK BAXI Nuvola 240Fi - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','vĂ˝mÄ›na trojcestnĂ©ho ventilu\r\n-prosĂ­m o vystavenĂ­ 2 faktur: a/na majitele(2190), b/na p.HrabĂˇkovou(2190),tel.603174705','pan SkĂˇla','2190','2190','ANO',NULL,'','ANO'),(614,371,5,0,'2021-03-08',0,'TepelnĂ© ÄŤerpadlo',0,'pĹ™Ă­pojka plynu od hodin aĹľ ke spotĹ™ebiÄŤi','','','pĹ™Ă­pojka plynu od hodin aĹľ ke spotĹ™ebiÄŤi                                                             ','provedenĂˇ tlakovĂˇ zkouĹˇka potrubĂ­ od hodin aĹľ ke spotĹ™ebiÄŤi  Ok','pan JiĹ™Ă­ Vrba','0','0','ANO',NULL,'','ANO'),(615,371,1,0,'2021-02-23',0,'TepelnĂ© ÄŤerpadlo',2,'pĹ™Ă­pojka plynu od hodin aĹľ ke spotĹ™ebiÄŤi','','','TepelnĂ© ÄŤerpadlo                                                              ','Vyhovuje ok','Markovi','','','ANO',NULL,'','ANO'),(616,284,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400 vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu1,2mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  7m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba  1n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(617,285,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu1,2mosazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  5m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 2n.p.  ','','p. AbrahĂˇm','ano','','ANO',NULL,'','ANO'),(618,286,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­  samostatnĂˇspalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100x60mm. KouĹ™ovod s funkcĂ­ komĂ­na â€“ rourouAL.SpotĹ™ebiÄŤ -plyn.PetBaxi-24Kw  typu C.Napojen  kouĹ™ovodem o svÄ›tlosti 100x60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 1x kolenem 90 stupĹĹŻ s kontrolnĂ­m otvorem.ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  3n.p chodba.Kontrolu spalinovĂ© cesty lze provĂ©st z ĂşstĂ­ komĂ­na+ kontrolnĂ­m otvorem na kouĹ™ovodu.                                                                                                ','','p. AbrahĂˇm','ano','','ANO',NULL,'','ANO'),(620,276,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AL  H400  vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Viadrus   28 kW  v provedenĂ­ B- napojen kouĹ™ovodem AL -130mm. DĂ©lka kouĹ™ovodu 1,5m â€“osazen  1x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v suterĂ©nu .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  16m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  techn. mĂ­stnost - suterĂ©n .                                 ','','','','','ANO',NULL,'','ANO'),(621,272,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta P1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ kouĹ™ovod  AL pevnĂˇ roura o svÄ›tlosti  80mm. SpotĹ™ebiÄŤ PET â€“ Baxi  - 24 kW  v provedenĂ­  C - napojen  kouĹ™ovodem AL  80mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝+ kontrolnĂ­ otvor  . KomĂ­novĂˇ  konstrukce zdÄ›nĂˇ osazena nerez ohebnou hadicĂ­ v provedenĂ­ pĹ™etlak 2x0,12mm .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 12m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  prĂˇdelna 1n.p.                                                                                                   ','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(622,279,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AL  H400 vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Therm na zemnĂ­ plyn    24 kW  v provedenĂ­- B- napojen kouĹ™ovodem AL -130mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  2x kolenem  90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝. KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p .ĂšÄŤinnĂˇ   vĂ˝Ĺˇka spalinovĂ© cesty  14m- neĂşÄŤinnĂˇ - 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  techn. mĂ­stnost 1n.p .','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(623,332,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇcesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 130mm - napojen na zdÄ›nĂ˝  komĂ­n - osazen AL  ohebnou vloĹľkou o prĹŻmÄ›ru 130mm. SpotĹ™ebiÄŤ plyn. PET  na zemnĂ­ plyn o vĂ˝konu 24kW  v provedenĂ­ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,5m - osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 9m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  koupelna2n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 2n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(624,331,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ   spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena  AL  kouĹ™ovodem 130mm - napojen na zdÄ›nĂ˝  komĂ­n - osazen AL  ohebnou  vloĹľkou o prĹŻmÄ›ru 130mm. SpotĹ™ebiÄŤ plyn. PET  Therm  o vĂ˝konu 24kW  v provedenĂ­ B - napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,3m - osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 15,5m- neĂşÄŤinnĂˇ  0,3m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  kancelĂˇĹ™  1n.p KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(625,290,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 1,8m osazen 1x kolenem 90 stupĹĹŻ a 1x 60 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 13,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba1n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(627,292,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,8m osazen 2x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 11,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba2n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 2n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(628,293,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 130mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AL ohebnou vloĹľkou o prĹŻmÄ›ru 125mm. SpotĹ™ebiÄŤ plyn. PETThermona- 24kW v provedenĂ­  Bnapojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 2m osazen 1x kolenem 90 stupĹĹŻ a 1x 45 stupĹĹŻ .ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 8,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  koupelna  3n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(629,294,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇcesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 2m osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 8,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“koupelna3n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(630,295,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n, osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 20kW v provedenĂ­  B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 1,2m -  osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 5,3m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  koupelna4n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 4n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(631,296,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇcesta P1, kterĂˇ je tvoĹ™enaAL  kouĹ™ovodem 80mm - napojen na zdÄ›nĂ˝  komĂ­n, osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm  - koaxiĂˇlnÄ› osazena AK  ohebnou vloĹľkou dn 80mm â€“ provedenĂ­ pĹ™etlak. SpotĹ™ebiÄŤplyn. PET Baxi- 24kW v provedenĂ­  C -napojen kouĹ™ovodem AL .DĂ©lkakouĹ™ovodu 1,8m osazen 2x kolenem 90 stupĹĹŻ a 1x 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 4,5m- neĂşÄŤinnĂˇ  0,0m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 4n.p.KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 4n.p.','','','','','NE',NULL,'','ANO'),(632,298,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 20kW v provedenĂ­ B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 0,8m osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 4,3m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“5n.p.KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 5n.p.KomĂ­nv ĂşstĂ­ osazen  3m nĂˇstavcem. ','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(634,314,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti  80mm. SpotĹ™ebiÄŤ PETâ€“Baxi  - 24kW v provedenĂ­  C -napojen kouĹ™ovodem AL 80mm. DĂ©lka kouĹ™ovodu10mâ€“osazen2x kolenem 90stupĹĹŻ- kouĹ™ovodrozebĂ­ratelnĂ˝ .ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ salon  2n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(635,315,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena ALkoaxiĂˇlnĂ­m kouĹ™ovodem â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti 100/60mm. SpotĹ™ebiÄŤ PETâ€“Baxi  - 24kW v provedenĂ­- B-napojenkoaxiĂˇlnĂ­m  kouĹ™ovodem AL+AL -100/60mm. DĂ©lka kouĹ™ovodu2mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovodrozebĂ­ratelnĂ˝ .ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty 2m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ koupelna  3n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(636,316,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena ALkoaxiĂˇlnĂ­m kouĹ™ovodem â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti 100/60mm. SpotĹ™ebiÄŤ PETBaxi  - 24kW v provedenĂ­ B-napojenkoaxiĂˇlnĂ­m  kouĹ™ovodem AL+AL -100/60mm. DĂ©lka kouĹ™ovodu2mosazenna pĹ™Ă­mo - kouĹ™ovod rozebĂ­ratelnĂ˝ .ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty 2m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ koupelna  3n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(637,319,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90 stupĹĹŻ â€“ kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  9m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ kuchyĹ 2n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(638,320,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.UÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  6m-neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ kuchyĹ 2n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(639,323,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400 vloĹľkou   DN 120mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­ B- napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupĹĹŻ - kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  12m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba   1n.p.  ','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(640,324,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  12m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 1n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(641,325,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena ALkouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝ - zdÄ›nĂ˝komĂ­n -osazen AC H400dnvloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.UÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  9mâ€“ neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ kuchyĹ 2n.p. DigestoĹ™ provedena ve vnitĹ™nĂ­m reĹľimu filtrace.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(642,326,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena ALkouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝ - zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤPETâ€“Baxi24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.UÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  9m-neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 2n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(643,327,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90 stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 3n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  6m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 3n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(644,328,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena ALkouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝ - zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­ B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 3n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  9m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ kuchyĹ 3n.p. DigestoĹ™ provedena ve vnitĹ™nĂ­m reĹľimu filtrace.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(645,262,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - oprdinace 1n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AL ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 1 x 90 stupĹĹŻ z pevnĂ©ho hlinĂ­ku o prĹŻmÄ›ru 120 mm a dĂ©lce 0,8 m. ĂšÄŤinnĂˇ dĂ©lka 11 m-neĂşÄŤinnĂˇ 0,3 m. ','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(646,263,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - technickĂˇ mĂ­stnost 1n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AL ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 1 x 90 stupĹĹŻ z pevnĂ©ho hlinĂ­ku o prĹŻmÄ›ru 120 mm a dĂ©lce 0,6 m. ĂšÄŤinnĂˇ dĂ©lka 11 m-neĂşÄŤinnĂˇ 0,3 m. ','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(647,266,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - kuchyĹ 2n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AL ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 1 x 90 a 1x45 stupĹĹŻ z pevnĂ©ho nerezu o prĹŻmÄ›ru 120 mm a dĂ©lce 0,6 m. ĂšÄŤinnĂˇ dĂ©lka 8 m-neĂşÄŤinnĂˇ 0,3 m. ','','','','','ANO',NULL,'','ANO'),(648,265,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - chodba 2n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AC ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 1 x 90stupĹĹŻ z pevnĂ©ho nerezu o prĹŻmÄ›ru 120 mm a dĂ©lce 1,2 m. ĂšÄŤinnĂˇ dĂ©lka 8 m-neĂşÄŤinnĂˇ 0,3 m. ','','','','','ANO',NULL,'','ANO'),(649,264,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - chodba 2n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AL ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 2 x 90stupĹĹŻ z pevnĂ©ho hlinĂ­ku o prĹŻmÄ›ru 120 mm a dĂ©lce 1,2 m. ĂšÄŤinnĂˇ dĂ©lka 8 m-neĂşÄŤinnĂˇ 0,3 m. ','','','','','ANO',NULL,'','ANO'),(650,269,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem-120 mm. KouĹ™ovod osazen 1x kolenem 90 stupĹĹŻ o dĂ©lce 0,7 m. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PETBaxi-24kW Typu B. KomĂ­n zdÄ›nĂ˝ osazen AL H400 o prĹŻmÄ›ru 120mm. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 5,5 m - neĂşÄŤinnĂˇ 0,2 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe 1n.p-Hala ÄŤĂ­slo 3 - KrÄŤka.','','','','','NE',NULL,'','ANO'),(651,343,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem-120 mm. KouĹ™ovod osazen 1x kolenem 90 stupĹĹŻ o dĂ©lce 0,7 m. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PETBaxi-24kW Typu B. KomĂ­n zdÄ›nĂ˝ osazen AL H400 o prĹŻmÄ›ru 120mm. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 5,5 m - neĂşÄŤinnĂˇ 0,2 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe 1n.p-Hala ÄŤĂ­slo 1 - MarĹˇĂ­k.','','','','','NE',NULL,'','ANO'),(652,257,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­  samostatnĂˇ spalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100/60mm. KouĹ™ovod s funkcĂ­ komĂ­na veden pĹ™es stĹ™echu do venkovnĂ­ho prostoru rourou AL. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PetBaxi-24Kw  typu C. Napojen kouĹ™ovodem o svÄ›tlosti 100/60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 2x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  2n.p fa.TruhlĂˇrna.\r\n','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(653,258,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­  samostatnĂˇ spalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100/60mm. KouĹ™ovod s funkcĂ­ komĂ­na veden pĹ™es stĹ™echu do venkovnĂ­ho prostoru. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PetBaxi-24Kw  typu C. Napojen koaxiĂˇlnĂ­m kouĹ™ovodem o svÄ›tlosti 100/60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  2n.p fa. Nespo','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(654,259,6,0,'2021-03-23',1,'',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­  samostatnĂˇ spalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100/60mm. KouĹ™ovod s funkcĂ­ komĂ­na veden pĹ™es stĹ™echu do venkovnĂ­ho prostoru. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PetBaxi-24Kw  typu C. Napojen koaxiĂˇlnĂ­m kouĹ™ovodem o svÄ›tlosti 100/60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  2n.p fa. Nespo.\r\nKotel slouĹľĂ­ pro prodejnu Barev LakĹŻ','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(655,281,4,0,'2021-03-31',0,'BAXI prime 24 - kondenzaÄŤnĂ­ kotel',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','Prime 24 - kondenzaÄŤnĂ­ kotel\r\nRozvody plynu od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ.           ','ZprovoznÄ›nĂ­ novĂ©ho plyn. kotle.\r\nvĹˇe ok','pan SkĂˇla','','','ANO',NULL,'','ANO'),(656,364,12,0,'2021-04-01',3,'',12,NULL,NULL,NULL,'','Faktura za montĂˇĹľ hasĂ­cĂ­ch pĹ™Ă­strojĹŻ vÄŤetnÄ› kontroly (protokolu)','','','','NE',NULL,'','ANO'),(657,368,12,0,'2021-04-01',3,'',12,NULL,NULL,NULL,'','Faktura za montĂˇĹľ hasĂ­cĂ­ch pĹ™Ă­strojĹŻ vÄŤetnÄ› kontroly (protokolu)','','','','NE',NULL,'','ANO'),(658,369,12,0,'2021-04-01',3,'',12,NULL,NULL,NULL,'','Faktura za montĂˇĹľ hasĂ­cĂ­ch pĹ™Ă­strojĹŻ vÄŤetnÄ› kontroly (protokolu)','','','','NE',NULL,'','ANO'),(659,370,12,0,'2021-04-01',3,'',12,NULL,NULL,NULL,'','Faktura za montĂˇĹľ hasĂ­cĂ­ch pĹ™Ă­strojĹŻ vÄŤetnÄ› kontroly (protokolu)','','','','NE',NULL,'','ANO'),(660,360,12,0,'2021-04-01',3,'HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST',12,NULL,NULL,NULL,'HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','Faktura za montĂˇĹľ hasĂ­cĂ­ch pĹ™Ă­strojĹŻ vÄŤetnÄ› kontroly (protokolu)','','','','ANO',NULL,'','ANO'),(661,257,5,0,'2021-06-01',0,'BAXI NUVOLA 3 Comfort 240Fi',0,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','','DrobnĂˇ oprava pĹ™Ă­vodu vzduchu (klapka), do budoucna se doporuÄŤuje opravit \r\nkonstrukci komĂ­nu nynĂ­ je do tvaru Z. LĂ©pe je dodrĹľet pĹ™Ă­mĂ˝ smÄ›r.','pan SkĂˇla','300','','ANO','2021-06-01','','ANO'),(662,365,12,0,'2021-07-16',3,'',12,NULL,NULL,NULL,'','Faktura za montĂˇĹľ hasĂ­cĂ­ch pĹ™Ă­strojĹŻ vÄŤetnÄ› kontroly (protokolu)','','','','NE',NULL,'','NE'),(663,262,5,0,'2021-08-25',0,'BAXI Â Eco 240i',0,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI Â Eco 240i vĂ˝mÄ›na za BAXI ECOFOUR 24\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','Provedena vĂ˝mÄ›na poĹˇkozenĂ©ho kotle byl instalovĂˇn kotel BAXI ECOFOUR 24','Markovi','','','ANO','2021-08-25','','ANO'),(664,366,12,0,'2021-09-30',3,'',12,NULL,NULL,NULL,'HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST - 5 ks vÄŤetnÄ› 5 ks skĹ™Ă­nÄ›k','vĹˇe ok','Markovi','','','NE',NULL,'','NE'),(665,367,12,0,'2021-09-30',3,'',12,NULL,NULL,NULL,'HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','vĹˇe ok','','','','NE',NULL,'','NE'),(666,313,1,0,'2021-09-30',0,'BAXI nuvola 240Fi',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','vĹˇe ok','pan MatkoviÄŤ','','','ANO',NULL,'','ANO'),(668,259,5,0,'2021-10-15',0,'BAXI LUNA 1,2 Fi',0,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','VĂ˝mÄ›na vÄ›trĂˇku na kotli.','','pan SkĂˇla','','','NE',NULL,'','NE'),(669,262,5,0,'2021-11-27',0,'BAXI ECOFOUR 24',0,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI Â Eco 240i - poĹˇkozen demontovĂˇn\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ\r\n25.08.2021 vĂ˝mÄ›na kotle za BAXI ECOFOUR 24','DochĂˇzelo ke ztrĂˇtÄ› vody a tlaku v topenĂ­. Byla trochu vypuĹˇtÄ›na voda a dofouknuta \r\nexpanznĂ­ nĂˇdrĹľ na cca.1.1 baru.','Markovi','','','ANO',NULL,'','NE'),(671,276,6,0,'2022-02-18',1,'SamostatnĂˇ Â spalinovĂˇ Â cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AL  H400  vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Viadrus   28 kW  v provedenĂ­ B- napojen kouĹ™ovodem AL -130mm. DĂ©lka kouĹ™ovodu 1,5m â€“osazen  1x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v suterĂ©nu .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  16m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  techn. mĂ­stnost - suterĂ©n .                                 ','','p. AbrahĂˇm','','','NE',NULL,'','NE'),(672,324,6,0,'2022-02-18',1,'SamostatnĂˇ Â spalinovĂˇ Â cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  12m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 1n.p.','','','','','ANO',NULL,'','ANO'),(673,323,6,0,'2022-02-18',1,'SamostatnĂˇ  spalinovĂˇ  cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AC H400 vloĹľkou   DN 120mm. SpotĹ™ebiÄŤ PET â€“Baxi  - 24 kW  v provedenĂ­ B- napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupĹĹŻ - kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty  12m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba   1n.p.  ','','','','','ANO',NULL,'','ANO'),(674,325,6,0,'2022-02-18',1,'SamostatnĂˇ Â spalinovĂˇ Â cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena ALkouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝ - zdÄ›nĂ˝komĂ­n -osazen AC H400dnvloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.UÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  9mâ€“ neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ kuchyĹ 2n.p. DigestoĹ™ provedena ve vnitĹ™nĂ­m reĹľimu filtrace.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(675,326,6,0,'2022-02-18',1,'SamostatnĂˇ Â  spalinovĂˇ Â cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena ALkouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝ - zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤPETâ€“Baxi24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu 0,5mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.UÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  9m-neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 2n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(676,327,6,0,'2022-02-18',1,'SamostatnĂˇ  spalinovĂˇ  cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90 stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 3n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  6m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 3n.p.','','p. AbrahĂˇm','','','ANO',NULL,'',''),(677,328,6,0,'2022-02-18',1,'SamostatnĂˇ  spalinovĂˇ   cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena ALkouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝ - zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­ B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 3n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  9m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ kuchyĹ 3n.p. DigestoĹ™ provedena ve vnitĹ™nĂ­m reĹľimu filtrace.','','p. AbrahĂˇm','','','ANO',NULL,'',''),(678,272,6,0,'2022-02-18',1,'SamostatnĂˇ Â spalinovĂˇ Â cesta P1',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta P1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ kouĹ™ovod  AL pevnĂˇ roura o svÄ›tlosti  80mm. SpotĹ™ebiÄŤ PET â€“ Baxi  - 24 kW  v provedenĂ­  C - napojen  kouĹ™ovodem AL  80mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  1x kolenem  90stupĹĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝+ kontrolnĂ­ otvor  . KomĂ­novĂˇ  konstrukce zdÄ›nĂˇ osazena nerez ohebnou hadicĂ­ v provedenĂ­ pĹ™etlak 2x0,12mm .ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 12m- neĂşÄŤinnĂˇ- 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  prĂˇdelna 1n.p.                                                                                                   ','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(679,279,6,0,'2022-02-18',1,'SamostatnĂˇ Â spalinovĂˇ Â cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena AL  kouĹ™ovodem  â€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝   komĂ­n - osazen AL  H400 vloĹľkou   DN  120mm. SpotĹ™ebiÄŤ PET â€“Therm na zemnĂ­ plyn    24 kW  v provedenĂ­- B- napojen kouĹ™ovodem AL -130mm. DĂ©lka kouĹ™ovodu 0,5m â€“osazen  2x kolenem  90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝. KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p .ĂšÄŤinnĂˇ   vĂ˝Ĺˇka spalinovĂ© cesty  14m- neĂşÄŤinnĂˇ - 0,3 m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  techn. mĂ­stnost 1n.p .','','p. AbrahĂˇm','','','ANO',NULL,'',''),(680,332,6,0,'2022-02-18',1,'SamostatnĂˇ Â spalinovĂˇ Â cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇcesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 130mm - napojen na zdÄ›nĂ˝  komĂ­n - osazen AL  ohebnou vloĹľkou o prĹŻmÄ›ru 130mm. SpotĹ™ebiÄŤ plyn. PET  na zemnĂ­ plyn o vĂ˝konu 24kW  v provedenĂ­ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,5m - osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 9m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  koupelna2n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 2n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','NE'),(681,281,6,0,'2022-02-18',1,'KomĂ­n systĂ©movĂ˝kondenzaÄŤnĂ­ kotel-mĂ­sto gamat  ',6,NULL,NULL,NULL,'NovĂ˝ kondenzaÄŤnĂ­ kotel-vĂ˝mÄ›na mĂ­sto gamat                              ','','p. AbrahĂˇm','','','ANO',NULL,'',''),(682,284,6,0,'2022-02-18',1,'SamostatnĂˇ Â spalinovĂˇ Â cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400 vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu1,2mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 1n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  7m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba  1n.p.','','p. AbrahĂˇm','','','ANO',NULL,'',''),(683,285,6,0,'2022-02-18',1,'SamostatnĂˇ Â spalinovĂˇ Â cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu1,2mosazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  5m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ chodba 2n.p.  ','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(684,286,6,0,'2022-02-18',1,'SamostatnĂˇ Â spalinovĂˇ Â cesta P1',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­  samostatnĂˇspalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100x60mm. KouĹ™ovod s funkcĂ­ komĂ­na â€“ rourouAL.SpotĹ™ebiÄŤ -plyn.PetBaxi-24Kw  typu C.Napojen  kouĹ™ovodem o svÄ›tlosti 100x60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 1x kolenem 90 stupĹĹŻ s kontrolnĂ­m otvorem.ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  3n.p chodba.Kontrolu spalinovĂ© cesty lze provĂ©st z ĂşstĂ­ komĂ­na+ kontrolnĂ­m otvorem na kouĹ™ovodu.                                                                                                ','','p. AbrahĂˇm','','','ANO',NULL,'',''),(685,378,6,0,'2022-02-18',1,'KomĂ­n systĂ©movĂ˝-kondenzaÄŤnĂ­ kotel',6,NULL,NULL,NULL,'KomĂ­n systĂ©movĂ˝-Ricom gas Cvikov osazen Ocel/PP rourou o svÄ›tlosti DN 100/60 mm. CelkovĂˇ dĂ©lka 1,8 m. Novostavba bytovĂ© jednotky 1n.p.-nepodsklepenĂ˝, stĹ™echa valbovĂˇ. VyĂşstÄ›nĂ­ spalinovĂ© cesty - 1n.p. chodba.','','p. AbrahĂˇm','','','ANO',NULL,'',''),(686,331,6,0,'2022-02-18',1,'SamostatnĂˇ  spalinovĂˇ  cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ   spalinovĂˇ  cesta N1, kterĂˇ je tvoĹ™ena  AL  kouĹ™ovodem 130mm - napojen na zdÄ›nĂ˝  komĂ­n - osazen AL  ohebnou  vloĹľkou o prĹŻmÄ›ru 130mm. SpotĹ™ebiÄŤ plyn. PET  Therm  o vĂ˝konu 24kW  v provedenĂ­ B - napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,3m - osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ  vĂ˝Ĺˇka spalinovĂ© cesty 15,5m- neĂşÄŤinnĂˇ  0,3m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  kancelĂˇĹ™  1n.p KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','','p. AbrahĂˇm','','','ANO',NULL,'',''),(687,290,6,0,'2022-02-18',1,'SamostatnĂˇ  spalinovĂˇ cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 1,8m osazen 1x kolenem 90 stupĹĹŻ a 1x 60 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 13,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba1n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 1n.p.','','p. AbrahĂˇm','','','ANO',NULL,'','ANO'),(688,291,6,0,'2022-02-18',1,'KomĂ­n systĂ©movĂ˝-kondenzaÄŤnĂ­ kotel',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇcesta P1, kterĂˇ je tvoĹ™ena PP  kouĹ™ovodem 80mm - napojen na zdÄ›nĂ˝  komĂ­n, osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm  - koaxiĂˇlnÄ› osazena PP ohebnou vloĹľkou dn 75mm . SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­  C -napojen kouĹ™ovodem PP. DĂ©lka kouĹ™ovodu 1,8m osazen 1x kolenem 90 stupĹĹŻ a 1x 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 13,5m- neĂşÄŤinnĂˇ  0,0m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  chodba2n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 2n.p.','','p. AbrahĂˇm','','','ANO',NULL,'',''),(689,292,6,0,'2022-02-18',1,'SamostatnĂˇ spalinovĂˇ cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 0,8m osazen 2x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 11,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  chodba2n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 2n.p.','','p. AbrahĂˇm','','','ANO',NULL,'',''),(690,293,6,0,'2022-02-18',1,'SamostatnĂˇ spalinovĂˇ cesta P1',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 130mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AL ohebnou vloĹľkou o prĹŻmÄ›ru 125mm. SpotĹ™ebiÄŤ plyn. PETThermona- 24kW v provedenĂ­  Bnapojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 2m osazen 1x kolenem 90 stupĹĹŻ a 1x 45 stupĹĹŻ .ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 8,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“  koupelna  3n.pKontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','','p. AbrahĂˇm','','','ANO',NULL,'',''),(691,294,6,0,'2022-02-18',1,'SamostatnĂˇ spalinovĂˇ cesta P1',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇcesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 24kW v provedenĂ­ B-napojen kouĹ™ovodem AL. DĂ©lka kouĹ™ovodu 2m osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 8,5m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤeâ€“koupelna3n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 3n.p.','','p. AbrahĂˇm','','','ANO',NULL,'',''),(692,295,6,0,'2022-02-18',1,'SamostatnĂˇ spalinovĂˇ cesta P1',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n, osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 20kW v provedenĂ­  B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 1,2m -  osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 5,3m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“  koupelna4n.p. KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 4n.p.','','p. AbrahĂˇm','','','ANO',NULL,'',''),(694,314,6,0,'2022-02-18',1,'SamostatnĂˇ  spalinovĂˇ  cesta P1',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodem â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti  80mm. SpotĹ™ebiÄŤ PETâ€“Baxi  - 24kW v provedenĂ­  C -napojen kouĹ™ovodem AL 80mm. DĂ©lka kouĹ™ovodu10mâ€“osazen2x kolenem 90stupĹĹŻ- kouĹ™ovodrozebĂ­ratelnĂ˝ .ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty 10m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ salon  2n.p.','','p. AbrahĂˇm','','','ANO',NULL,'',''),(695,315,6,0,'2022-02-18',1,'SamostatnĂˇ spalinovĂˇ cesta P1',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena ALkoaxiĂˇlnĂ­m kouĹ™ovodem â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti 100/60mm. SpotĹ™ebiÄŤ PETâ€“Baxi  - 24kW v provedenĂ­- B-napojenkoaxiĂˇlnĂ­m  kouĹ™ovodem AL+AL -100/60mm. DĂ©lka kouĹ™ovodu2mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovodrozebĂ­ratelnĂ˝ .ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty 2m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ koupelna  3n.p.','','p. AbrahĂˇm','','','ANO',NULL,'',''),(696,316,6,0,'2022-02-18',1,'SamostatnĂˇ spalinovĂˇ cesta P1',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena ALkoaxiĂˇlnĂ­m kouĹ™ovodem â€“ kouĹ™ovod s funkcĂ­ komĂ­na o svÄ›tlosti 100/60mm. SpotĹ™ebiÄŤ PETBaxi  - 24kW v provedenĂ­ B-napojenkoaxiĂˇlnĂ­m  kouĹ™ovodem AL+AL -100/60mm. DĂ©lka kouĹ™ovodu2mosazenna pĹ™Ă­mo - kouĹ™ovod rozebĂ­ratelnĂ˝ .ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty 2m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ koupelna  3n.p.','','p. AbrahĂˇm','','','ANO',NULL,'',''),(697,319,6,0,'2022-02-18',1,'SamostatnĂˇ  spalinovĂˇ  cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90 stupĹĹŻ â€“ kouĹ™ovod rozebĂ­ratelnĂ˝.KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.ĂšÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  9m- neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ kuchyĹ 2n.p.','','p. AbrahĂˇm','','','ANO',NULL,'',''),(698,320,6,0,'2022-02-18',1,'SamostatnĂˇ Â spalinovĂˇ Â cesta N1',6,NULL,NULL,NULL,'SamostatnĂˇ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL kouĹ™ovodemâ€“ napojen na vĂ­cevrstvĂ˝  zdÄ›nĂ˝komĂ­n -osazen AC H400vloĹľkou DN120mm. SpotĹ™ebiÄŤ PETâ€“Baxi- 24kW v provedenĂ­  B-napojen kouĹ™ovodem AL -120mm. DĂ©lka kouĹ™ovodu0,5mâ€“osazen1x kolenem 90stupnĹŻ- kouĹ™ovod rozebĂ­ratelnĂ˝ .KontrolnĂ­ dvĂ­Ĺ™ka na patÄ› komĂ­na v 2n.p.UÄŤinnĂˇvĂ˝Ĺˇka spalinovĂ© cesty  6m-neĂşÄŤinnĂˇ- 0,3 m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“ kuchyĹ 2n.p.','','p. AbrahĂˇm','','','ANO',NULL,'',''),(699,262,6,0,'2022-02-18',1,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - oprdinace 1n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AL ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 1 x 90 stupĹĹŻ z pevnĂ©ho hlinĂ­ku o prĹŻmÄ›ru 120 mm a dĂ©lce 0,8 m. ĂšÄŤinnĂˇ dĂ©lka 11 m-neĂşÄŤinnĂˇ 0,3 m. ','','p. AbrahĂˇm','','','ANO',NULL,'',''),(700,263,6,0,'2022-02-18',1,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - technickĂˇ mĂ­stnost 1n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AL ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 1 x 90 stupĹĹŻ z pevnĂ©ho hlinĂ­ku o prĹŻmÄ›ru 120 mm a dĂ©lce 0,6 m. ĂšÄŤinnĂˇ dĂ©lka 11 m-neĂşÄŤinnĂˇ 0,3 m. ','','p. AbrahĂˇm','','','ANO',NULL,'',''),(701,257,6,0,'2022-02-18',1,'IndividuĂˇlnĂ­ spal cesta P1',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­  samostatnĂˇ spalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100/60mm. KouĹ™ovod s funkcĂ­ komĂ­na veden pĹ™es stĹ™echu do venkovnĂ­ho prostoru rourou AL. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PetBaxi-24Kw  typu C. Napojen kouĹ™ovodem o svÄ›tlosti 100/60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 2x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  2n.p fa.TruhlĂˇrna.\r\n','','p. AbrahĂˇm','','','ANO',NULL,'',''),(702,258,6,0,'2022-02-18',1,'IndividuĂˇlnĂ­ spal cesta P1',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­  samostatnĂˇ spalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100/60mm. KouĹ™ovod s funkcĂ­ komĂ­na veden pĹ™es stĹ™echu do venkovnĂ­ho prostoru. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PetBaxi-24Kw  typu C. Napojen koaxiĂˇlnĂ­m kouĹ™ovodem o svÄ›tlosti 100/60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  2n.p fa. Nespo','','p. AbrahĂˇm','','','ANO',NULL,'',''),(703,259,6,0,'2022-02-18',1,'IndividuĂˇlnĂ­ spal cesta P1',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­  samostatnĂˇ spalinovĂˇ  cesta P1 , kterĂˇ je tvoĹ™ena AL kouĹ™ovodem- koaxiĂˇlnĂ­m 100/60mm. KouĹ™ovod s funkcĂ­ komĂ­na veden pĹ™es stĹ™echu do venkovnĂ­ho prostoru. SpotĹ™ebiÄŤ-plyn kotel na zemnĂ­ plyn PetBaxi-24Kw  typu C. Napojen koaxiĂˇlnĂ­m kouĹ™ovodem o svÄ›tlosti 100/60mm-dĂ©lka kouĹ™ovodu 1,5m. Osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 1,8m- neĂşÄŤinnĂˇ 0m. UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe  2n.p fa. Nespo.\r\nKotel slouĹľĂ­ pro prodejnu Barev LakĹŻ','','p. AbrahĂˇm','','','ANO',NULL,'',''),(704,298,17,0,'2022-02-18',1,'SamostatnĂˇ spalinovĂˇ cesta P1',6,NULL,NULL,NULL,'SamostatnĂˇ  spalinovĂˇ cesta P1, kterĂˇ je tvoĹ™ena AK kouĹ™ovodem 120mm - napojen na zdÄ›nĂ˝  komĂ­n osazen AK ohebnou vloĹľkou o prĹŻmÄ›ru 120mm. SpotĹ™ebiÄŤ plyn. PET Baxi- 20kW v provedenĂ­ B-napojen kouĹ™ovodem AK. DĂ©lka kouĹ™ovodu 0,8m osazen 1x kolenem 90 stupĹĹŻ. ĂšÄŤinnĂˇ vĂ˝Ĺˇka spalinovĂ© cesty 4,3m- neĂşÄŤinnĂˇ  0,3m.UmĂ­stÄ›nĂ­ spotĹ™ebiÄŤe â€“5n.p.KontrolnĂ­ dvĂ­Ĺ™ka umĂ­stÄ›na na patÄ› komĂ­na v 5n.p.KomĂ­nv ĂşstĂ­ osazen  3m nĂˇstavcem. ','NĂˇjemce nebyl pĹ™Ă­tomen','','','','ANO',NULL,'',''),(705,266,17,0,'2022-02-18',1,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - kuchyĹ 2n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AL ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 1 x 90 a 1x45 stupĹĹŻ z pevnĂ©ho nerezu o prĹŻmÄ›ru 120 mm a dĂ©lce 0,6 m. ĂšÄŤinnĂˇ dĂ©lka 8 m-neĂşÄŤinnĂˇ 0,3 m. ','NĂˇjemce nebyl pĹ™Ă­tomen','','','','ANO',NULL,'',''),(706,265,17,0,'2022-02-18',1,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AC jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - chodba 2n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AC ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 1 x 90stupĹĹŻ z pevnĂ©ho nerezu o prĹŻmÄ›ru 120 mm a dĂ©lce 1,2 m. ĂšÄŤinnĂˇ dĂ©lka 8 m-neĂşÄŤinnĂˇ 0,3 m. ','NĂˇjemce nebyl pĹ™Ă­tomen','','','','ANO',NULL,'',''),(707,264,17,0,'2022-02-18',1,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1',6,NULL,NULL,NULL,'IndividuĂˇlnĂ­ spalinovĂˇ cesta N1, kterĂˇ je tvoĹ™ena AL jednovrstvĂ˝m kouĹ™ovodem. PlynovĂ˝ spotĹ™ebiÄŤ-kotel na zemnĂ­ plyn Baxi-24kW v provedenĂ­ B. UmĂ­stÄ›nĂ­ - chodba 2n.p. KomĂ­n zdÄ›nĂ˝, vĂ­cevrstvĂ­-vyvloĹľkovĂˇn AL ohebnou hadicĂ­ o prĹŻmÄ›ru 120 mm. PoÄŤet kolen 2 x 90stupĹĹŻ z pevnĂ©ho hlinĂ­ku o prĹŻmÄ›ru 120 mm a dĂ©lce 1,2 m. ĂšÄŤinnĂˇ dĂ©lka 8 m-neĂşÄŤinnĂˇ 0,3 m. ','NĂˇjemce nebyl pĹ™Ă­tomen','','','','ANO',NULL,'',''),(708,376,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(709,380,17,0,'2017-01-01',1,'',6,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(710,281,17,0,'2017-01-01',1,'',6,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(711,376,17,0,'2017-01-01',1,'',6,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(712,360,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(713,360,17,0,'2017-01-01',1,'',6,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(717,380,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(718,378,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(719,364,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(720,279,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(721,332,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(722,281,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(723,365,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(724,284,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(725,285,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(726,286,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(727,366,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(728,331,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(729,290,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(730,291,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(731,292,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(732,293,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(733,294,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(734,295,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(735,298,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(736,367,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(737,301,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(738,302,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(739,303,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(740,304,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(741,305,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(742,306,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(743,307,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(744,308,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(745,309,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(746,368,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(747,313,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(748,314,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(749,315,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(750,316,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(751,369,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(752,319,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(753,370,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(754,323,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(755,324,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(756,325,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(757,326,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(758,327,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(759,328,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(760,376,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(761,363,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(762,364,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(763,279,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(764,332,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(765,365,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(766,284,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(767,285,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(768,286,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(769,331,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(770,290,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(771,291,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(772,292,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(773,293,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(774,294,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(775,295,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(776,298,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(777,301,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(778,302,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(779,303,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(780,304,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(781,305,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(782,306,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(783,307,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(784,308,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(785,309,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(786,368,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(787,313,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(788,314,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(789,315,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(790,316,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(791,369,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(792,319,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(793,320,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(794,370,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(795,323,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(796,324,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(797,325,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(798,326,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(799,327,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(800,328,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(801,376,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(802,363,3,0,'2022-09-17',0,'rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry',1,'','','','rozvod od uzĂˇvÄ›ru plynu aĹľ po bytovĂ© plynomÄ›ry','','','','','NE',NULL,'','NE'),(803,380,16,138,'2022-09-17',0,'Baxi Prime 24 - kondenzaÄŤnĂ­ kotel',16,'rozvod od plynomÄ›ru po plyn. zaĹ™Ă­zenĂ­','','','Baxi Prime 24 - kondenzaÄŤnĂ­ kotel\r\nrozvod od uzĂˇvÄ›ru plynomÄ›ru aĹľ po plynovĂˇ zaĹ™izenĂ­','','','','','NE',NULL,'','NE'),(804,326,1,69,'2022-05-23',0,'BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel \r\nnutnĂ© odpojenĂ­ digestoĹ™e v kuchyni pro bezpeÄŤnĂ˝ provoz kotle','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(805,327,1,67,'2022-05-23',0,'BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun \r\nvzduchu pro kotel nutnĂ© odpojenĂ­ digestoĹ™e v kuchyni pro bezpeÄŤnĂ˝ provoz kotle','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(806,328,1,119,'2022-05-23',0,'BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun \r\nvzduchu pro kotel nutnĂ© odpojenĂ­ digestoĹ™e v kuchyni pro bezpeÄŤnĂ˝ provoz kotle','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(807,323,1,8,'2022-05-23',0,'BAXI Ecofour 240 i - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 240 i - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel ','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(808,324,1,175,'2022-05-23',0,'BAXI Ecofour 240 i - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 240 i - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel ','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(809,325,1,173,'2022-05-23',0,'BAXI Ecofour 240 i - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 240 i - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel ','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(810,380,1,138,'2022-05-16',0,'Baxi Prime 24 - kondenzaÄŤnĂ­ kotel',2,'rozvod od plynomÄ›ru po plyn. zaĹ™Ă­zenĂ­','','','Baxi Prime 24 - kondenzaÄŤnĂ­ kotel\r\nrozvod od uzĂˇvÄ›ru plynomÄ›ru aĹľ po plynovĂˇ zaĹ™izenĂ­','','pan PankoviÄŤ','','','ANO',NULL,'','ANO'),(811,332,1,49,'2022-05-16',0,'BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','nutnĂˇ kontrola po 6.mÄ›sĂ­cĹŻ provozu (listopad) z dĹŻvodu zneÄŤiĹˇtÄ›nĂ­ kotle','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(812,276,1,122,'2022-05-16',0,'VIADRUS G25 - atmosfĂ©rickĂ˝ kotel, plyn kamna',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','plynovĂˇ kamna','','VIADRUS G25 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ\r\nplynovĂ˝ sporĂˇk                           ','Byla provedena oprava kotle vĂ˝mÄ›na ÄŤidla','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(813,279,1,50,'2022-05-16',0,'THERM 12 - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ,','','','THERM 12 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','pan PankoviÄŤ','','','ANO',NULL,'','ANO'),(814,319,1,89,'2022-05-16',0,'BAXI ECO 3 Compact 240i - turbo kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI ECO 3 Compact 240i - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu \r\npro kotel nutnĂ© odpojenĂ­ digestoĹ™e v kuchyni pro bezpeÄŤnĂ˝ provoz kotle','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(815,320,1,116,'2022-05-16',0,'BAXI ECO 3 Compact 240i - turbo kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI ECO 3 Compact 240i - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel\r\nnutnĂ© odpojenĂ­ digestoĹ™e v kuchyni pro bezpeÄŤnĂ˝ provoz kotle','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(816,301,1,176,'2022-05-30',0,'BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','pan PankoviÄŤ','','','ANO',NULL,'','ANO'),(817,306,1,178,'2022-05-30',0,'BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel ','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(818,305,1,91,'2022-05-30',0,'BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 i atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel ','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(819,307,1,179,'2022-05-30',0,'BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel ','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(820,308,1,183,'2022-05-30',0,'BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','NutnĂˇ instalace CO hlĂˇsiÄŤe ','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(821,309,1,113,'2022-05-30',0,'BAXI Ecofour 24 fi - turbo kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 fi - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','pan PankoviÄŤ','','','ANO',NULL,'','ANO'),(822,291,1,121,'2022-05-25',0,'BAXI Prime 24 - kondenzaÄŤnĂ­ kotel',2,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','BAXI Prime 24 - kondenzaÄŤnĂ­ kotel\r\nplynovĂ˝ sporĂˇk\r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','pan PankoviÄŤ','','','ANO',NULL,'','ANO'),(823,294,1,114,'2022-05-25',0,'BAXI Main 24i - turbo kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Main 24i - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel ','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(824,331,1,147,'2022-05-25',0,'THERM 23LXI - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','THERM 23LXI - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel ','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(825,290,1,28,'2022-05-25',0,'BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 i\r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel ','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(826,292,1,80,'2022-05-25',0,'BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ','zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel ','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(827,293,1,56,'2022-05-25',0,'THERM 23 - atmosfĂ©rickĂ˝ kotel',2,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','THERM 23 - atmosfĂ©rickĂ˝ kotel\r\nplynovĂ˝ sporĂˇk\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','instalace CO hlĂˇsiÄŤe ','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(828,298,1,190,'2022-05-25',0,'BAXI Main 24i - turbo kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Main 24i - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(829,302,1,102,'2022-05-30',0,'BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 i atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe\r\n','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel ','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(830,316,1,43,'2022-05-09',0,'BAXI Main 24 fi - turbo kotel',2,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','BAXI Main 24 fi - turbo kotel\r\nplynovĂ˝ sporĂˇk\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','pan PankoviÄŤ','','','ANO',NULL,'','ANO'),(831,315,1,94,'2022-05-09',0,'Baxi Main 24 fi - turbo kotel',2,'plynovĂ˝ sporĂˇk','rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','Baxi Main 24 fi - turbo kotel\r\nplynovĂ˝ sporĂˇk\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','pan PankoviÄŤ','','','ANO',NULL,'','ANO'),(832,314,1,24,'2022-05-09',0,'PK BAXI Nuvola 240Fi - turbo kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','PK BAXI Nuvola 240Fi - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','pan PankoviÄŤ','','','ANO',NULL,'','ANO'),(833,313,1,0,'2022-05-09',0,'PK BAXI Nuvola 240Fi - turbo kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','','','pan PankoviÄŤ','','','ANO',NULL,'','ANO'),(834,378,1,192,'2022-05-10',0,'BAXI prime 24 - kondenzaÄŤnĂ­ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','Prime 24 - kondenzaÄŤnĂ­ kotel\r\nRozvody plynu od plynomÄ›ru aĹľ po spotĹ™ebiÄŤ.','','pan PankoviÄŤ','','','ANO',NULL,'','ANO'),(835,284,1,20,'2022-05-10',0,'BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel',1,'rozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','','','BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru aĹľ po spotĹ™ebiÄŤe','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel ','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(836,286,1,10,'2022-05-10',0,'BAXI Ecofour 24 Fi - turbo kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','BAXI Ecofour 24 Fi - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ                                                                                               ','Zkontrolovat komĂ­n, zda se neovlivĹuje sĂˇnĂ­ s odfukem turbo kotel','pan PankoviÄŤ','','','ANO',NULL,'','ANO'),(837,285,1,44,'2022-05-10',0,'BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','BAXI Ecofour 24 i - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel ','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(838,295,1,194,'2022-05-25',0,'BAXI Main 24i - turbo kotel',2,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','','BAXI Main 24i - turbo kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤe','zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel ','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(839,262,1,129,'2022-05-02',0,'BAXI ECOFOUR 24 i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI Â Eco 240i - poĹˇkozen demontovĂˇn\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ\r\n25.08.2021 vĂ˝mÄ›na kotle za BAXI ECOFOUR 24','NutnĂˇ instalace CO hlĂˇsiÄŤe ','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(840,264,1,126,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','plynovĂ˝ sporĂˇk','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ\r\nplynovĂ˝ sporĂˇk','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(841,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(842,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(843,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(844,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(845,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(846,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(847,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(848,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(849,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(850,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(851,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(852,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(853,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(854,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(855,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(856,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(857,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(858,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(859,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(860,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(861,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(862,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(863,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(864,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(865,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(866,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(867,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(868,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(869,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(870,263,1,128,'2022-05-02',0,'BAXI  Eco 240i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI  Eco 240i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\nNutnĂˇ vĂ˝mÄ›na kotle z dĹŻvodu stĂˇĹ™Ă­ a opotĹ™ebenĂ­ vĹˇech provoznĂ­ch a bezpeÄŤnostnĂ­ch dĂ­lĹŻ.','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(871,265,1,139,'2022-05-02',0,'BAXI ECOFOUR 240 i',2,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','','BAXI ECOFOUR 240 i\r\nrozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','NutnĂˇ instalace CO hlĂˇsiÄŤe a zhotovit otvory pro pĹ™Ă­sun vzduchu pro kotel. \r\n\r\n','pan PankoviÄŤ','','','ANO',NULL,'','NE'),(873,266,20,0,'2017-01-01',4,'',15,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(874,265,20,0,'2017-01-01',4,'',15,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(875,264,20,0,'2017-01-01',4,'',15,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(876,366,12,0,'2022-09-30',3,'SkĹ™Ă­Ĺ + HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST ',12,'','','','HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST - 5 ks vÄŤetnÄ› 5 ks skĹ™Ă­nÄ›k','servis poĹľĂˇrnĂ­ho zaĹ™Ă­zenĂ­','','','','NE',NULL,'','NE'),(877,367,12,0,'2022-09-30',3,'SkĹ™Ă­Ĺ + HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST ',12,'','','','HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST','JateÄŤnĂ­ 1836-1837 kontrola 2021.pdf','','','','NE',NULL,'','NE'),(879,365,20,0,'2017-01-01',4,'',15,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(880,366,20,0,'2017-01-01',4,'',15,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(881,367,20,0,'2017-01-01',4,'',15,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(882,368,20,0,'2017-01-01',4,'',15,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(883,369,20,0,'2017-01-01',4,'',15,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(884,370,20,0,'2017-01-01',4,'',15,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(885,376,20,0,'2017-01-01',4,'',15,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(886,359,20,0,'2017-01-01',4,'',15,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(887,257,20,0,'2017-01-01',4,'',15,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(888,258,20,0,'2017-01-01',4,'',15,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(889,259,20,0,'2017-01-01',4,'',15,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(890,344,20,0,'2017-01-01',4,'',15,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(891,361,20,0,'2017-01-01',4,'',15,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(892,292,5,80,'2017-11-01',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ','MontĂˇĹľ CO hlĂˇsiÄŤe + kouĹ™ovĂ˝ hlĂˇsiÄŤ','Markovi','','','NE',NULL,'','NE'),(893,292,5,80,'2023-01-25',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',3,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤ','','','BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel\r\nrozvod od plynomÄ›ru po spotĹ™ebiÄŤ','Provedena oprava - vĂ˝mÄ›na termostatu, NĂˇjemce zaplatil 900KÄŤ.','Markovi','900','','ANO','2023-01-25','','NE'),(895,360,0,0,'2023-01-02',4,'PENB Kategorie E',15,'','','','','','Markovi','','','NE',NULL,'','NE'),(896,360,20,0,'2017-01-01',4,'',15,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(897,360,0,0,'2023-01-02',4,'Kategorie E',15,'','','','','','Markovi','','Ano','ANO','2023-01-25','',''),(898,407,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(899,407,17,0,'2017-01-01',1,'',6,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(900,331,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(901,292,5,80,'2023-01-31',0,'BAXI ECOFOUR 24 - atmosfĂ©rickĂ˝ kotel',3,'NovĂ˝ kotel','','',NULL,'31.01.2023 VĂ˝mÄ›na kotle na typ: BAXI ECOFOUR 24, kterĂ˝ byl dĹ™Ă­ve u panĂ­\r\nĹ imanovĂ© v areĂˇlu MĂ­rova DubĂ­, vĂ˝mÄ›nu provedl pan KuiĹˇ. Stav kotle 25.08.2021 novĂ˝.','Markovi','','','NE','2023-01-31','Marek','NE'),(902,264,5,126,'2022-12-21',0,'BAXI  Eco 240i',3,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','plynovĂ˝ sporĂˇk','',NULL,'VĂ˝mÄ›na kotle za kondenzaÄŤnĂ­ Luna classic 24','pan PankoviÄŤ','','','ANO',NULL,'','ANO'),(903,263,5,128,'2022-10-04',0,'BAXI  Eco 240i',3,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','',NULL,'21.12. 2022 VĂ˝mÄ›na kotle za kondenzaÄŤnĂ­ Luna classic 24','pan PankoviÄŤ','','','NE',NULL,'',''),(904,410,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(905,410,17,0,'2017-01-01',1,'',6,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(906,408,17,0,'2017-01-01',1,'',6,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(907,409,17,0,'2017-01-01',1,'',6,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(908,359,17,0,'2017-01-01',1,'',6,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(909,410,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(910,408,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(911,409,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(912,408,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(913,409,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(914,262,2,212,'2023-08-03',0,'BAXI prime 24 - kondenzaÄŤnĂ­ kotel',3,'rozvod od podruĹľnĂ©ho plynomÄ›ru aĹľ po spotĹ™ebiÄŤ','','',NULL,'revize plynovĂ©ho zaĹ™Ă­zenĂ­','','','','NE',NULL,'','NE'),(915,328,4,119,'2023-08-15',0,'BAXI Ecofour 24 - atmosfĂ©rickĂ˝ kotel',1,'rozvod od plynomÄ›ru po spotĹ™ebiÄŤe','','',NULL,'15.08. 2023 VĂ˝mÄ›na kotle za kondenzaÄŤnĂ­ kotel Baxi Luna classic 24','','','','NE',NULL,'','NE'),(916,366,12,0,'2023-09-20',3,'SkĹ™Ă­Ĺ + HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST ',12,'','','',NULL,'Kontrola JateÄŤnĂ­ 1836 a 1837','','','','NE',NULL,'','NE'),(917,367,12,0,'2023-09-20',3,'SkĹ™Ă­Ĺ + HasĂ­cĂ­ pĹ™Ă­stroj prĂˇĹˇkovĂ˝ 6 kg - P6Real ST ',12,'','','',NULL,'Kontrola JateÄŤnĂ­ 1836-1837','','','','NE',NULL,'','NE'),(918,410,18,0,'2017-01-01',2,'',9,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(919,427,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE');
INSERT INTO `skontroly_uk` VALUES (920,428,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(921,429,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(922,430,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(923,418,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(924,419,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(925,421,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(926,422,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(927,423,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(928,424,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(929,425,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(930,426,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(931,463,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(932,359,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(933,257,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(934,258,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(935,259,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(936,344,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(937,339,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(938,463,19,0,'2017-01-01',3,'',12,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(939,437,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(940,438,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(941,440,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(942,439,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(943,446,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(944,450,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(945,451,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(946,452,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(947,453,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(948,455,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(949,456,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(950,457,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(951,458,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(952,468,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(953,469,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(954,468,17,0,'2017-01-01',1,'',6,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(955,469,17,0,'2017-01-01',1,'',6,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(956,463,17,0,'2017-01-01',1,'',6,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(957,470,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE'),(958,472,16,0,'2017-01-01',0,'',3,'','','',NULL,NULL,'','','','NE',NULL,'','NE');

#
# Structure for table "skontroly_zar"
#

